CN104361250A  Photovoltaic grid connected safety evaluation method  Google Patents
Photovoltaic grid connected safety evaluation method Download PDFInfo
 Publication number
 CN104361250A CN104361250A CN201410689866.8A CN201410689866A CN104361250A CN 104361250 A CN104361250 A CN 104361250A CN 201410689866 A CN201410689866 A CN 201410689866A CN 104361250 A CN104361250 A CN 104361250A
 Authority
 CN
 China
 Prior art keywords
 evaluation
 index
 photovoltaic
 matrix
 voltage
 Prior art date
 Legal status (The legal status is an assumption and is not a legal conclusion. Google has not performed a legal analysis and makes no representation as to the accuracy of the status listed.)
 Pending
Links
 238000011156 evaluation Methods 0.000 title claims abstract description 90
 239000011159 matrix material Substances 0.000 claims abstract description 58
 238000000034 method Methods 0.000 claims abstract description 48
 230000000875 corresponding Effects 0.000 claims abstract description 4
 241000036569 Carp sprivivirus Species 0.000 claims description 12
 238000004458 analytical method Methods 0.000 claims description 3
 238000004364 calculation method Methods 0.000 claims description 3
 230000001105 regulatory Effects 0.000 claims description 3
 238000010248 power generation Methods 0.000 abstract description 3
 238000004445 quantitative analysis Methods 0.000 description 3
 238000004451 qualitative analysis Methods 0.000 description 2
 230000000052 comparative effect Effects 0.000 description 1
 238000010586 diagram Methods 0.000 description 1
 235000013399 edible fruits Nutrition 0.000 description 1
 238000005516 engineering process Methods 0.000 description 1
 230000001737 promoting Effects 0.000 description 1
 238000004064 recycling Methods 0.000 description 1
Abstract
The invention discloses a photovoltaic grid connected safety evaluation method, which comprises the following steps of step 1, selecting a photovoltaic power station grid connected safety evaluation index, and building an evaluation matrix according to the index; step 2, carrying out index syntropy processing and dimensionless processing on the evaluation matrix to obtain a standard evaluation matrix; step 3, confirming the evaluation matrix and an index weight vector based on an analytic hierarchy process; step 4, utilizing a method of distance of goodbad solutions to calculate relative proximity corresponding to each photovoltaic power station, and realizing comprehensive evaluation on photovoltaic power station grid connected safety through sorting of the relative proximities. The photovoltaic grid connected safety evaluation method can comprehensively and objectively evaluate the safety running conditions of the photovoltaic power station grid connection, and provides the evaluation basis for the photovoltaic power generation grid connected safety conditions for an electric power department.
Description
Technical field
The invention belongs to gridconnected safety evaluatio technical field, relate to a kind of gridconnected method for evaluating safety, be specifically related to a kind of based on analytical hierarchy process and the good and bad gridconnected method for evaluating safety separating Furthest Neighbor.
Background technology
Development distributed photovoltaic power generation, to optimizing China's energy structure, realizing energy supply diversification, tackle climate change, preserve the ecological environment, promoting that the sustainable development of socioeconomy has a very important role, is also the basic demand of implementing a scientific outlook on development, building a resourceconserving society simultaneously.From fast development and the photovoltaic plant high accident rate of solar energy power generating, the security of Solar use is very important.The security of Solar use not only can make a big impact to operation of power networks economy, and can limit the development of photovoltaic generation to a certain extent.Meanwhile, due to the intermittence of photovoltaic generation and the otherness of regional sun power, the security of different photovoltaic electric station grid connection is difficult to compare.
Summary of the invention
For the deficiencies in the prior art, the object of this invention is to provide a kind of based on analytical hierarchy process and the good and bad gridconnected method for evaluating safety separating Furthest Neighbor, the method evaluates the safe operation situation of photovoltaic electric station grid connection comprehensively, objectively, for power department provides Appreciation gist to photovoltaic power generation gridconnecting safety conditions.
The technical solution adopted in the present invention is: a kind of gridconnected method for evaluating safety, is characterized in that, comprise the following steps:
Step 1: choose photovoltaic electric station grid connection Safety Evaluation Index, according to this Index Establishment Evaluations matrix;
Step 2: index is carried out to Evaluations matrix and changes process in the same way and go dimension process, obtain standard evaluation matrix;
Step 3: based on analytical hierarchy process determination Evaluations matrix and index weights vector;
Step 4: utilize good and bad Furthest Neighbor of separating to calculate relative proximities corresponding to each photovoltaic plant, and realize the comprehensive evaluation to photovoltaic electric station grid connection security by the sequence of relative proximities.
