CN103792465A  Power distribution network onephase grounding fault location method based on zero sequence voltage  Google Patents
Power distribution network onephase grounding fault location method based on zero sequence voltage Download PDFInfo
 Publication number
 CN103792465A CN103792465A CN201310721987.1A CN201310721987A CN103792465A CN 103792465 A CN103792465 A CN 103792465A CN 201310721987 A CN201310721987 A CN 201310721987A CN 103792465 A CN103792465 A CN 103792465A
 Authority
 CN
 China
 Prior art keywords
 fault
 current
 centerdot
 line
 prime
 Prior art date
 Legal status (The legal status is an assumption and is not a legal conclusion. Google has not performed a legal analysis and makes no representation as to the accuracy of the status listed.)
 Granted
Links
 230000001264 neutralization Effects 0.000 claims abstract description 35
 230000001629 suppression Effects 0.000 claims abstract description 21
 238000004458 analytical method Methods 0.000 claims abstract description 5
 230000000875 corresponding Effects 0.000 claims description 13
 230000000694 effects Effects 0.000 claims description 9
 230000004807 localization Effects 0.000 claims description 7
 238000005259 measurement Methods 0.000 claims description 5
 230000005540 biological transmission Effects 0.000 claims description 3
 239000003990 capacitor Substances 0.000 claims description 3
 238000002592 echocardiography Methods 0.000 claims description 3
 230000005611 electricity Effects 0.000 claims description 3
 238000009434 installation Methods 0.000 claims description 3
 238000005070 sampling Methods 0.000 abstract 1
 238000004088 simulation Methods 0.000 abstract 1
 238000006467 substitution reaction Methods 0.000 description 7
 238000004364 calculation method Methods 0.000 description 4
 238000005516 engineering process Methods 0.000 description 3
 239000011159 matrix material Substances 0.000 description 3
 101700004025 DHRSX Proteins 0.000 description 2
 238000010586 diagram Methods 0.000 description 2
 230000007274 generation of a signal involved in cellcell signaling Effects 0.000 description 2
 238000011160 research Methods 0.000 description 2
 238000004891 communication Methods 0.000 description 1
 238000011161 development Methods 0.000 description 1
 238000004519 manufacturing process Methods 0.000 description 1
 238000000034 method Methods 0.000 description 1
 230000001052 transient Effects 0.000 description 1
Abstract
A power distribution network onephase grounding fault location method based on a zero sequence voltage belongs to a power distribution network grounding fault location method. The fault location method starts from an overall zero sequence parameter of a singleend radial medium voltage power distribution network, analyzes a onephase grounding fault while taking a distributed parameter model influence into consideration, measures a steadystate zero sequence voltage value and a zero sequence current of each feeder line at a bus position and at a tail end of each outlet line, and finds zero sequence voltage variation characteristics of a fault feeder line and nonfault feeder line. According to the invention, a large number of existing devices are used, the data sampling requirement is low in terms of being realtime, and the method of the invention is easy to realize; the simulation model analysis is established according to the actual parameters, so that the fault location can be realized in the system in which the neutral point is not grounded or the neutral point is grounded through an arc suppression coil; the precision is quite high; and the location method of the invention can be applied to the medium and low voltage power distribution network.
Description
Technical field:
The present invention relates to a kind of method of distribution net work earthing fault range finding, particularly a kind of method of the range finding of the onephase earthing failure in electric distribution network based on residual voltage.
Background technology:
Power distribution network safe operation provides important guarantee to social production life, is difficult to estimate once there is significant trouble economic loss.Therefore, the fault of quick and precisely finding range, economy, safety and reliability to electric system are extremely important.Singlephase earth fault probability of happening maximum in power distribution network.
Along with the development of distribution network automated technology, the novel panel switches with measurement and communication function are installed on feeder line, can obtain a large amount of circuit information about power, then use electrician's network graph theory principle to set up adjacency matrix and the nodal information matrix of node, and then draw fault judgment matrix and to its ultimate analysis, can judge fault section.The identification of fault section can realize quick excision fault, but can not realize accurately fault localization, cannot meet followup work requirement.Mainly contain two kinds of methods for fault localization: traveling wave method and impedance method.Wherein traveling wave method has good accuracy, and impedance method has good stability, the advantage of comprehensive two kinds of methods, and utilize the phase relation of measurement point negativesequence current and trouble spot negative sequence voltage to find range.But distribution line complex structure, branch are numerous, circuit distance is short, be difficult to solve the identification of fault wave head and the problem that mixed surge impedance of a line changes.Need many cover row ripple checkout equipments, financial cost is higher simultaneously.Therefore traveling wave method is difficult to be applicable to power distribution network.If employing impedance method, not only can overcome a range finding difficult problem for traveling wave method, and can utilize a large amount of existing equipment that puts into operation, hardware investment is little, easily realizes.For bothend impedance method, can adopt phase compensation method to eliminate error between asynchronous zerosequence current, the voltage collecting to carry out fault distance calculating.But the impedance method adopting adopts lumped parameter model to calculate mostly in the past, owing to not considering the impact of distributed capacitance, error calculated is larger.Based on the fault distancefinding method of distributed parameter model, while having overcome based on lumped parameter model, ignore the drawback of distributed capacitance impact, can improve distance accuracy.Part computing method adopt fixing route parameter calculation, the larger error of same existence.China's medium voltage distribution network mostly is singleended radial electrical network, the singlephase earth fault that mostly occurs, and failure line selection and fault section determine that research aspect has obtained great successes and obtained good application, the fault location difficulty that how to realize medium voltage distribution network is larger.When singlephase earth fault, transient state energy is little, and travelling wave signal measures difficulty; And traditional ranging technology based on impedance method is used for highvoltage fence, neutral grounding mode is different from low and medium voltage distribution network, when research, how to consider and to consider cannot directly apply to medium voltage distribution network by uniline more from positive order parameter.
