A kind of computer room airflow circulating system
The present invention relates to computer room air circulation technical field, specifically a kind of computer room airflow circulating system.
In IT industry, computer room generally refers to telecommunications, Netcom, movement, two-wire, electric power and government or enterprise etc., storage
Server, the places of service IT are provided for user and employee, tens small square meters are general to place twenty or thirty cabinet, greatly
Square meters up to ten thousand place thousands of a cabinets, it is even more, usually place various servers and minicomputer, such as IBM inside computer room
Minicomputer, HP minicomputers, SUN minicomputers, etc., the temperature and humidity and anti-static precautions of computer room have strict requirements,
Amateur project personnel cannot generally enter, and the server in computer room runs many business, for example, move multimedia message, short disappear
Breath, talk business etc..Computer room is critically important, and without computer room, work, life all can be by extreme influences, so each computer room
There is professional's management, ensures business normal operation.
As computer room（Computer learning room/data center）, its physical environment is strictly controlled, is broadly divided into
Several aspects：That is temperature, power supply, floor, fire prevention system.Mention temperature, generally be all air-conditioning.Idle call controls number
According to the temperature and humidity at center, " the hot criterion of data processing circumstance " suggestion temperature range of Refrigeration ＆ Air-Conditioning engineering association is 20-
25 DEG C (68-75 ℉), humidity range 40-55% are 17 DEG C suitable for the maximum dew-point temperature of data center environment.In data
Heart power can heat air, be excluded from except non-thermal, and otherwise environment temperature will rise, and lead to electronic equipment failure.It is logical
Control air themperature is crossed, server component can be kept within the scope of temperature/humidity as defined in manufacturer.Air-conditioning system passes through cooling
Room air drops to dew point help and controls humidity, and humidity is too big, and water may start to condense on the inner member.If in drying
Environment in, auxiliary humidification system can add vapor, because if humidity is too low, may lead to electrostatic discharge problem, can
It can damage component.The power supply of computer room forms standby electricity by one or more uninterruptible power supplies (UPS) and/or diesel-driven generator
Source.All it is full redundancy in order to avoid there is Single Point of Faliure, all electric system, including stand-by power supply.For server key
For, it to be connected to two power supplys simultaneously, to realize the reliability of N+1 redundant systems.Static switch is used for ensuring sending out sometimes
Moment is switched to another power supply from a power supply when raw power failure.The floor of computer room will promote 60 centimetres with respect to tile floor
(2 feet), this highly becomes higher with social development, is 80-100 centimetres, is uniformly distributed with providing better air-flow.This
Sample air-conditioning system also can be poured into cold air under floor, while also provide more sufficient space for underground power line wiring, existing
The data cable at codes or data center is typically to be laid with via overhead cable disk, but still some people suggest due to safety concerns also
It is that data line should be routed under floor, and consider to increase cooling system.There is no the floor promoted can be in small-sized data center
Without antistatic floor.Computer cabinet is often organized into a passage of heat, so that the efficiency that ventilates is best.Computer room
Fire prevention system include passive and active design, and fire prevention action executive plan.Smoke detector would generally be installed, burnt
Fire alarm can be found in advance before generating open fire, can be blocked power supply before intensity of a fire increase, be put out a fire manually using fire extinguisher.
Data center cannot use automatic sprinkler, because electronic component would generally break down after meeting water, especially
It is that can become even worse using above-water method situation in the case that power supply does not block.Even if being mounted with automatic sprinkler system, cleaning
Gas extinguishing system should also start earlier than automatic sprinkler system.Fire wall should be also installed in data center, it in this way can be with
By burning things which may cause a fire disaster control in subrange, fire, which even occurs, to reduce to minimum by loss, due to being placed with clothes in computer room
Business device so that it is more demanding to the air conditions of computer room when work, it needs to make computer room interior air-flow circulation, ensures that computer room uses
Safety, in the prior art, traditional computer room most air circulatory system are simple and crude, some are only merely to open up a few fan windows, no
Good ventilation is carried out conducive to computer room, air environment is poor, and traditional computer room airflow circulating facility has a single function, Bu Nengman
The present requirement of foot.
