CN101122623A  High voltage electricity transmission system thunderproof property parameter test method  Google Patents
High voltage electricity transmission system thunderproof property parameter test method Download PDFInfo
 Publication number
 CN101122623A CN101122623A CNA200710121781XA CN200710121781A CN101122623A CN 101122623 A CN101122623 A CN 101122623A CN A200710121781X A CNA200710121781X A CN A200710121781XA CN 200710121781 A CN200710121781 A CN 200710121781A CN 101122623 A CN101122623 A CN 101122623A
 Authority
 CN
 China
 Prior art keywords
 lightning
 thunder
 thunderbolt
 discharge channel
 electric
 Prior art date
Links
 238000010998 test method Methods 0.000 title claims description 8
 230000005540 biological transmission Effects 0.000 title abstract description 18
 230000005611 electricity Effects 0.000 title description 10
 XEEYBQQBJWHFJMUHFFFAOYSAN iron Chemical compound data:image/svg+xml;base64,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 data:image/svg+xml;base64,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 [Fe] XEEYBQQBJWHFJMUHFFFAOYSAN 0.000 claims abstract description 24
 229910052742 iron Inorganic materials 0.000 claims abstract description 13
 206010042255 Struck by lightning Diseases 0.000 claims description 12
 230000005684 electric field Effects 0.000 claims description 12
 206010021750 Infantile spasms Diseases 0.000 abstract 5
 239000011514 iron Substances 0.000 abstract 2
 239000004020 conductors Substances 0.000 abstract 1
 238000000034 method Methods 0.000 description 5
 238000010586 diagram Methods 0.000 description 2
 238000004088 simulation Methods 0.000 description 2
 230000015556 catabolic process Effects 0.000 description 1
 230000000875 corresponding Effects 0.000 description 1
 230000000694 effects Effects 0.000 description 1
 230000000306 recurrent Effects 0.000 description 1
Abstract
The invention relates to a testing method of antilightening performance parameters of highvoltage transmission system, pertaining to the antilightning technology in the art of electricians. First is to calculate the development probability Pi in i direction of a discharge channel each time, repeat the calculation, a lightning pilot develops forward to get the discharge channel; the second is to respectively calculate the number of lightning attacks on wire, lightning conductor and iron tower; at last, according to the number of lightning attack wires/total number of lightning attacks and the number of lightning attack iron towers/total number of lightning attacks, the attack rate and the counterattack rate are got. The calculation shows that calculating the transmission line by the invention, particularly the attack rate of super and ultrahigh voltage lines is much closer to the actual operational result compared with the traditional rule method and electrical geometric model.
Description
Technical field
The present invention relates to a kind of method of testing, relate in particular to the lightning protection properties test of super, UHV transmission line and transformer station, belong to the electrical field shocking preventing technology antilightening performance parameters.
Background technology
Thunder and lightning is the recurrent a kind of atmospheric discharge phenomenon of nature.It causes significant impact to the operation of electric system.When stronger thunder and lightning transmission line of lightning strike, cause power outage thereby tripping operation generally can take place circuit.Along with the raising of voltage class of electric power system, the height of transmission line of electricity is more and more higher, thus the accident of easy more generation transmission line of lightning strike lead, and this claims thunderbolt in electric system.Transmission line of lightning strike divides counterattack and two kinds of situations of shielding, when be struck by lightning lightning conducter and iron tower cause line tripping, claims counterattack; When the thunderbolt lead causes tripping operation, claim shielding.Generally speaking, shielding is than the easier line tripping that causes of counterattack.Therefore, when line design, wish that generally risk of shielding failure (the shielding number of times/number of times always is struck by lightning) is low, can reduce tripping rate with lightning strike like this.
Corresponding counterattack and shielding have two parameters of describing the line thunder protection performance, claim counterattack tripout rate and shielding tripout rate.The general tripping rate with lightning strike that adopts rules method and electric geometric model to test transmission line of electricity.More or less there are some problems in these methods when being applied to the practical problems analysis, the actual risk of shielding failure of transmission line of electricity is higher than said method, and therefore existing theory can not be explained the shielding problem of transmission line of electricity.After particularly UHV (ultrahigh voltage), extra high voltage line occurred in recent years, along with the raising of electric pressure, electric power line pole tower was more and more higher, and shaft tower is high more, the easy more generation shielding of circuit.Two kinds of traditional methods can't be explained the higher problem of the actual risk of shielding failure of super, extra high voltage line especially.
Summary of the invention
The objective of the invention is method of testing, describe the lightning stroke process of thunder and lightning, manifest the distortion and the multiplelimb phenomenon of nature thunder discharge passage, to test relevant lightning protection properties parameter with existing fractal theory to antilightening performance parameters.
The method of testing to antilightening performance parameters that the present invention proposes may further comprise the steps:
(1) calculates the development probability P of each discharge channel to the i direction
_{i}:
${P}_{i}=\frac{{\left({E}_{i}\right)}^{\mathrm{\η}}}{\underset{n}{\mathrm{\Σ}}{\left({E}_{i}\right)}^{\mathrm{\η}}}$
Wherein, E
_{i}Be the electric field intensity of i direction, adopt method of finite difference (Finite Difference Method) by finding the solution the current potential Laplce of band edge circle condition
^{2}=0 equation obtains, and η is the factor of influence of ambient atmosphere electric field to the thunder and lightning path, between 05;
(2) repeating step (1), thunder and lightning the guide advance, and obtains discharge channel;
(3) calculate the number of times that thunder and lightning hits lead, lightning conducter and iron tower respectively;
(4) according to the thunderbolt lead number of times/number of times that always is struck by lightning, obtain risk of shielding failure;
(5) according to the thunderbolt iron tower number of times/number of times that always is struck by lightning, obtain risk of flashback.