Summary of the invention
The object of the invention is to provide a kind of method of the range finding of the onephase earthing failure in electric distribution network based on residual voltage, solution distribution network line complex structure, the large problem of singlephase ground fault distance measuring error that branch is numerous, the short feature of circuit distance is brought.
The object of the present invention is achieved like this: this fault distancefinding method is from singleended radial medium voltage distribution network entirety Zero sequence parameter, while analyzing singlephase earth fault, consider the impact of distributed parameter model, stable state residual voltage value and each feeder line zerosequence current after measurement bus place and each outlet end fault, find out fault feeder and nonfault feeder residual voltage Variation Features.
Concrete steps are as follows:
(1), distributed parameter transmission line model
Power distribution network is carried out to fault localization, utilize distributed parameter model to carry out fault localization; By line parameter circuit value is calculated, when singlephase earth fault occurs, conduction current is much smaller than capacitance current over the ground, therefore can ignore the impact that electricity is led over the ground, zero sequence equivalent circuit distributed parameter model is reduced to line impedance and ground capacitance is evenly distributed along the line;
(2), nonfault line analysis
Feeder line is divided into n minizone, gets wherein arbitrary minizone and be denoted as [x, x+ Δ x], this minizone produce to vagabond current Δ I
_{c}=I
_{c}Δ x, I
_{c}for the line mutualground capacitor electric current of unit length;
For nonfault line, the electric current Δ I that each minizone produces
_{c}the scope flowing through is on the line the position x to place, minizone by bus, then flows to trouble spot through ground; If reference position corresponding to every minizone is x, the voltage that function of current produces is respectively Δ I
_{c}xx, the voltage that each interval function of current over the ground producing produces on circuit: Δ U=Δ I
_{c}xx, in formula: X is the resistance value of circuit unit length;
Known according to superposition theorem, the residual voltage at circuit two ends is poor is the result of zerosequence current effect, and above formula both sides obtain x integration simultaneously:
${\∫}_{0}^{l}d{\stackrel{\·}{U}}^{\′}={\∫}_{0}^{l}{\stackrel{.}{I}}_{C}\·X\·x\·\mathrm{dx},$ Calculate:
${\stackrel{.}{U}}_{2}{\stackrel{.}{U}}_{1}=\frac{1}{2}{I}_{C}\·X\·{l}^{2}\left(1\right),$ L is nonfault line length,
nonfault line first and end residual voltage respectively;
(3), isolated neutral system faulty line is analyzed
For faulty line, trouble spot current flowing comprises nonfault capacitive earth current and faulty line capacitive earth current; Voltage, current distributions behind trouble spot are identical with nonfault line, minizone capacitive earth current flows to the earth by electric capacity, flow back to circuit by trouble spot again, to the circuit before trouble spot without effect, be equivalent to circuit, ground capacitance, and trouble spot between form loop checking installation; Minizone capacitive earth current flows to the earth by ground capacitance, then flows back to bus through trouble spot by circuit; Therefore minizone over the ground the function of current produce the scope of voltage be by minizone to trouble spot, minizone goes out one to bus section, busbar section electric current one and enters to cancel out each other; If fault distance is x, voltage variety Δ U '=Δ I that the function of current over the ground producing apart from the minizone of bus x ' produces on circuit
_{c}x (xx '); The same, can obtain the voltage variety that bus produces to the trouble spot linetoground function of current in circuit:
${\∫}_{0}^{x}d{\stackrel{\·}{U}}^{\′}={\∫}_{0}^{x}{\stackrel{.}{I}}_{C}\·X\·(x{x}^{\′})\·{\mathrm{dx}}^{\′},$ ?