As preferably, the photovoltaic electric station grid connection Safety Evaluation Index described in step 1 comprises photovoltaic and to dissolve capacity limit, shortcircuit current rate of growth, percent harmonic distortion, rate of qualified voltage, voltage fluctuation rate, SVC/SVG dynamic response performance; Wherein:
(1) photovoltaic is dissolved capacity: be incorporated into the power networks to realize distributed photovoltaic power plant safety, national grid has made relevant regulations to the photovoltaic capacity of dissolving; Wherein singlepoint photovoltaic capacity of dissolving is determined according to distributed photovoltaic modular design criterion; When photovoltaic T connects, the photovoltaic capacity of each circuit no more than circuit with peak load 60%, when photovoltaic adopts access via telephone line, its capacity adopts the 6MW specified in modular design; The substation photovoltaic capacity of dissolving must not exceed 25% of substation's band peak load;
(2) shortcircuit current rate of growth: grid short circuit electric current Growth Rate Calculation formula is as follows
Wherein, I
_{aE}for shortcircuit current before photovoltaic access; I
_{bE}for shortcircuit current after photovoltaic access; I
_{uP}% is shortcircuit current rate of growth;
(3) percent harmonic distortion: the computing formula of percent harmonic distortion is as follows
Wherein U
_{b}for voltage total harmonic distortion, THD is percent harmonic distortion, U
_{1}for fundamental voltage effective value, U
_{n}for each harmonic voltage effective value, n gets infinity from 2;
(4) rate of qualified voltage: the computing formula of rate of qualified voltage is as follows
Wherein, U% represents rate of qualified voltage; T
_{1}represent the voltage overtime; T
_{2}represent voltage detecting T.T.;
(5) voltage fluctuation rate: the computing formula of voltage fluctuation rate is as follows
Wherein,  U
_{t} represent the absolute value of voltage fluctuation difference, U
_{0}represent voltage duration, U
_{v}% represents voltage fluctuation rate;
(6) SVC/SVG dynamic response performance: according to and the change in voltage of site, judge that can dynamic reactive compensation device SVC/SVG meet regulatory requirements in the continuous working period after change in voltage; Record the situation up to standard of reactive power compensator in month, can realize the evaluation to reactive power compensator in month, evaluation index RP is: RP=G/H; Wherein RP represents compliance rate, and G represents the number of times up to standard in the unit interval, and H represents the total degree that needs compensate.
As preferably, described in step 1, set up Evaluations matrix, its Evaluations matrix Y=(Y
_{1}, Y
_{2}, Y
_{3}, Y
_{4}, Y
_{5}, Y
_{6}), Y
_{1}for photovoltaic is dissolved capacity limit, Y
_{2}for shortcircuit current rate of growth, Y
_{3}for percent harmonic distortion, Y
_{4}for rate of qualified voltage, Y
_{5}for voltage fluctuation rate, Y
_{6}for SVC/SVG dynamic response performance.
As preferably, carrying out index to Evaluations matrix and change process in the same way described in step 2, its specific implementation process is first structural matrix Y '=(y
_{ij})
_{m × n}, wherein m is the number of evaluation index, and n evaluates individual number; Because shortcircuit current rate of growth, percent harmonic distortion, voltage fluctuation rate are negative index, therefore process is changed in the same way to it be converted into direct index; The computing formula that negative index is converted into direct index is as follows:
Wherein, y
_{ij}represent the matrix element carrying out index and change in the same way, maxY
_{i}represent indicator vector Y
_{i}the maximal value of middle element, k value gets 0.1.
Evaluation index is divided three classes: direct index, negative index and interval index, and direct index represents that desired value larger reflection situation is more excellent; Negative index expression index larger reflection situation is more excellent; Interval index expression index situation in specified scope is optimum.
As preferably, go dimension process described in step 2 to Evaluations matrix, its detailed process is to matrix Y '
_{i}carry out nondimensionalization process, turn to canonical matrix Y "
_{i}; Wherein carry out the matrix element y of dimension process "
_{ij}account form is as follows
As preferably, described in step 3 based on analytical hierarchy process determination Evaluations matrix and index weights vector, its specific implementation comprises following substep:
Step 3.1: determine target and factor of evaluation: choose 6 evaluation indexes that photovoltaic plant runs, then evaluation vector u={u
_{1}, u
_{2}..., u
_{6}; u
_{1}, u
_{2}..., u
_{6}represent the evaluation index of 6 described in step 1 respectively;
Step 3.2: Judgement Matricies S=(u
_{ij})
_{p × p}, wherein p is index number;
Step 3.3: the Maximum characteristic root λ calculating judgment matrix S
_{max}, and characteristic of correspondence vector A, proper vector A are the importance ranking of a factor of evaluation, are an evaluation criterion weight and distribute;
Step 3.4: the consistency check of judgment matrix S; Determine coincident indicator CI=(λ
_{max}n)/(n1) and Average Random Consistency Index RI, the i.e. average of CI; When random Consistency Ratio
time, then the result of step analysis sequence meets consistance, and each judge index weight allocation is rational; Otherwise, again to redistribute each index weights to the evaluation element value of judgment matrix.