The method of testing to antilightening performance parameters that the present invention proposes, its advantage is to describe the lightning stroke process of thunder and lightning with fractal theory, more meets the actual conditions of thunderbolt.By changing the parameter in fractal, change the shape and the degreeof tortuosity of thunderbolt passage, the thunderbolt point when determining the thunderbolt circuit, thus obtain the thunderbolt rate of transmission line of electricity.Calculating shows, adopts method computing electric power line of the present invention, and the risk of shielding failure of particularly super, extra high voltage line more approaches The actual running results than traditional rules method and electric geometric model.
Description of drawings
Fig. 1 is the transmission line of electricity synoptic diagram.
Fig. 2 is the constitutional diagram of thunder and lightning guide during near ground.
Embodiment
The method of testing to antilightening performance parameters that the present invention proposes may further comprise the steps:
(1) calculates the development probability P of each discharge channel to the i direction
_{i}:
${P}_{i}=\frac{{\left({E}_{i}\right)}^{\mathrm{\η}}}{\underset{n}{\mathrm{\Σ}}{\left({E}_{i}\right)}^{\mathrm{\η}}}$
Wherein, E
_{i}Be the electric field intensity of i direction, adopt method of finite difference (Finite Difference Method) by finding the solution the current potential Laplce of band edge circle condition
^{2}=0 equation obtains, and η is the factor of influence of ambient atmosphere electric field to the thunder and lightning path, between 05;
(2) repeating step (1), thunder and lightning the guide advance, and obtains discharge channel;
(3) calculate the number of times that thunder and lightning hits lead, lightning conducter and iron tower respectively;
(4) according to the thunderbolt lead number of times/number of times that always is struck by lightning, obtain risk of shielding failure;
(5) according to the thunderbolt iron tower number of times/number of times that always is struck by lightning, obtain risk of flashback.
The present invention introduces the simulation of thunder discharge with fractal theory, has shown the distortion and the bifurcation of thunder discharge passage better.By changing fractal coefficient, the thunder discharge phenomenon of different torsion resistances and different branches can be described.
On this basis, use this method in the Analysis of Lightning Stroke of actual transmission line of electricity.
The principle of the inventive method is as follows: describe the passage of thunder discharge with fractal theory, the developing direction of each discharge is determined by following formula:
In the formula, P
_{i}Be the development probability of discharge channel to the i direction, E
_{i}Be the electric field intensity of i direction, by finding the solution current potential Laplce (Laplace) of band edge circle condition
^{2}=0 equation obtains, and η is the factor of influence of ambient atmosphere electric field to the thunder and lightning path, between 05.
By changing factor of influence in the fractal expression formula (change the factor and characterize ambient atmosphere electric field that thundercloud causes influence degree) to the thunder and lightning path, can change the torsion resistance and the bifurcated situation of thunder discharge passage, can be according to the observation during actual value and the fractal dimension that calculates the actual discharge photo determine.Situation with this method research transmission line of lightning strike, thinking is: according to boundary condition, current potential as thundercloud, (Finite Difference Method) finds the solution the Laplace equation with method of finite difference, obtain the electric field intensity of all directions, determine discharge guide developing direction according to formula (1) then, like this, advance step by step, obtain discharge channel shown in Figure 2.When the thunder and lightning passage is overhead higher, ground situation does not influence the development of thunder and lightning passage, and when thunder and lightning guide head closely during face, the object of differing heights, different ground connection situations will influence thunder and lightning guide's developing direction on the ground, when the electric field on the ground between certain object and the guide's head reaches the atmosphere breakdown field strength, the incident of this object of being struck by lightning this moment has just taken place, thereby the ground lightning strike spot of current thunderbolt has also just been determined.Said process is applied to transmission line of electricity, and the lightning stroke process of particularly super, UHV transmission line just can be determined to be struck by lightning in iron tower, ground, still is struck by lightning in lead, lightning conducter.By hundreds of times calculating, the size of risk of shielding failure in the time of just can analyzing this circuit of thunderbolt, thus can improve the iron tower shape, thus risk of shielding failure reduced.
The inventive method adopts the discharge process of fractal theory simulation thunder and lightning, and this method be applied to surpass, performance parameters such as the risk of shielding failure of extra high voltage line and shielding tripout rate calculate; By changing the complicacy that some factors in fractal change the thunder discharge passages.Adopt the inventive method can test the lightning protection effect of different transmission lines of electricity, the gained result more approaches The actual running results than traditional rules method and electric geometric model.
As an example, the present invention is that the iron tower of h=30m calculates to height shown in Figure 1, supposes thundercloud height H=300m.Fig. 2 is the situation of thunder and lightning guide during near ground.The result is as follows: simulated 100 thunderbolts altogether, the thunderbolt iron tower is wherein arranged 25 times, 65 thunderbolt lightning conducters, 10 thunderbolt leads, thereby obtain this circuit shielding incidence=thunderbolt lead number of times/number of times=10/100=10% always is struck by lightning, by calculating, just can obtain the shielding tripout rate of this circuit to whole circuit thunderbolt number of times.
Claims (1)
1. method of testing to antilightening performance parameters is characterized in that method may further comprise the steps:
(1) calculates the development probability P of each discharge channel to the i direction
_{i}:
${P}_{i}=\frac{{\left({E}_{i}\right)}^{\mathrm{\η}}}{\underset{n}{\mathrm{\Σ}}{\left({E}_{i}\right)}^{\mathrm{\η}}}$
Wherein, E
_{i}Be the electric field intensity of i direction, adopt method of finite difference (Finite Difference Method) by finding the solution the current potential Laplce of band edge circle condition
^{2}=0 equation obtains, and η is the factor of influence of ambient atmosphere electric field to the thunder and lightning path, between 05;
(2) repeating step (1), thunder and lightning the guide advance, and obtains discharge channel;
(3) calculate the number of times that thunder and lightning hits lead, lightning conducter and iron tower respectively;
(4) according to the thunderbolt lead number of times/number of times that always is struck by lightning, obtain risk of shielding failure;
(5) according to the thunderbolt iron tower number of times/number of times that always is struck by lightning, obtain risk of flashback.
Priority Applications (1)
Application Number  Priority Date  Filing Date  Title 