${\stackrel{.}{U}}^{\′}=\frac{1}{2}{\stackrel{.}{I}}_{C}\·X\·{x}^{2};$ Trouble spot also comprise nonfault line to vagabond current to bus section, busbar section zerosequence current and
voltage variety in this interval generation:
${\stackrel{.}{U}}^{\″}={\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}}\·X\·x;$ Known according to superposition theorem:
${\stackrel{.}{U}}^{\′}+{\stackrel{.}{U}}^{\″}=(\frac{1}{2}{\stackrel{.}{I}}_{C}\·x{\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}})X\·x={\stackrel{.}{U}}_{f}{\stackrel{.}{U}}_{1}^{\′}\left(2\right);$ The change in voltage of trouble spot circuit is identical with nonfault line situation, therefore,
wherein: l ' is faulty line total length,
corresponding faulty line first and end residual voltage and fault point voltage respectively; (2), (3) formula is added:
${\stackrel{.}{U}}_{2}^{\′}{\stackrel{.}{U}}_{1}^{\′}=\frac{1}{2}{\stackrel{.}{I}}_{C}\·X\·({l}^{\′2}{2l}^{\′}\·x)+{\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}}\·X\·x\left(4\right);$
(4), neutral point is analyzed through arc suppression coil faulty line
Nonfault line zerosequence current and the residual voltage situation of change of neutral by arc extinction coil grounding system are identical with isolated neutral system; And faulty line zerosequence current situation is equivalent to flow through in trouble spot stack the inductance current of arc suppression coil on isolated neutral system faulty line basis
as system works in full compensating coefficient is, trouble spot reactive current is zero, if ignore system active current, the zerosequence current recording from fault branch head end is the capacitance current being produced by this branch road self, and application residual voltage changes and cannot find range; But in arc suppression coil when operation, is for avoiding resonance appearance, generally operate in overcompensation state, also that the zerosequence current character of fault branch occurs when singlephase earthing is similar to nonfault branch, because the capacitance current that self distribution parameter does not produce on yearonyear basis of overcompensation situation will be more greatly, and
the gain of parameter of large I when tuning by arc suppression coil; Residual voltage acts on after the current hysteresis that arc suppression coil produces 90 °, and 90 ° of leading residual voltages of capacitive earth current, therefore
with
single spinecho.
the voltage variety producing in fault section:
finally, draw the formula corresponding to compensated distribution network:
${\stackrel{.}{U}}_{2}^{\′}{\stackrel{.}{U}}_{1}^{\′}=\frac{1}{2}{\stackrel{.}{I}}_{C}\·X\·({l}^{\′2}{2l}^{\′}\·x)+({\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}}{\stackrel{.}{I}}_{L})\·X\·x\left(5\right);$
Beneficial effect, has adopted such scheme, can utilize a large amount of existing equipment that puts into operation, and realizes simply, has stronger economy and good practical value; Employing distributed parameter model calculates, and has overcome in power distribution network tradition Fault Locating Method owing to using lumped parameter model to cause the problem that error is larger; The method is not only applicable to isolated neutral system, also be applicable to neutral by arc extinction coil grounding system, and only need obtain each branch road zerosequence current and branch road end residual voltage steadystate value and the tuning situation of arc suppression coil after singlephase earth fault, on the basis of correctly selecting fault feeder, can accurately find range.
Accompanying drawing explanation
Fig. 1 zero sequence equivalent circuit distributed parameter model.
Fig. 2 nonfault line zerosequence current distribution plan.
Fig. 3 isolated neutral system faulty line zerosequence current forms feature.
Fig. 4 neutral point arc suppression coil earthing system faulty line zerosequence current forms feature.
The method flow diagram of the onephase earthing failure in electric distribution network range finding of Fig. 5 based on residual voltage.
Fig. 6 PSCAD realistic model.
Embodiment:
Embodiment 1: this fault distancefinding method is from singleended radial medium voltage distribution network entirety Zero sequence parameter, while analyzing singlephase earth fault, consider the impact of distributed parameter model, stable state residual voltage value and each feeder line zerosequence current after measurement bus place and each outlet end fault, find out fault feeder and nonfault feeder residual voltage Variation Features.
Concrete steps are as follows:
1, distributed parameter transmission line model
Utilize distributed parameter model to carry out fault localization to power distribution network; By line parameter circuit value is calculated, when singlephase earth fault occurs, conduction current is much smaller than capacitance current over the ground, therefore can ignore the impact that electricity is led over the ground, zero sequence equivalent circuit distributed parameter model is reduced to line impedance and ground capacitance is evenly distributed along the line;
2, nonfault line analysis
Feeder line is divided into n minizone, gets wherein arbitrary minizone and be denoted as [x, x+ Δ x], this minizone produce to vagabond current Δ I
_{c}=I
_{c}Δ x, I
_{c}for the line mutualground capacitor electric current of unit length;
For nonfault line, the electric current Δ I that each minizone produces
_{c}the scope flowing through is on the line the position x to place, minizone by bus, then flows to trouble spot through ground; If reference position corresponding to every minizone is x, the voltage that function of current produces is respectively Δ I
_{c}xx, the voltage that each interval function of current over the ground producing produces on circuit: Δ U=Δ I
_{c}xx, in formula: X is the resistance value of circuit unit length;
Known according to superposition theorem, the residual voltage at circuit two ends is poor is the result of zerosequence current effect, and above formula both sides obtain x integration simultaneously:
${\∫}_{0}^{l}d{\stackrel{\·}{U}}^{\′}={\∫}_{0}^{l}{\stackrel{.}{I}}_{C}\·X\·x\·\mathrm{dx},$ Calculate:
${\stackrel{.}{U}}_{2}{\stackrel{.}{U}}_{1}=\frac{1}{2}{I}_{C}\·X\·{l}^{2}\left(1\right),$ L is nonfault line length
nonfault line first and end residual voltage respectively;
3, isolated neutral system faulty line is analyzed
For faulty line, trouble spot current flowing comprises nonfault capacitive earth current and faulty line capacitive earth current; Voltage, current distributions behind trouble spot are identical with nonfault line, minizone capacitive earth current flows to the earth by electric capacity, flow back to circuit by trouble spot again, to the circuit before trouble spot without effect, be equivalent to circuit, ground capacitance, and trouble spot between form loop checking installation; Minizone capacitive earth current flows to the earth by ground capacitance, then flows back to bus through trouble spot by circuit; Therefore minizone over the ground the function of current produce the scope of voltage be by minizone to trouble spot, minizone goes out one to bus section, busbar section electric current one and enters to cancel out each other; If fault distance is x, voltage variety Δ U '=Δ I that the function of current over the ground producing apart from the minizone of bus x ' produces on circuit
_{c}x (xx '); The same, can obtain the voltage variety that bus produces to the trouble spot linetoground function of current in circuit:
${\∫}_{0}^{x}d{\stackrel{\·}{U}}^{\′}={\∫}_{0}^{x}{\stackrel{.}{I}}_{C}\·X\·(x{x}^{\′})\·{\mathrm{dx}}^{\′},$ ?