As preferably, quality solution Furthest Neighbor described in step 4 refers to determines reference point in space, comprising optimum point and the most bad point, then calculates the distance of each evaluation object and reference point, higher with the nearlyer security of optimum point, higher with the security far away of the most bad distance; Calculate the relative proximities of sample point to optimum sample point according to quality solution Furthest Neighbor, realize the evaluation to gridconnected security finally by the relative proximities sequence calculated, relative proximities solves as follows:
Relative proximities C
_{j}calculating formula:
Wherein, C
_{j}represent the relative proximities of sample point to optimum sample point;
represent the distance of sample point to the most bad point;
represent the distance of sample point to optimum point;
After utilizing Weight of Coefficient through Analytic Hierarchy Process, according to following formula determination weighted data matrix Y " ':
Y″′＝Y″
_{i}·ω
_{i},i＝1,2…m
Wherein, ω
_{i}represent the weight of each evaluation index;
Form optimum ideal sample by the maximal value of evaluation index each in all samples, form the most bad ideal sample by the minimum value of an evaluation index, use Y respectively
^{+}and Y
^{}represent:
Sample is to the distance of optimum point
${D}_{j}^{+}=\sqrt{\underset{i=1}{\overset{m}{\mathrm{\Σ}}}{({y}_{\mathrm{ij}}{y}_{i}^{+})}^{2}},j=\mathrm{1,2},...n$
Sample is to the distance of the most bad point
${D}_{j}^{}=\sqrt{\underset{i=1}{\overset{m}{\mathrm{\Σ}}}{({y}_{\mathrm{ij}}{y}_{i}^{})}^{2}},j=\mathrm{1,2},...n$
According to relative proximities C
_{j}size each evaluation object is sorted, C
_{j}the relative distance of larger expression evaluation object and ideal sample is less, and evaluation result is better.
Compared with the prior art, advantage of the present invention is:
1, the present invention proposes analytical hierarchy process to be used for the weight calculating gridconnected safe operation index.Gridconnected safe operation index is divided into some levels by the method, and judgement is compared to the significance level between two two indexes, after setting up judgment matrix, obtain by the proper vector and eigenvalue of maximum calculating judgment matrix the weight phasor reflecting different index significance level.Analytical hierarchy process is by organically combining quantitative analysis method and method for qualitative analysis, and quantitative test goes out the influence degree of each index to evaluation result exactly, and algorithm is simply clear and definite and practical;
2, quality is separated the comprehensive evaluation that Furthest Neighbor is used for realizing gridconnected safe operation situation by the present invention's proposition.The method, by determining reference point at higher dimensional space, comprises optimum point and the most bad point, then calculates the distance of each evaluation object index and optimum point or the most bad point.The distance of gridconnected Safety Evaluation Index and optimum point is less or larger with the distance of the most bad point, illustrates that to be evaluated gridconnected combination property more excellent, otherwise poorer.Finally, gained distance is utilized to calculate the relative proximities of sample point to optimum sample point, and then by realizing the comprehensive evaluation of Operation of Wind Power Plant to degree of closeness sequence.Good and bad Furthest Neighbor of separating is weighted process according to the overlaps of index to it, be applicable to dynamic and the relativity feature of different photovoltaic electric station grid connection runnability, therefore the method can determine quantitative analysis foundation for the evaluation comparison of different photovoltaic electric station grid connection performance provides;
3, the gridconnected method for evaluating safety based on analytical hierarchy process and good and bad solution Furthest Neighbor provided by the invention evaluates gridconnected safe operation situation comprehensively, objectively, provides Appreciation gist for power department carries out Integrated comparative to photovoltaic plant ruuning situation.
Accompanying drawing explanation
Fig. 1: be process flow diagram of the present invention.
Embodiment
Understand for the ease of those of ordinary skill in the art and implement the present invention, below in conjunction with drawings and Examples, the present invention is described in further detail, should be appreciated that exemplifying embodiment described herein is only for instruction and explanation of the present invention, is not intended to limit the present invention.
Analytical hierarchy process (be called for short AHP) is filled in the base of a fruit 20 century 70 midterms formally proposed by the U.S. scholar Thomas that plans strategies for, it is that a kind of quantitative and qualitative analysis combines, systematization, stratification analytical approach.The method is divided into each factor in challenge some levels of interkniting and makes it methodization, according to the fuzzy Judgment to objective reality, with regard to the expression of the relative importance quantitative of each level, recycling mathematical method determines the weight of whole element relative importance order.Due to the practicality in the decision problem of process complexity and validity, it is applied in multiple field.