CNB200710121781XA CN100498357C (en)  20070914  20070914  High voltage electricity transmission system thunderproof property parameter test method 
Applications Claiming Priority (1)
Application Number  Priority Date  Filing Date  Title 

CNB200710121781XA CN100498357C (en)  20070914  20070914  High voltage electricity transmission system thunderproof property parameter test method 
Publications (2)
Publication Number  Publication Date 

CN101122623A true CN101122623A (en)  20080213 
CN100498357C CN100498357C (en)  20090610 
Family
ID=39085042
Family Applications (1)
Application Number  Title  Priority Date  Filing Date 

CNB200710121781XA CN100498357C (en)  20070914  20070914  High voltage electricity transmission system thunderproof property parameter test method 
Country Status (1)
Country  Link 

CN (1)  CN100498357C (en) 
Cited By (5)
Publication number  Priority date  Publication date  Assignee  Title 

CN101290336B (en) *  20080618  20100602  昆明理工大学  Alternatingcurrent powerline thunderbolt shielding failure and counterattack recognition method 
CN102637219A (en) *  20120302  20120815  清华大学  Lightning fractal method based on charge simulation method and finite difference method in power system 
CN103809076A (en) *  20121109  20140521  国家电网公司  Power transmission line fault processing method and device 
CN104897977A (en) *  20140307  20150909  武汉三相电力科技有限公司  Power transmission line lightning stroke frequency direct monitoring method 
CN106680632A (en) *  20161230  20170517  杭州后博科技有限公司  Iron tower lightning protection performance detection method based on electromagnetic radiation abnormity determination and system 
Family Cites Families (4)
Publication number  Priority date  Publication date  Assignee  Title 