${\stackrel{.}{U}}^{\′}=\frac{1}{2}{\stackrel{.}{I}}_{C}\·X\·{x}^{2};$ Trouble spot also comprise nonfault line to vagabond current to bus section, busbar section zerosequence current and
voltage variety in this interval generation:
${\stackrel{.}{U}}^{\″}={\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}}\·X\·x;$ Known according to superposition theorem:
${\stackrel{.}{U}}^{\′}+{\stackrel{.}{U}}^{\″}=(\frac{1}{2}{\stackrel{.}{I}}_{C}\·x{\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}})X\·x={\stackrel{.}{U}}_{f}{\stackrel{.}{U}}_{1}^{\′}\left(2\right);$ The change in voltage of trouble spot circuit is identical with nonfault line situation, therefore,
wherein: l ' is faulty line total length,
corresponding faulty line first and end residual voltage and fault point voltage respectively; (2), (3) formula is added:
${\stackrel{.}{U}}_{2}^{\′}{\stackrel{.}{U}}_{1}^{\′}=\frac{1}{2}{\stackrel{.}{I}}_{C}\·X\·({l}^{\′2}{2l}^{\′}\·x)+{\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}}\·X\·x\left(4\right);$
4, neutral point is analyzed through arc suppression coil faulty line
Nonfault line zerosequence current and the residual voltage situation of change of neutral by arc extinction coil grounding system are identical with isolated neutral system; And faulty line zerosequence current situation is equivalent to flow through in trouble spot stack the inductance current of arc suppression coil on isolated neutral system faulty line basis
; As system works in full compensating coefficient is, trouble spot reactive current is zero, if ignore system active current, the zerosequence current recording from fault branch head end is the capacitance current being produced by this branch road self, and application residual voltage changes and cannot find range; But in arc suppression coil when operation, is for avoiding resonance appearance, generally operate in overcompensation state, also that the zerosequence current character of fault branch occurs when singlephase earthing is similar to nonfault branch, because the capacitance current that self distribution parameter does not produce on yearonyear basis of overcompensation situation will be more greatly, and
the gain of parameter of large I when tuning by arc suppression coil; Residual voltage acts on after the current hysteresis that arc suppression coil produces 90 °, and 90 ° of leading residual voltages of capacitive earth current, therefore
with
single spinecho.
the voltage variety producing in fault section:
finally, draw the formula corresponding to compensated distribution network:
${\stackrel{.}{U}}_{2}^{\′}{\stackrel{.}{U}}_{1}^{\′}=\frac{1}{2}{\stackrel{.}{I}}_{C}\·X\·({l}^{\′2}{2l}^{\′}\·x)+({\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}}{\stackrel{.}{I}}_{L})\·X\·x\left(5\right);$
As shown in Figure 5, specific implementation step is as follows for this method specific implementation process flow diagram:
From wave recording device, reading flow is crossed head end zerosequence current and end residual voltage Wave data after arc suppression coil electric current (for neutral by arc extinction coil grounding system), busbar voltage, each feeder fault;
The data that read are carried out to Fast Fourier Transform (FFT) (FFT), obtain the effective value that each signal is corresponding, adopt power frequency component calculates can harmonic carcellation etc. the error of signal generation;
On the basis completing in route selection, determine fault branch;
To record the data substitution formula (1) that nonfault line is corresponding, online calculate fault moment circuit unit length zero sequence impedance value X;
Judge system neutral earthing mode;
For isolated neutral system, the circuit unit length zero sequence impedance value X substitution formula (4) that the data that faulty line is recorded and step 4 calculate calculates fault distance; For neutral by arc extinction coil grounding system, substitution formula (5) calculates.