Good and bad solution Furthest Neighbor regards evaluation object as the variable on coordinate, geometrically forming one with evaluation object index for coordinate axis sunlight higher dimensional space, each point being evaluated to as if being determined in this space by its multiple desired values of reflection viewed from geometric angle, by comparing to these spatial point and optimum point or the most bad some distance the comprehensive evaluation realized being evaluated object.The optimal value of index is the desirable level of evaluation this index interior in period, the relative superior or inferior degree of each operating index of wind energy turbine set can be judged by the difference calculating gridconnected security operating index value and desirable level, and then can according to the comprehensive evaluation of indices situation realization to gridconnected security situation.
Ask for an interview Fig. 1, provided by the invention based on analytical hierarchy process and the good and bad gridconnected method for evaluating safety separating Furthest Neighbor, comprise the steps:
Step 1: choose photovoltaic electric station grid connection Safety Evaluation Index, according to this Index Establishment Evaluations matrix;
Wherein photovoltaic electric station grid connection Safety Evaluation Index comprises photovoltaic and to dissolve capacity limit, shortcircuit current rate of growth, percent harmonic distortion, rate of qualified voltage, voltage fluctuation rate, SVC/SVG dynamic response performance; Wherein:
(1) photovoltaic is dissolved capacity: be incorporated into the power networks to realize distributed photovoltaic power plant safety, national grid has made relevant regulations to the photovoltaic capacity of dissolving; Wherein singlepoint photovoltaic capacity of dissolving is determined according to distributed photovoltaic modular design criterion; When photovoltaic T connects, the photovoltaic capacity of each circuit no more than circuit with peak load 60%, when photovoltaic adopts access via telephone line, its capacity adopts the 6MW specified in modular design; The substation photovoltaic capacity of dissolving must not exceed 25% of substation's band peak load;
(2) shortcircuit current rate of growth: grid short circuit electric current Growth Rate Calculation formula is as follows
Wherein, I
_{aE}for shortcircuit current before photovoltaic access; I
_{bE}for shortcircuit current after photovoltaic access; I
_{uP}% is shortcircuit current rate of growth;
(3) percent harmonic distortion: the computing formula of percent harmonic distortion is as follows
Wherein U
_{b}for voltage total harmonic distortion, THD is percent harmonic distortion, U
_{1}for fundamental voltage effective value, U
_{n}for each harmonic voltage effective value, n gets infinity from 2;
(4) rate of qualified voltage: the computing formula of rate of qualified voltage is as follows
Wherein, U% represents rate of qualified voltage; T
_{1}represent the voltage overtime; T
_{2}represent voltage detecting T.T.;
(5) voltage fluctuation rate: the computing formula of voltage fluctuation rate is as follows
Wherein,  U
_{t} represent the absolute value of voltage fluctuation difference, U
_{0}represent voltage duration, U
_{v}% represents voltage fluctuation rate;
(6) SVC/SVG dynamic response performance: according to and the change in voltage of site, judge that can dynamic reactive compensation device SVC/SVG meet regulatory requirements in the continuous working period after change in voltage; Record the situation up to standard of reactive power compensator in month, can realize the evaluation to reactive power compensator in month, evaluation index RP is: RP=G/H; Wherein RP represents compliance rate, and G represents the number of times up to standard in the unit interval, and H represents the total degree that needs compensate.
Its Evaluations matrix Y=(Y
_{1}, Y
_{2}, Y
_{3}, Y
_{4}, Y
_{5}, Y
_{6}), Y
_{1}for photovoltaic is dissolved capacity limit, Y
_{2}for shortcircuit current rate of growth, Y
_{3}for percent harmonic distortion, Y
_{4}for rate of qualified voltage, Y
_{5}for voltage fluctuation rate, Y
_{6}for SVC/SVG dynamic response performance.
Step 2: index is carried out to Evaluations matrix and changes process in the same way and go dimension process, obtain standard evaluation matrix;
Wherein carry out index to Evaluations matrix and change process in the same way, its specific implementation process is first structural matrix Y '=(y
_{ij})
_{m × n}, wherein m is the number of evaluation index, and n evaluates individual number; Because shortcircuit current rate of growth, percent harmonic distortion, voltage fluctuation rate are negative index, therefore process is changed in the same way to it be converted into direct index; The computing formula that negative index is converted into direct index is as follows:
Wherein, y
_{ij}represent the matrix element carrying out index and change in the same way, maxY
_{i}represent indicator vector Y
_{i}the maximal value of middle element, k value gets 0.1.
Evaluation index is divided three classes: direct index, negative index and interval index, and direct index represents that desired value larger reflection situation is more excellent; Negative index expression index larger reflection situation is more excellent; Interval index expression index situation in specified scope is optimum.