CN2336493Y (en) *  19980210  19990901  江西省电力通信公司  Lightning protection device for transmission lines 
CN2404248Y (en) *  19991216  20001101  成都星河科技产业有限公司  Special lightningprotection & arc extinguishing device for highvoltage transmission line 
CN100361123C (en) *  20051028  20080109  清华大学  Whole line and multiparameter integrated optimizing method for determining lightningproof performance of power transmission line 
CN100468072C (en) *  20060714  20090311  华北电力大学  Highvoltage transmission line lightning stroke flashover path detection method 

2007
 20070914 CN CNB200710121781XA patent/CN100498357C/en not_active IP Right Cessation
Cited By (8)
Publication number  Priority date  Publication date  Assignee  Title 

CN101290336B (en) *  20080618  20100602  昆明理工大学  Alternatingcurrent powerline thunderbolt shielding failure and counterattack recognition method 
CN102637219A (en) *  20120302  20120815  清华大学  Lightning fractal method based on charge simulation method and finite difference method in power system 
CN103809076A (en) *  20121109  20140521  国家电网公司  Power transmission line fault processing method and device 
CN103809076B (en) *  20121109  20170315  国家电网公司  Transmission line malfunction processing method and processing device 
CN104897977A (en) *  20140307  20150909  武汉三相电力科技有限公司  Power transmission line lightning stroke frequency direct monitoring method 
CN104897977B (en) *  20140307  20180202  武汉三相电力科技有限公司  A kind of direct monitoring method of transmission line lightning stroke frequency 
CN106680632A (en) *  20161230  20170517  杭州后博科技有限公司  Iron tower lightning protection performance detection method based on electromagnetic radiation abnormity determination and system 
CN106680632B (en) *  20161230  20210108  杭州后博科技有限公司  Iron tower lightning protection performance detection method and system based on electromagnetic radiation abnormity judgment 
Also Published As
Publication number  Publication date 

CN100498357C (en)  20090610 
Similar Documents
Publication  Publication Date  Title 

US9360352B2 (en)  Method for determining lightning hazard distribution of power network  
CN101315400B (en)  Electric power line lightning protection performance estimation method based on thunder and lightning parametric statistics  
CN105548819B (en)  A kind of HVDC transmission line internal fault external fault recognition methods based on antitraveling wave  
CN102854415B (en)  Method for assessing lightning flashover risks of regional power grid lines  
CN101345415B (en)  Travelling wave analysis recognition method for thunderbolt shielding failure and counterattack discrimination of direct current transmission line  
CN102565628B (en)  Method for identifying properties of lightning faults of overhead line on basis of amplitude interval distribution of lightning current  
CN101242098B (en)  Thunder failure recognition method for row wave protection of DC power transmission line  
CN104155526B (en)  A kind of method for measuring the electric power line pole tower earthing or grounding means Transient grounding resistance with lightning conducter  
EP2423499A1 (en)  Lightning protection for wind turbines  
CN107255743B (en)  A kind of extra high voltage direct current transmission line lightning fault recognition methods based on power spectrum similarity  
Taniguchi et al.  Flashover characteristics of long air gaps with negative switching impulses  
CN106099753B (en)  Weight icecovering area without lightning conducter Transmission Line Design method  
CN101290337B (en)  High voltage direct current transmission line thunderbolt shielding failure and counterattack recognition method  
CN103236666B (en)  Transmission line located lightening arresting method  
CN104111393A (en)  Comprehensive evaluation analysis method for power transformer shortcircuiting resistance  
CN106199354A (en)  Insulator chain parallel connection gaps lightning impulse effectiveness and flashover characteristic method of testing  
CN101499638B (en)  Method for improving lightning protection capability of ultra extrahigh voltage transmission line  
CN105067951B (en)  T link singlephase ground fault distance measuring methods based on many time section informations  
CN102820643A (en)  High voltage direct current power transmission line protection method based on voltage and current mutation direction  
CN102426305B (en)  Power grid thunder damage risk evaluation method  
CN102435921B (en)  The decision method of same tower double back transmission line insulation and resistance to lightning impulse performance  
Radičević et al.  Impact of wind turbine blade rotation on the lightning strike incidence–A theoretical and experimental study using a reducedsize model  
CN103594931A (en)  Active type microwave induction lightning protection system  
CN107992962B (en)  Power transmission line lightning protection measure optimal selection method based on entropy weight method  
CN100361123C (en)  Whole line and multiparameter integrated optimizing method for determining lightningproof performance of power transmission line 
Legal Events
Date  Code  Title  Description 

PB01  Publication  
C06  Publication  
SE01  Entry into force of request for substantive examination  
C10  Entry into substantive examination  
GR01  Patent grant  
C14  Grant of patent or utility model  
CF01  Termination of patent right due to nonpayment of annual fee 
Granted publication date: 20090610 Termination date: 20180914 

CF01  Termination of patent right due to nonpayment of annual fee 