(1) electric current and voltage distribution characteristics after fault
After fault, feeder line capacitive earth current distributes along the line, first all capacitive earth currents flow to the earth, flow back to faulty line through trouble spot, finally flow to bus, the circulation of vagabond current has been produced to effect to the variation of residual voltage, the rule that nonfault line residual voltage effective value along the line is increased by oblique line to line end gradually by bus distributes, the rule that faulty line residual voltage effective value is increased by oblique line to bus section gradually by trouble spot distributes, trouble spot distributes by the rule increasing gradually by oblique line to line end, it is trouble spot place residual voltage effective value minimum.
(2) Fault Location Algorithm
After fault occurs and malfunction stable after, from wave recording device, read busbar voltage, after each feeder fault, head end zerosequence current and end residual voltage Wave data also need to flow through the Wave data of arc suppression coil electric current for neutral by arc extinction coil grounding system, the data that read are carried out to Fast Fourier Transform (FFT) (FFT), obtain the effective value that each signal is corresponding, adopt power frequency component calculates can harmonic carcellation etc. the error of signal generation, in utilization, the existing ripe variant projects of location of step result of calculation basis is determined faulty line, the data substitution formula that nonfault line is corresponding will be recorded
online calculate fault moment circuit unit length zero sequence impedance value X, the circuit unit length zero sequence impedance value X substitution formula that the data that faulty line recorded for isolated neutral system and upper step calculate
calculate fault distance, for neutral by arc extinction coil grounding system, substitution formula
${\stackrel{.}{U}}_{2}^{\′}{\stackrel{.}{U}}_{1}^{\′}=\frac{1}{2}{\stackrel{.}{I}}_{C}\·X\·({l}^{\′2}{2l}^{\′}\·x)+{\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}}\·X\·x$ Calculate.
The effect assessment of scheme:
The present invention has very high position precision and possesses very high adaptability at Complicated Distribution Network, and for different neutral grounding modes, the present invention all can meet.Now take a model as example:
Utilize PSCAD/EMTDC Software tool to set up the realistic model of the singleended radial network system of 35kV, as shown in Figure 6.Circuit Fault on Secondary Transformer connects arc suppression coil through isolating switch, can centering point earthfree and compensated distribution network emulation; System has three cables, and cable length is got respectively 18km, 16km and 20km, and cable adopts three singlephase cables that are embedded in underground 1m to be del and places the system of laying of (axle center spacing is 30mm), and crosssection of cable area is got 240mm2; Bus bar side adopts the 110kV of ΥΔ connection to become 35kV transformer, and line end adopts the 35kV of ΔΥ connection to become the transformer of 10kV; Load connects the threephase balancing load of 0.35MW+0.08MVar.
With isolated neutral system, be that example is calculated there is metallic earthing apart from bus 2km place.Busbar voltage is 20469.2V, and each feeder line head end zerosequence current is 7.33167A, 6.51593A, 13.8476A, each feeder terminal residual voltage 20493.9V, 20488.7V, 20483.4V.Utilize existing variant projects of location, it is circuit III that for example ratio phase comparing method can be judged faulty line.
Utilize circuit I unit of account length circuit capacitive earth current I
_{c}and unit length zero sequence impedance value X:I
_{c}=I
_{c1}/ l
_{1}=0.407315A/km.
$X=\frac{2({U}_{2}{U}_{1})}{{I}_{C}\·{l}_{1}}=0.374327\mathrm{\Ω}/\mathrm{km}$
For isolated neutral system, nonfault line capacitive earth current and equal zerosequence current that faulty line head end measures:
${I}_{C3}={I}_{C1}+{I}_{{C}_{\mathrm{\Σ}}}=13.8476A.$
Above each result of calculation substitution formula (4) is obtained to fault distance x=1.9791km.
Definition measuring error is:
error is 0.104%.
For the validity of checking this method, table 1 has provided isolated neutral system singlephase earth fault and has betided diverse location, range finding result when the different transition resistance ground connection.
Table 1 isolated neutral singlephase ground fault distance measuring result
This algorithm is equally applicable to neutral by arc extinction coil grounding system as can be seen from Table 2, and all has higher range accuracy for different dehumorous degree.