Wherein go dimension process to Evaluations matrix, its detailed process is to matrix Y '
_{i}carry out nondimensionalization process, turn to canonical matrix Y "
_{i}; Wherein carry out the matrix element y of dimension process "
_{ij}account form is as follows
Step 3: based on analytical hierarchy process determination Evaluations matrix and index weights vector; Its specific implementation comprises following substep:
Step 3.1: determine target and factor of evaluation: choose 6 evaluation indexes that photovoltaic plant runs, then evaluation vector u={u
_{1}, u
_{2}..., u
_{6}; u
_{1}, u
_{2}..., u
_{6}represent the evaluation index of 6 described in step 1 respectively;
Step 3.2: Judgement Matricies S=(u
_{ij})
_{p × p}, wherein p is index number;
Step 3.3: the Maximum characteristic root λ calculating judgment matrix S
_{max}, and characteristic of correspondence vector A, proper vector A are the importance ranking of a factor of evaluation, are an evaluation criterion weight and distribute;
Step 3.4: the consistency check of judgment matrix S; Determine coincident indicator CI=(λ
_{max}n)/(n1) and Average Random Consistency Index RI, the i.e. average of CI; When random Consistency Ratio
time, then the result of step analysis sequence meets consistance, and each judge index weight allocation is rational; Otherwise, again to redistribute each index weights to the evaluation element value of judgment matrix.
Step 4: utilize good and bad Furthest Neighbor of separating to calculate relative proximities corresponding to each photovoltaic plant, and realize the comprehensive evaluation to photovoltaic electric station grid connection security by the sequence of relative proximities;
Good and bad solution Furthest Neighbor refers to determines reference point in space, comprising optimum point and the most bad point, then calculates the distance of each evaluation object and reference point, higher with the nearlyer security of optimum point, higher with the security far away of the most bad distance; Calculate the relative proximities of sample point to optimum sample point according to quality solution Furthest Neighbor, realize the evaluation to gridconnected security finally by the relative proximities sequence calculated, relative proximities solves as follows:
Relative proximities C
_{j}calculating formula:
Wherein, C
_{j}represent the relative proximities of sample point to optimum sample point;
represent the distance of sample point to the most bad point;
represent the distance of sample point to optimum point;
After utilizing Weight of Coefficient through Analytic Hierarchy Process, according to following formula determination weighted data matrix Y " ':
Y″′＝Y″
_{i}·ω
_{i},i＝1,2…m
Wherein, ω
_{i}represent the weight of each evaluation index;
Form optimum ideal sample by the maximal value of evaluation index each in all samples, form the most bad ideal sample by the minimum value of an evaluation index, use Y respectively
^{+}and Y
^{}represent:
Sample is to the distance of optimum point
${D}_{j}^{+}=\sqrt{\underset{i=1}{\overset{m}{\mathrm{\Σ}}}{({y}_{\mathrm{ij}}{y}_{i}^{+})}^{2}},j=\mathrm{1,2},...n$
Sample is to the distance of the most bad point
${D}_{j}^{}=\sqrt{\underset{i=1}{\overset{m}{\mathrm{\Σ}}}{({y}_{\mathrm{ij}}{y}_{i}^{})}^{2}},j=\mathrm{1,2},...n$
According to relative proximities C
_{j}size each evaluation object is sorted, C
_{j}the relative distance of larger expression evaluation object and ideal sample is less, and evaluation result is better.
In test process, the present invention have selected some typical light overhead utilities data that are incorporated into the power networks and has carried out a large amount of tests.Can be found out by test result, propose the effective evaluation that can realize gridconnected security based on analytical hierarchy process and the good and bad gridconnected method for evaluating safety separating Furthest Neighbor.
Should be understood that, the part that this instructions does not elaborate all belongs to prior art.
Should be understood that; the abovementioned description for preferred embodiment is comparatively detailed; therefore the restriction to scope of patent protection of the present invention can not be thought; those of ordinary skill in the art is under enlightenment of the present invention; do not departing under the ambit that the claims in the present invention protect; can also make and replacing or distortion, all fall within protection scope of the present invention, request protection domain of the present invention should be as the criterion with claims.
Claims (7)
1. a gridconnected method for evaluating safety, is characterized in that, comprises the following steps:
Step 1: choose photovoltaic electric station grid connection Safety Evaluation Index, according to this Index Establishment Evaluations matrix;
Step 2: index is carried out to Evaluations matrix and changes process in the same way and go dimension process, obtain standard evaluation matrix;
Step 3: based on analytical hierarchy process determination Evaluations matrix and index weights vector;
Step 4: utilize good and bad Furthest Neighbor of separating to calculate relative proximities corresponding to each photovoltaic plant, and realize the comprehensive evaluation to photovoltaic electric station grid connection security by the sequence of relative proximities.