The purpose of the present invention is to provide a kind of computer room airflow circulating systems, to solve mentioned above in the background art ask
To achieve the above object, the present invention provides the following technical solutions：
A kind of computer room airflow circulating system, including circulating box, the circulating box are rectangular box body, and circulating box is sealing structure,
Circulating box upper end is equipped with fixed frame, and circulating box is fixed in computer room roof by fixed frame, and fixed frame includes welded plate, welded plate weldering
It is connected on circulating box, support plate is fixed on welded plate, support plate upper end is equipped with connecting plate, connecting hole is housed on connecting plate, is followed
Ring case left end side is equipped with outdoor gas-tpe fitting, and outdoor gas-tpe fitting connects the first air inlet pipe being arranged in circulating box, cycle
Airscoop shroud is housed on the downside of case left end, airscoop shroud connects the second air inlet pipe being arranged in circulating box, the first air inlet pipe and second into
Tracheae connects three-way control valve, and three-way control valve connects gas gathering mask, and gas gathering mask connects air box, and air box is fixed in circulating box
It is interior, air-introduced machine is housed in air box, air-conditioning interface, the cycle of air-conditioning interface right end are housed on the cycle chamber interior wall of air box right end
Mounting groove is housed on the downside of case, the first cover board is housed on mounting groove, circulating box is bolted in the first cover board, and circulating box corresponds to spiral shell
The position of bolt is provided with link block, and threaded hole is provided in link block, and threaded hole is matched with bolt, and the first cover board is built-in air
Purifying tube, air purification cylinder both ends are hatch frame, and air purification cylinder inner wall is provided with internal thread, filter is housed in air purification cylinder
Rack, screen holder outer wall are equipped with external screw thread, and screen holder is built-in air basket strainer, and stuffing frame, filler are housed in air purification cylinder
External screw thread is housed on frame outer wall, dedusting adsorption stuffing is housed in stuffing frame, cycle chamber interior wall corresponds to the setting of air purification cylinder position
There is rubber pad, pipe with spiral pipe is provided on the right side of air purification cylinder, pipe with spiral pipe one end connects water supply connector, the pipe with spiral pipe other end
Water outlet connector is connected, the second mounting groove is housed on the circulating box on the right side of pipe with spiral pipe, the second cover board is housed in the second mounting groove, the
Two cover boards are stainless steel component, and the corresponding cycle chamber interior wall of the second cover board is equipped with fixed block, and fixed magnet is housed in fixed block, the
Second stuffing frame is housed in two cover boards, dehumidifying filler is housed in the second stuffing frame, the corresponding cycle chamber interior wall of the second stuffing frame
Position is provided with rubber base, and permanent magnet is housed in rubber base, air leaving cover is housed on the downside of circulating box right end.
As a further solution of the present invention：It is described outdoor gas-tpe fitting by tracheae communication chamber outside.
As a further solution of the present invention：The three-way control valve is electrically-controlled valve.
As a further solution of the present invention：The air-introduced machine is fixed by the bracket in air box.
As a further solution of the present invention：Swing handle is housed on the screen holder and stuffing frame.
As a further solution of the present invention：The air cleaning net is provided with two layers.
As a further solution of the present invention：The water supply connector connects water pump by water pipe, and water pump connects deep well.
As a further solution of the present invention：There are three the fixed mount settings.
As a further solution of the present invention：First cover area is more than mounting groove.
As a further solution of the present invention：Handle is housed on second cover board.
Compared with prior art, the beneficial effects of the invention are as follows：The present invention can realize in computer room room air cycle and
Air cleaning processing is played the role of in outdoor air outer circulation, realizes that gang air-conditioner uses, simple operation can carry out water cooling
Cooling and dehumidification treatments keep the good circulation of computer room air-flow.
Description of the drawings
Fig. 1 is the structural schematic diagram of computer room airflow circulating system.
Fig. 2 is computer room airflow circulating system internal structure schematic diagram.
In figure：Inlet suction port, 2- fixed frames, 3- circulating boxes, 4- support plates, 5- connecting plates, 6- welded plates, 7- connect outside the rooms 1-
Connect hole, 8- air leaving covers, 9- airscoop shrouds, the second air inlet pipe of 10-, the first air inlet pipe of 11-, 12- gas gathering masks, 13- air boxes, 14- skies
Adjust interface, 15- rubber pads, 16- screen holders, 17- air purification cylinder, 18- water outlet connectors, 19- pipe with spiral pipe, 20- fixed magnets,
21- permanent magnets, 22- rubber bases, 23- fixed blocks, the second stuffing frames of 24-, 25- dehumidifying filler, 26- handles, the second cover boards of 27-,
28- water supply connectors, 29- link blocks, 30- bolts, 31- dedustings adsorption stuffing, 32- stuffing frames, 33- air cleanings net, 34- rotations
Handle, the first cover boards of 35-, 36- air-introduced machines, 37- holders, 38- three-way control valves.