Claims (1)
1. the method for the range finding of the onephase earthing failure in electric distribution network based on residual voltage, it is characterized in that: this fault distancefinding method is from singleended radial medium voltage distribution network entirety Zero sequence parameter, while analyzing singlephase earth fault, consider the impact of distributed parameter model, stable state residual voltage value and each feeder line zerosequence current after measurement bus place and each outlet end fault, find out fault feeder and nonfault feeder residual voltage Variation Features;
Concrete steps are as follows:
(1), distributed parameter transmission line model
Power distribution network is carried out to fault localization, utilize distributed parameter model to carry out fault localization; By line parameter circuit value is calculated, when singlephase earth fault occurs, conduction current is much smaller than capacitance current over the ground, therefore can ignore the impact that electricity is led over the ground, zero sequence equivalent circuit distributed parameter model is reduced to line impedance and ground capacitance is evenly distributed along the line;
(2), nonfault line analysis
Feeder line is divided into n minizone, gets wherein arbitrary minizone and be denoted as [x, x+ Δ x], this minizone produce to vagabond current Δ I
_{c}=I
_{c}Δ x, I
_{c}for the line mutualground capacitor electric current of unit length;
For nonfault line, the electric current Δ I that each minizone produces
_{c}the scope flowing through is on the line the position x to place, minizone by bus, then flows to trouble spot through ground; If reference position corresponding to every minizone is x, the voltage that function of current produces is respectively Δ I
_{c}xx, the voltage that each interval function of current over the ground producing produces on circuit: Δ U=Δ I
_{c}xx, in formula: X is the resistance value of circuit unit length;
Known according to superposition theorem, the residual voltage at circuit two ends is poor is the result of zerosequence current effect, and above formula both sides obtain x integration simultaneously:
${\∫}_{0}^{l}d\stackrel{.}{U}={\∫}_{0}^{l}{\stackrel{.}{I}}_{C}\·X\·x\·\mathrm{dx},$ Calculate:
${\stackrel{.}{U}}_{2}{\stackrel{.}{U}}_{1}=\frac{1}{2}{I}_{C}\·X\·{l}^{2}\left(1\right),$ L is nonfault line length,
nonfault line first and end residual voltage respectively;
(3), isolated neutral system faulty line is analyzed
For faulty line, trouble spot current flowing comprises nonfault capacitive earth current and faulty line capacitive earth current; Voltage, current distributions behind trouble spot are identical with nonfault line, minizone capacitive earth current flows to the earth by electric capacity, flow back to circuit by trouble spot again, to the circuit before trouble spot without effect, be equivalent to circuit, ground capacitance, and trouble spot between form loop checking installation; Minizone capacitive earth current flows to the earth by ground capacitance, then flows back to bus through trouble spot by circuit; Therefore minizone over the ground the function of current produce the scope of voltage be by minizone to trouble spot, minizone goes out one to bus section, busbar section electric current one and enters to cancel out each other; If fault distance is x, voltage variety Δ U '=Δ I that the function of current over the ground producing apart from the minizone of bus x ' produces on circuit
_{c}x (xx '); The same, can obtain the voltage variety that bus produces to the trouble spot linetoground function of current in circuit:
${\∫}_{0}^{x}d{\stackrel{\·}{U}}^{\′}={\∫}_{0}^{x}{\stackrel{.}{I}}_{C}\·X\·(x{x}^{\′})\·{\mathrm{dx}}^{\′},$ ?
${\stackrel{.}{U}}^{\′}=\frac{1}{2}{\stackrel{.}{I}}_{C}\·X\·{x}^{2};$ Trouble spot also comprise nonfault line to vagabond current to bus section, busbar section zerosequence current and
voltage variety in this interval generation:
${\stackrel{.}{U}}^{\″}={\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}}\·X\·x;$ Known according to superposition theorem:
${\stackrel{.}{U}}^{\′}+{\stackrel{.}{U}}^{\″}=(\frac{1}{2}{\stackrel{.}{I}}_{C}\·x{\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}})X\·x={\stackrel{.}{U}}_{f}{\stackrel{.}{U}}_{1}^{\′}$ (2); The change in voltage of trouble spot circuit is identical with nonfault line situation, therefore,
wherein: l ' is faulty line total length,
corresponding faulty line first and end residual voltage and fault point voltage respectively; (2), (3) formula is added:
${\stackrel{.}{U}}_{2}^{\′}{\stackrel{.}{U}}_{1}^{\′}=\frac{1}{2}{\stackrel{.}{I}}_{C}\·X\·({l}^{\′2}{2l}^{\′}\·x)+{\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}}\·X\·x\left(4\right);$
(4), neutral point is analyzed through arc suppression coil faulty line
Nonfault line zerosequence current and the residual voltage situation of change of neutral by arc extinction coil grounding system are identical with isolated neutral system; And faulty line zerosequence current situation is equivalent to flow through in trouble spot stack the inductance current I L of arc suppression coil on isolated neutral system faulty line basis; As system works in full compensating coefficient is, trouble spot reactive current is zero, if ignore system active current, the zerosequence current recording from fault branch head end is the capacitance current being produced by this branch road self, and application residual voltage changes and cannot find range; But in arc suppression coil when operation, is for avoiding resonance appearance, generally operate in overcompensation state, also that the zerosequence current character of fault branch occurs when singlephase earthing is similar to nonfault branch, because the capacitance current that self distribution parameter does not produce on yearonyear basis of overcompensation situation will be more greatly, and
the gain of parameter of large I when tuning by arc suppression coil; Residual voltage acts on after the current hysteresis that arc suppression coil produces 90 °, and 90 ° of leading residual voltages of capacitive earth current, therefore
single spinecho.
