Buried underground workshop all-pass wind-warm syndrome, wet sub-control system
The utility model relates to buried underground workshop ventilating system, especially relates to buried underground workshop all-pass wind-warm syndrome, wet sub-control system.
The key link of room ventilation, air-conditioning system is exactly to inquire into the problem that adopts which kind of air-supply air current composition method and type, so this field has received domestic and international correlative study scholar and project planner's attention.
Along with science and technology development, human to living environment and production environment Temperature and Humidity Control require more and more high on every side; The application of the production of exact science instrument, aerospace equipment element, electronic devices and components and weaving production line etc. all have quite strict requirement to warm and humid environmental condition; At present, buried underground workshop air handling system all takes in the same apparatus of air conditioning, to regulate simultaneously control to the control and regulation of temperature, wet index.This just need provide working-medium waters such as heating, humidification, cooling to the apparatus of air conditioning; Carry out cold and hot exchange through heat exchanger room air is carried out adjustment; Adopt chilled water to make the too high air of humidity separate out condensate simultaneously, or adopt humidifier in air, to add the relative humidity that moisture improves air.The chilled water that above-mentioned air conditioning mode adopts all will consume mass energy, also needs huge equipment and space, fabricating yard.And there are hidden danger in the variation, the indoor air quality that are difficult to adapt to well indoor heat moisture ratio.Because temperature, humidity divide control can solve the problem that traditional air-conditioning system is existing and self can not effect a radical cure on the principle preferably; As: system can't normally not move when 1, humidity height and temperature were high: like yellow plum season in the Yangtze river basin; Because the outside air temperature low humidity is high; This moment, air-conditioner did not reach start-up temperature, and compressor does not move and fan operation, and indoor humidity can't be handled; Simultaneously fan operation is constantly sent into new wind to indoor, and outdoor humid air is on the contrary through making indoor air humidity reach outdoor air humidity in the new wind inlet chamber; Air-conditioning cool-down dehumidification simultaneously when 2, freeze summer: because room conditioning control is to have temperature controlledly, therefore air-conditioning no longer freezes when indoor temperature reaches setting value after, is blower fan does not reach cool-down dehumidification in running effect; Moisture removal when 3, the moisture removal of air-conditioning system operation in the sub-load gap is less than stable operation.The home and abroad began to continue to increase to warm and humid minute control techniques research dynamics in recent years, and achievement in research and paper have issue also the time, but was not seen in the report of relevant buried underground workshop all-pass wind-warm syndrome, wet sub-control system.
Summary of the invention
The utility model purpose is to provide a kind of buried underground workshop all-pass wind-warm syndrome, wet sub-control system, reaches energy saving economy, environmental protection, does not take the purpose of fabricating yard.
For realizing above-mentioned purpose, the utility model is taked following technical proposals:
The described buried underground workshop all-pass wind-warm syndrome of the utility model, wet sub-control system comprise gas mixing air channel, and said gas mixing air channel air inlet does not communicate with there being the tailwater gallery of pressure inner chamber, and its gas outlet communicates with underground workshop is indoor; Said Hydropower Station Underground is indoor to communicate with fan inlet, communicates with the pressure fan air inlet through airduct through the air channel respectively; Said pressure fan air outlet communicates with gas mixing air channel.
Gas outlet, said gas mixing air channel is controlled demanding underground power house inner chamber and is communicated with temperature, humidity; Said temperature, humidity are controlled demanding underground power house inner chamber and are required low underground power house inner chamber to communicate through the air channel with temperature, humidity control; Said temperature, humidity control require low underground power house inner chamber to communicate with fan inlet, communicate with the pressure fan air inlet through airduct through the air channel respectively.
The utility model advantage is the external environment fresh air indoor through there not being the tailwater gallery of pressure introducing Hydropower Station Underground; Because the natural heat exchanger that cold storage bodies such as gallery water body and rock surface constitutes; Carry out the dehumidification of damp and hot exchange desuperheat with outdoor high temperature, highly humid air, reduced the air absolute moisture content that new wind is brought underground power house in a large number.The relative humidity of considering air inducing is greater than 90% humidity considerably beyond the underground power house environmental requirement; At this moment carrying out calculation control according to the humiture index; High temperature air draft in the chamber of going to the factory partially and low temperature, high humidity (relative humidity is high) cold wind are mixed in gas mixing air channel, heat up and send in the underground power house after falling wet process.Since during the operation of the ventilating system of the utility model with draw buried power station do not have press tailrace tunnel cold air as temperature, the wet working medium of regulating, saved the mechanical refrigeration device and the apparatus of air conditioning; Therefore, realized energy-conservation, environmental protection, do not take the purpose in an interior erection space and place.
Description of drawings
Fig. 1 is the described system architecture sketch map of the utility model.
The specific embodiment
As shown in Figure 1; The described buried underground workshop all-pass wind-warm syndrome of the utility model, wet sub-control system; Comprise gas mixing air channel 1, said gas mixing air channel 1 air inlet does not communicate with there being the tailwater gallery of pressure 2 inner chambers, and its gas outlet is controlled demanding underground power house 7 inner chambers and communicated with temperature, humidity; Said temperature, humidity are controlled demanding underground power house 7 inner chambers and are required low underground power house 9 inner chambers to communicate through air channel 8 with temperature, humidity control; Said temperature, humidity control require low underground power house 9 inner chambers to communicate with air-introduced machine 4 air inlets, communicate with pressure fan 6 air inlets through airduct 5 through air channel 3 respectively.
The utility model operation principle is summarized as follows:
Under air-introduced machine 4 effects; The outdoor high temperature fresh air carries out damp and hot exchange desuperheat, dehumidification via cold storage body surface layers such as not having pressure tailwater gallery 2 and the water body in it, rock; Reduce new wind and brought the air absolute moisture content in the underground power house 7,9 in a large number into, carried out humidity control; Temperature, humidity control require an air part in the low underground power house 9 under pressure fan 6 effects with it in the air of higher temperature deliver in the gas mixing air channel 1; Mix with the fresh air that carries out damp and hot exchange; Heat up and fall wet (falling relative humidity) processing; Carry out adjustment control, another part is extremely outdoor through air-introduced machine 4 discharge ground.Through controlling the size of air-introduced machine 4, pressure fan 6 air quantity respectively, reach temperature, the humidity index that controls environment and require.