2. gridconnected method for evaluating safety according to claim 1, is characterized in that: the photovoltaic electric station grid connection Safety Evaluation Index described in step 1 comprises photovoltaic and to dissolve capacity limit, shortcircuit current rate of growth, percent harmonic distortion, rate of qualified voltage, voltage fluctuation rate, SVC/SVG dynamic response performance; Wherein:
(1) photovoltaic is dissolved capacity: be incorporated into the power networks to realize distributed photovoltaic power plant safety, singlepoint photovoltaic capacity of dissolving is determined according to distributed photovoltaic modular design criterion; When photovoltaic T connects, the photovoltaic capacity of each circuit no more than circuit with peak load 60%, when photovoltaic adopts access via telephone line, its capacity adopts the 6MW specified in modular design; The substation photovoltaic capacity of dissolving must not exceed 25% of substation's band peak load;
(2) shortcircuit current rate of growth: grid short circuit electric current Growth Rate Calculation formula is as follows
Wherein, I
_{aE}for shortcircuit current before photovoltaic access; I
_{bE}for shortcircuit current after photovoltaic access; I
_{uP}% is shortcircuit current rate of growth;
(3) percent harmonic distortion: the computing formula of percent harmonic distortion is as follows
Wherein U
_{b}for voltage total harmonic distortion, THD is percent harmonic distortion, U
_{1}for fundamental voltage effective value, U
_{n}for each harmonic voltage effective value, n gets infinity from 2;
(4) rate of qualified voltage: the computing formula of rate of qualified voltage is as follows
Wherein, U% represents rate of qualified voltage; T
_{1}represent the voltage overtime; T
_{2}represent voltage detecting T.T.;
(5) voltage fluctuation rate: the computing formula of voltage fluctuation rate is as follows
Wherein,  U
_{t} represent the absolute value of voltage fluctuation difference, U
_{0}represent voltage duration, U
_{v}% represents voltage fluctuation rate;
(6) SVC/SVG dynamic response performance: according to and the change in voltage of site, judge that can dynamic reactive compensation device SVC/SVG meet regulatory requirements in the continuous working period after change in voltage; Record the situation up to standard of reactive power compensator in month, can realize the evaluation to reactive power compensator in month, evaluation index RP is: RP=G/H; Wherein RP represents compliance rate, and G represents the number of times up to standard in the unit interval, and H represents the total degree that needs compensate.
3. gridconnected method for evaluating safety according to claim 1, is characterized in that: set up Evaluations matrix, its Evaluations matrix Y=(Y described in step 1
_{1}, Y
_{2}, Y
_{3}, Y
_{4}, Y
_{5}, Y
_{6}), Y
_{1}for photovoltaic is dissolved capacity limit, Y
_{2}for shortcircuit current rate of growth, Y
_{3}for percent harmonic distortion, Y
_{4}for rate of qualified voltage, Y
_{5}for voltage fluctuation rate, Y
_{6}for SVC/SVG dynamic response performance.
4. gridconnected method for evaluating safety according to claim 3, is characterized in that: carrying out index to Evaluations matrix and change process in the same way described in step 2, and its specific implementation process is first structural matrix Y '=(y
_{ij})
_{m × n}, wherein m is the number of evaluation index, and n evaluates individual number; Because shortcircuit current rate of growth, percent harmonic distortion, voltage fluctuation rate are negative index, therefore process is changed in the same way to it be converted into direct index; The computing formula that negative index is converted into direct index is as follows:
Wherein, y
_{ij}represent the matrix element carrying out index and change in the same way, max Y
_{i}represent indicator vector Y
_{i}the maximal value of middle element, k value gets 0.1.
5. gridconnected method for evaluating safety according to claim 4, is characterized in that: go dimension process to Evaluations matrix described in step 2, and its detailed process is to matrix Y '
_{i}carry out nondimensionalization process, turn to canonical matrix Y "
_{i}; Wherein carry out the matrix element y of dimension process "
_{ij}account form is as follows
6. gridconnected method for evaluating safety according to claim 2, is characterized in that: described in step 3 based on analytical hierarchy process determination Evaluations matrix and index weights vector, its specific implementation comprises following substep:
Step 3.1: determine target and factor of evaluation: choose 6 evaluation indexes that photovoltaic plant runs, then evaluation vector u={u
_{1}, u
_{2}..., u
_{6}; u
_{1}, u
_{2}..., u
_{6}represent the evaluation index of 6 described in step 1 respectively;
Step 3.2: Judgement Matricies S=(u
_{ij})
_{p × p}, wherein p is index number;
Step 3.3: the Maximum characteristic root λ calculating judgment matrix S
_{max}, and characteristic of correspondence vector A, proper vector A are the importance ranking of a factor of evaluation, are an evaluation criterion weight and distribute;
Step 3.4: the consistency check of judgment matrix S; Determine coincident indicator CI=(λ
_{max}n)/(n1) and Average Random Consistency Index RI, the i.e. average of CI; When random Consistency Ratio
time, then the result of step analysis sequence meets consistance, and each judge index weight allocation is rational; Otherwise, again to redistribute each index weights to the evaluation element value of judgment matrix.