the voltage variety producing in fault section:
finally, draw the formula corresponding to compensated distribution network:
${\stackrel{.}{U}}_{2}^{\′}{\stackrel{.}{U}}_{1}^{\′}=\frac{1}{2}{\stackrel{.}{I}}_{C}\·X\·({l}^{\′2}{2l}^{\′}\·x)+({\stackrel{.}{I}}_{{C}_{\mathrm{\Σ}}}{\stackrel{.}{I}}_{L})\·X\·x\left(5\right);$
Priority Applications (1)
Application Number  Priority Date  Filing Date  Title 

CN201310721987.1A CN103792465B (en)  20131224  20131224  A kind of method of the range finding of the onephase earthing failure in electric distribution network based on residual voltage 
Applications Claiming Priority (1)
Application Number  Priority Date  Filing Date  Title 

CN201310721987.1A CN103792465B (en)  20131224  20131224  A kind of method of the range finding of the onephase earthing failure in electric distribution network based on residual voltage 
Publications (2)
Publication Number  Publication Date 

CN103792465A true CN103792465A (en)  20140514 
CN103792465B CN103792465B (en)  20160504 
Family
ID=50668329
Family Applications (1)
Application Number  Title  Priority Date  Filing Date 

CN201310721987.1A Active CN103792465B (en)  20131224  20131224  A kind of method of the range finding of the onephase earthing failure in electric distribution network based on residual voltage 
Country Status (1)
Country  Link 

CN (1)  CN103792465B (en) 
Cited By (12)
Publication number  Priority date  Publication date  Assignee  Title 

CN104808114A (en) *  20150504  20150729  中国矿业大学  Lowcurrent grounding fault line selection method based on widearea zerosequence voltage distribution characteristics 
CN105067950A (en) *  20150723  20151118  西安工程大学  Doubleterminal fault location method based on longitudinal impedance 
CN105652147A (en) *  20150909  20160608  三峡大学  Single/doublecircuit powertransmissionline wholeline highprecision fault range finding method 
CN107102241A (en) *  20170608  20170829  国网江苏省电力公司无锡供电公司  A kind of fault distancefinding method and device unknown based on R L line parameter circuit values 
CN109298288A (en) *  20181129  20190201  中国矿业大学  The distribution network failure section accurate positioning method of wide area zerosequence current distributed intelligence 
CN109521325A (en) *  20181016  20190326  山东职业学院  A kind of calculation method carrying out distribution line failure positioning using main oscillation frequency 
CN109581149A (en) *  20181204  20190405  华北电力大学  Travelling wave ranging method and system under arc suppression coil parallel low resistance earthing mode 
CN109870629A (en) *  20190114  20190611  国网江西省电力有限公司南昌供电分公司  A kind of fault simulation system and method based on neutral grounding mode 
CN110879332A (en) *  20191205  20200313  南京南瑞继保电气有限公司  Singlephase earth fault phase selection method suitable for small current grounding system 
CN111103499A (en) *  20181009  20200505  长沙理工大学  Method for measuring ground parameters of power distribution network grounded through arc suppression coil series resistor 
CN111525441A (en) *  20200430  20200811  国网湖南省电力有限公司  Uninterrupted operation method for operation point 
CN111796165A (en) *  20200721  20201020  河海大学  Power distribution network fault positioning method based on selfadaptive Fourier transform 
Citations (6)
Publication number  Priority date  Publication date  Assignee  Title 

US20100277181A1 (en) *  20060112  20101104  Abb Technology Ltd.  Method and device for fault location in a twoterminal transmission or distribution power line 
CN202710702U (en) *  20120720  20130130  王道龙  Mediumvoltage distribution network fault monitoring device 
CN103022992A (en) *  20121123  20130403  山东电力集团公司  Feeder ground positioning method based on dispersion zero sequence voltage detection 
CN103245893A (en) *  20130410  20130814  昆明理工大学  Radial distribution network layered and distributed ANN fault location method based on natural frequency 
CN103293440A (en) *  20130519  20130911  国家电网公司  Line singlephase earth fault singleterminal ranging method implemented by aid of sequence components 
CN103293442A (en) *  20130519  20130911  国家电网公司  Line singlephase earth fault singleterminal location method implemented by aid of zerosequence voltage distribution characteristics 

2013
 20131224 CN CN201310721987.1A patent/CN103792465B/en active Active
Patent Citations (6)
Publication number  Priority date  Publication date  Assignee  Title 

US20100277181A1 (en) *  20060112  20101104  Abb Technology Ltd.  Method and device for fault location in a twoterminal transmission or distribution power line 
CN202710702U (en) *  20120720  20130130  王道龙  Mediumvoltage distribution network fault monitoring device 
CN103022992A (en) *  20121123  20130403  山东电力集团公司  Feeder ground positioning method based on dispersion zero sequence voltage detection 
CN103245893A (en) *  20130410  20130814  昆明理工大学  Radial distribution network layered and distributed ANN fault location method based on natural frequency 
CN103293440A (en) *  20130519  20130911  国家电网公司  Line singlephase earth fault singleterminal ranging method implemented by aid of sequence components 
CN103293442A (en) *  20130519  20130911  国家电网公司  Line singlephase earth fault singleterminal location method implemented by aid of zerosequence voltage distribution characteristics 
Cited By (17)
Publication number  Priority date  Publication date  Assignee  Title 

CN104808114A (en) *  20150504  20150729  中国矿业大学  Lowcurrent grounding fault line selection method based on widearea zerosequence voltage distribution characteristics 
CN104808114B (en) *  20150504  20171229  中国矿业大学  The earth fault line selection method of wide area zero sequence spread voltage feature 