Specific implementation mode
Following will be combined with the drawings in the embodiments of the present invention, and technical solution in the embodiment of the present invention carries out clear, complete
Site preparation describes, it is clear that described embodiments are only a part of the embodiments of the present invention, instead of all the embodiments.It is based on
Embodiment in the present invention, it is obtained by those of ordinary skill in the art without making creative efforts every other
Embodiment shall fall within the protection scope of the present invention.
Please refer to Fig.1-2, in the embodiment of the present invention, a kind of computer room airflow circulating system, including circulating box 3, the cycle
Case 3 is rectangular box body, and circulating box 3 is sealing structure, and 3 upper end of circulating box is equipped with fixed frame 2, and circulating box 3 is solid by fixed frame 2
It is connected on computer room roof, fixed frame 2 includes welded plate 6, and welded plate 6 is welded on circulating box 3, and support plate is fixed on welded plate 6
4,4 upper end of support plate is equipped with connecting plate 5, and connecting hole 7 is housed on connecting plate 5, and 3 left end side of circulating box is equipped with outdoor gas-tpe fitting
1, outdoor gas-tpe fitting 1 connects the first air inlet pipe 11 being arranged in circulating box 3, and airscoop shroud 9 is housed on the downside of 3 left end of circulating box,
Airscoop shroud 9 connects the second air inlet pipe 10 being arranged in circulating box 3, and the first air inlet pipe 11 and the second air inlet pipe 10 connect threeway control
Valve 38 processed, three-way control valve 38 connect gas gathering mask 12, and gas gathering mask 12 connects air box 13, and air box 13 is fixed in circulating box 3,
Air-introduced machine 36 is housed in air box 13, air-conditioning interface 14 is housed on 3 inner wall of circulating box of 13 right end of air box, air-conditioning interface 14 is right
3 downside of circulating box at end is equipped with mounting groove, the first cover board 35 is housed, the first cover board 35 is connected by bolt 30 and recycled on mounting groove
Case 3, the position that circulating box 3 corresponds to bolt 30 are provided with link block 29, threaded hole, threaded hole and bolt are provided in link block 29
30 matchings, the first cover board 35 is built-in an air purifying tube 17, and 17 both ends of air purification cylinder are hatch frame, in air purification cylinder 17
Wall is provided with internal thread, and screen holder 16 is housed in air purification cylinder 17, and 16 outer wall of screen holder is equipped with external screw thread, and screen holder 16 is built-in
There is an air basket strainer 33, stuffing frame 32 is housed in air purification cylinder 17, external screw thread is housed on 32 outer wall of stuffing frame, in stuffing frame 32
Equipped with dedusting adsorption stuffing 31,3 inner wall of circulating box corresponds to 17 position of air purification cylinder and is provided with rubber pad 14, air purification cylinder 17
Right side is provided with pipe with spiral pipe 19, and 19 one end of pipe with spiral pipe connects water supply connector 28, and the connection water outlet of 19 other end of pipe with spiral pipe connects
First 18, the second mounting groove is housed on the circulating box 31 on the right side of pipe with spiral pipe 1, the second cover board 27 is housed in second mounting groove, second
Cover board 27 is stainless steel component, and 3 inner wall of the second 27 corresponding circulating box of cover board is equipped with fixed block 23, is equipped with and fixes in fixed block 23
Magnet 20, the second cover board 27 is interior equipped with the second stuffing frame 24, and the second stuffing frame 24 is interior equipped with dehumidifying filler 25, the second stuffing frame 24
The position of 3 inner wall of corresponding circulating box is provided with rubber base 22, and permanent magnet 21,3 right end of circulating box downside are housed in rubber base 22
Equipped with air leaving cover 8, outdoor gas-tpe fitting 1 by tracheae communication chamber outside, three-way control valve 38 is electrically-controlled valve, and air-introduced machine 36 passes through branch
Frame 37 is fixed in air box 13, and swing handle 34 is housed on screen holder 16 and stuffing frame 32, and air cleaning net 33 is provided with two
Layer, water supply connector 28 connect water pump by water pipe, and water pump connects deep well, and there are three the settings of fixed frame 2,35 area of the first cover board
More than mounting groove, handle 26 is housed on the second cover board 27.