7. gridconnected method for evaluating safety according to claim 4, it is characterized in that: the quality solution Furthest Neighbor described in step 4 refers to determines reference point in space, comprising optimum point and the most bad point, then the distance of each evaluation object and reference point is calculated, higher with the nearlyer security of optimum point, higher with the security far away of the most bad distance; Calculate the relative proximities of sample point to optimum sample point according to quality solution Furthest Neighbor, realize the evaluation to gridconnected security finally by the relative proximities sequence calculated, relative proximities solves as follows:
Relative proximities C
_{j}calculating formula:
${C}_{j}=\frac{{D}_{j}^{}}{{D}_{j}^{}+{D}_{j}^{+}};$
Wherein, C
_{j}represent the relative proximities of sample point to optimum sample point;
represent the distance of sample point to the most bad point;
represent the distance of sample point to optimum point;
After utilizing Weight of Coefficient through Analytic Hierarchy Process, according to following formula determination weighted data matrix Y " ':
Y″′＝Y″
_{i}·ω
_{i},i＝1,2...m
Wherein, ω
_{i}represent the weight of each evaluation index;
Form optimum ideal sample by the maximal value of evaluation index each in all samples, form the most bad ideal sample by the minimum value of an evaluation index, use Y respectively
^{+}and Y
^{}represent:
Sample is to the distance of optimum point
${D}_{j}^{+}=\sqrt{\underset{i=1}{\overset{m}{\mathrm{\Σ}}}{({y}_{\mathrm{ij}}{y}_{j}^{+})}^{2}},j=\mathrm{1,2},...n$
Sample is to the distance of the most bad point
${D}_{j}^{}=\sqrt{\underset{i=1}{\overset{m}{\mathrm{\Σ}}}{({y}_{\mathrm{ij}}{y}_{i}^{})}^{2}},j=\mathrm{1,2},...n$
According to relative proximities C
_{j}size each evaluation object is sorted, C
_{j}the relative distance of larger expression evaluation object and ideal sample is less, and evaluation result is better.
Priority Applications (1)
Application Number  Priority Date  Filing Date  Title 

CN201410689866.8A CN104361250A (en)  20141125  20141125  Photovoltaic grid connected safety evaluation method 
Applications Claiming Priority (1)
Application Number  Priority Date  Filing Date  Title 

CN201410689866.8A CN104361250A (en)  20141125  20141125  Photovoltaic grid connected safety evaluation method 
Publications (1)
Publication Number  Publication Date 

CN104361250A true CN104361250A (en)  20150218 
Family
ID=52528509
Family Applications (1)
Application Number  Title  Priority Date  Filing Date 

CN201410689866.8A Pending CN104361250A (en)  20141125  20141125  Photovoltaic grid connected safety evaluation method 
Country Status (1)
Country  Link 

CN (1)  CN104361250A (en) 
Cited By (4)
Publication number  Priority date  Publication date  Assignee  Title 

CN108764728A (en) *  20180529  20181106  云南电网有限责任公司  A kind of clean energy resource sends assessment and methods of comparison and selection and the device of scheme outside 
CN109583736A (en) *  20181121  20190405  广西电网有限责任公司  A kind of evaluation method of external electric power in receiving end Electricity Market Competition power 
CN110301664A (en) *  20190717  20191008  安徽中烟工业有限责任公司  A kind of quantitatively characterizing method of tobacco processing line processing intensity 
CN111260239A (en) *  20200122  20200609  长春工程学院  Active power distribution network risk assessment realtime assessment method considering distributed energy 
Citations (4)
Publication number  Priority date  Publication date  Assignee  Title 

CN102073935A (en) *  20101229  20110525  北京理工大学  Universal comprehensive evaluation system and method for customizing evaluation index system thereof 
CN102542347A (en) *  20111228  20120704  东南大学  Method for comprehensively evaluating electric energy quality 
KR20120131842A (en) *  20110526  20121205  대한민국(기상청장)  Site Analysis System and Method for Wind Power 
CN104102840A (en) *  20140716  20141015  国家电网公司  Evaluation method for photovoltaic power receptivity of power distribution network 

2014
 20141125 CN CN201410689866.8A patent/CN104361250A/en active Pending
Patent Citations (4)
Publication number  Priority date  Publication date  Assignee  Title 

CN102073935A (en) *  20101229  20110525  北京理工大学  Universal comprehensive evaluation system and method for customizing evaluation index system thereof 
KR20120131842A (en) *  20110526  20121205  대한민국(기상청장)  Site Analysis System and Method for Wind Power 
CN102542347A (en) *  20111228  20120704  东南大学  Method for comprehensively evaluating electric energy quality 