CN105067950A (en) *  20150723  20151118  西安工程大学  Doubleterminal fault location method based on longitudinal impedance 
CN105067950B (en) *  20150723  20180515  西安工程大学  Two Terminal Fault Location method based on longitudinal impedance 
CN105652147A (en) *  20150909  20160608  三峡大学  Single/doublecircuit powertransmissionline wholeline highprecision fault range finding method 
CN105652147B (en) *  20150909  20180724  三峡大学  A kind of mono/bisback transmission line all fronts highprecision fault distancefinding method 
CN107102241A (en) *  20170608  20170829  国网江苏省电力公司无锡供电公司  A kind of fault distancefinding method and device unknown based on R L line parameter circuit values 
CN111103499A (en) *  20181009  20200505  长沙理工大学  Method for measuring ground parameters of power distribution network grounded through arc suppression coil series resistor 
CN109521325A (en) *  20181016  20190326  山东职业学院  A kind of calculation method carrying out distribution line failure positioning using main oscillation frequency 
CN109298288A (en) *  20181129  20190201  中国矿业大学  The distribution network failure section accurate positioning method of wide area zerosequence current distributed intelligence 
CN109581149A (en) *  20181204  20190405  华北电力大学  Travelling wave ranging method and system under arc suppression coil parallel low resistance earthing mode 
CN109581149B (en) *  20181204  20200724  华北电力大学  Traveling wave distance measurement method and system under arc suppression coil parallel small resistance grounding mode 
CN109870629A (en) *  20190114  20190611  国网江西省电力有限公司南昌供电分公司  A kind of fault simulation system and method based on neutral grounding mode 
CN109870629B (en) *  20190114  20210326  国网江西省电力有限公司南昌供电分公司  Fault simulation system and method based on neutral point grounding mode 
CN110879332A (en) *  20191205  20200313  南京南瑞继保电气有限公司  Singlephase earth fault phase selection method suitable for small current grounding system 
CN111525441A (en) *  20200430  20200811  国网湖南省电力有限公司  Uninterrupted operation method for operation point 
CN111796165A (en) *  20200721  20201020  河海大学  Power distribution network fault positioning method based on selfadaptive Fourier transform 
Also Published As
Publication number  Publication date 

CN103792465B (en)  20160504 
Similar Documents
Publication  Publication Date  Title 

CN103792465B (en)  A kind of method of the range finding of the onephase earthing failure in electric distribution network based on residual voltage  
CN103675605B (en)  A kind of power distribution network earth fault line selection method based on the correlation analysis of faultsignal transient state  
Suonan et al.  A novel faultlocation method for HVDC transmission lines  
CN103308823B (en)  A kind of power distribution network singlephase disconnection phase to phase fault localization method  
CN101232176B (en)  Noneffective earthing distribution system fault locating method based on neutral point of transient traveling wave  
CN103941147B (en)  Utilize the distribution network cable singlephase ground fault distance measuring method of transient state principal frequency component  
CN104898021B (en)  A kind of distribution network fault line selection method based on k means cluster analyses  
CN102135571B (en)  Antiinterference measurement method for zero sequence impedance of superhighvoltage/ultrahighvoltage multiloop power transmission line  
CN103454555B (en)  Based on the onephase earthing failure in electric distribution network Section Location of parameter identification  
CN105093062A (en)  Comprehensive fault positioning method of transmission line  
CN102590654B (en)  Element and method for discriminating fault electrode of DC transmission line  
CN104793106A (en)  Distribution network line fault section positioning method based on current break rate  
CN104808114A (en)  Lowcurrent grounding fault line selection method based on widearea zerosequence voltage distribution characteristics  
CN103178508B (en)  Pilot protection method of VSCHVDC (Voltage Source ConverterHigh Voltage Direct Current) power transmission circuit based on shunt capacitance parameter identification  
CN108107319A (en)  A kind of multiterminal flexible direct current electric network fault localization method and system  
CN103616609A (en)  High voltage DC ground electrode circuit fault distance measurement method utilizing DC components  
CN109541392A (en)  A kind of oneend fault ranging method suitable for flexible HVDC transmission system  
CN108196162A (en)  The DC distribution net monopolar grounding fault wireline inspection method of model and parameters identification  
CN104808112A (en)  Section instantaneous powerbased method of positioning fault sections of distribution network lines  
CN105738769A (en)  Seriescompensation doublecircuit line fault locating method based on distributed parameter model  
CN107271842A (en)  A kind of parallel erected on same tower doublecircuit line Fault Locating Method based on positivesequence component in the same direction  
CN103424627A (en)  Method for measuring zerosequence impedance of parallel distribution network circuit at double ends  
CN103743996B (en)  A kind of based on π type equivalent circuit direct current grounding pole circuit fault distance measurement  
CN105116294A (en)  Traveling wave polarity measure based power distribution network cable fault monitoring method  
CN103245893A (en)  Radial distribution network layered and distributed ANN fault location method based on natural frequency 
Legal Events
Date  Code  Title  Description 

C06  Publication  
PB01  Publication  
C10  Entry into substantive examination  
SE01  Entry into force of request for substantive examination  
C14  Grant of patent or utility model  
GR01  Patent grant 