When the present invention works, 3 left end side of circulating box is equipped with outdoor gas-tpe fitting 1, and it is tight that outdoor gas-tpe fitting 1 plays connection
Gu effect, outdoor gas-tpe fitting 1 connects the first air inlet pipe 11 being arranged in circulating box 3, and air inlet is housed on the downside of 3 left end of circulating box
Cover 9, airscoop shroud 9 connect the second air inlet pipe 10 being arranged in circulating box 3, the first air inlet pipe 11 and the second air inlet pipe 10 connection three
Logical control valve 38, three-way control valve 38 connect gas gathering mask 12, and gas gathering mask 12 connects air box 13, pass through the first air inlet pipe 11 and the
Two air inlet pipe 10 carry out air inlet, realize that air pipeline circulation, air box 13 are fixed in circulating box 3, are equipped with and draw in air box 13
Wind turbine 36 can realize cycle and outdoor air outer circulation in room air, screen holder 16, strainer are housed in air purification cylinder 17
16 outer wall of frame is equipped with external screw thread, and screen holder 16 is built-in air basket strainer 33, and stuffing frame 32, filler are housed in air purification cylinder 17
External screw thread is housed on 32 outer wall of frame, dedusting adsorption stuffing 31 is housed in stuffing frame 32, air purification cylinder 17 is mainly used for carrying out empty
Gas purifies, and ensures that air quality, air cleaning net 33 are used to remove the large volume dust in air, dedusting adsorption stuffing 31 is main
For being adsorbed to the particle micronic dust in air, it can realize that air cleaning is handled, can realize that gang air-conditioner uses, operation
Simply, 17 right side of air purification cylinder is provided with pipe with spiral pipe 19, and 19 one end of pipe with spiral pipe connects water supply connector 28, pipe with spiral pipe 19
The other end connects water outlet connector 18, and dehumidifying filler 25 is housed in second stuffing frame 24, is filled out by the way that pipe with spiral pipe 19 and dehumidifying is arranged
Material 25, can carry out water-cooled cooling and meet dehumidification treatments simultaneously.
In the description of the present invention, it is to be understood that, term "center", " longitudinal direction ", " transverse direction ", "upper", "lower",
The orientation or positional relationship of the instructions such as "front", "rear", "left", "right", "vertical", "horizontal", "top", "bottom", "inner", "outside" is
It is based on the orientation or positional relationship shown in the drawings, is merely for convenience of description of the present invention and simplification of the description, rather than instruction or dark
Show that signified device or element must have a particular orientation, with specific azimuth configuration and operation, therefore should not be understood as pair
The limitation of the present invention.In addition, term " first ", " second " etc. are used for description purposes only, it is not understood to indicate or imply phase
To importance or implicitly indicate the quantity of indicated technical characteristic.The feature for defining " first ", " second " etc. as a result, can
To express or implicitly include one or more this feature.In the description of the present invention, unless otherwise indicated, " multiple "
It is meant that two or more.
In the description of the present invention, it should be noted that unless otherwise clearly defined and limited, term " installation ", " phase
Even ", " connection " shall be understood in a broad sense, for example, it may be being fixedly connected, may be a detachable connection, or be integrally connected；It can
Can also be electrical connection to be mechanical connection；It can be directly connected, can also indirectly connected through an intermediary, Ke Yishi
Connection inside two elements.For the ordinary skill in the art, above-mentioned term can be understood by concrete condition
Concrete meaning in the present invention.
It is obvious to a person skilled in the art that invention is not limited to the details of the above exemplary embodiments, Er Qie
In the case of without departing substantially from spirit or essential attributes of the invention, the present invention can be realized in other specific forms.Therefore, no matter
From the point of view of which point, the present embodiments are to be considered as illustrative and not restrictive, and the scope of the present invention is by appended power
Profit requires rather than above description limits, it is intended that all by what is fallen within the meaning and scope of the equivalent requirements of the claims
Variation is included within the present invention.
In addition, it should be understood that although this specification is described in terms of embodiments, but not each embodiment is only wrapped
Containing an independent technical solution, this description of the specification is merely for the sake of clarity, and those skilled in the art should
It considers the specification as a whole, the technical solutions in the various embodiments may also be suitably combined, forms those skilled in the art
The other embodiment being appreciated that.