CN104102840A (en) *  20140716  20141015  国家电网公司  Evaluation method for photovoltaic power receptivity of power distribution network 
NonPatent Citations (5)
Title 

何吉彪 等: "基于两种改进方法的电能质量综合评估", 《电力系统及其自动化学报》 * 
何吉彪: "变电站光伏发电系统的电能质量研究", 《中国优秀硕士学位论文全文数据库 工程科技Ⅱ辑》 * 
张文朝 等: "应用变异系数法和逼近理想解排序法的风电场综合评价", 《电网技术》 * 
李元戎 等: "基于物元分析的火电厂新建机组并网安全性评价", 《山东电力高等专科学校学报》 * 
李英资: "《太阳能光伏并网发电系统设计与应用》", 31 January 2014, 机械工业出版社 * 
Cited By (6)
Publication number  Priority date  Publication date  Assignee  Title 

CN108764728A (en) *  20180529  20181106  云南电网有限责任公司  A kind of clean energy resource sends assessment and methods of comparison and selection and the device of scheme outside 
CN109583736A (en) *  20181121  20190405  广西电网有限责任公司  A kind of evaluation method of external electric power in receiving end Electricity Market Competition power 
CN110301664A (en) *  20190717  20191008  安徽中烟工业有限责任公司  A kind of quantitatively characterizing method of tobacco processing line processing intensity 
CN110301664B (en) *  20190717  20220419  安徽中烟工业有限责任公司  Quantitative characterization method for processing strength of tobacco primary processing line 
CN111260239A (en) *  20200122  20200609  长春工程学院  Active power distribution network risk assessment realtime assessment method considering distributed energy 
CN111260239B (en) *  20200122  20220628  长春工程学院  Active power distribution network risk assessment realtime assessment method considering distributed energy 
Similar Documents
Publication  Publication Date  Title 

CN103426122B (en)  A kind of comprehensive evaluation method of microgrid  
CN103839192B (en)  Wind power plant comprehensive evaluation method based on analytic hierarchy process and comprehensive distance evaluation method  
CN103944175B (en)  Windsolarstorage joint electricity generation system power producing characteristics optimization method  
CN104361250A (en)  Photovoltaic grid connected safety evaluation method  
Zeng et al.  Orderly grid connection of renewable energy generation in China: Management mode, existing problems and solutions  
CN103530817A (en)  Distributed photovoltaic gridconnected adaptability evaluation method  
Adewuyi et al.  Multiobjective mix generation planning considering utilityscale solar PV system and voltage stability: Nigerian case study  
CN104156889A (en)  Wind farm performance evaluation system based on WAMS data and evaluation method thereof  
CN105225074A (en)  A kind of intelligent distribution system lowcarbon (LC) performance synthesis evaluation system  
CN103050985B (en)  A kind of method that wind storage system wide area is distributed rationally  
CN110896231B (en)  Distributed photovoltaic capacity receiving calculation method and system for power distribution network in poverty alleviation area  
CN110363351A (en)  A kind of distributed generation resource access increment power distribution network assessment Method for optimized planning and system  
CN105574632A (en)  Method for evaluating comprehensive benefits of AC/DC hybrid urban distribution network  
Wei et al.  Reliability evaluation of Microgrid with PVWG hybrid system  
CN104852399B (en)  Light stores up the stored energy capacitance dynamic optimization method of microgrid system  
CN107230999B (en)  Regional distributed photovoltaic maximum capacity access evaluation method  
Doukas et al.  Energy storage integration into grid connected utilityscale photovoltaic (PV) systems  
CN106410799A (en)  Addressing method for electromobile charging station suitable for photovoltaic highpermeability power distribution network  
CN106856331A (en)  A kind of gridconnected performance test methods of windlight combined power generation system  
CN108717608A (en)  Million kilowatt beach photovoltaic plant accesses electric network synthetic decisionmaking technique and system  
Hong et al.  A study of evaluation system based on large scale photovoltaic power generation  
CN109102196B (en)  Power distribution network diversified load digestion capacity assessment method and system  
Weihua et al.  Research on the control strategy of largescale wind power energy storage system  
Han et al.  Optimal Sizing Considering Power Uncertainty and Power Supply Reliability Based on LSTM and MOPSO for SWPBMs  
Hong et al.  Energy Storage Application in Improving Distribution Network’s Solar Photovoltaic (PV) Adoption Capability 
Legal Events
Date  Code  Title  Description 

C06  Publication  
PB01  Publication  
C10  Entry into substantive examination  
SE01  Entry into force of request for substantive examination  
RJ01  Rejection of invention patent application after publication 
Application publication date: 20150218 

RJ01  Rejection of invention patent application after publication 