CN105608269B  A kind of 500kV electric power line pole tower grounding body ray length evaluation method  Google Patents
A kind of 500kV electric power line pole tower grounding body ray length evaluation method Download PDFInfo
 Publication number
 CN105608269B CN105608269B CN201510960102.2A CN201510960102A CN105608269B CN 105608269 B CN105608269 B CN 105608269B CN 201510960102 A CN201510960102 A CN 201510960102A CN 105608269 B CN105608269 B CN 105608269B
 Authority
 CN
 China
 Prior art keywords
 grounding body
 tower grounding
 ray
 length
 electric power
 Prior art date
 Legal status (The legal status is an assumption and is not a legal conclusion. Google has not performed a legal analysis and makes no representation as to the accuracy of the status listed.)
 Active
Links
Classifications

 G—PHYSICS
 G06—COMPUTING; CALCULATING OR COUNTING
 G06F—ELECTRIC DIGITAL DATA PROCESSING
 G06F30/00—Computeraided design [CAD]
 G06F30/20—Design optimisation, verification or simulation
Landscapes
 Engineering & Computer Science (AREA)
 Physics & Mathematics (AREA)
 Theoretical Computer Science (AREA)
 Computer Hardware Design (AREA)
 Evolutionary Computation (AREA)
 Geometry (AREA)
 General Engineering & Computer Science (AREA)
 General Physics & Mathematics (AREA)
 Measurement Of Resistance Or Impedance (AREA)
Abstract
A kind of 500kV electric power line pole tower grounding body ray length evaluation method disclosed by the invention, comprising: establish tower grounding body Model；The impulse earthed resistance of tower grounding body Model is calculated according to model；The formula of the impulse earthed resistance of the Fitting Calculation tower grounding body；According to the formula of the impulse earthed resistance, it is fitted the effective length formula of tower grounding body ray；The effective length of tower grounding body ray is obtained according to actual soil resistivity；Wherein: the ground connection body Model includes four steel bodies and the tower grounding body ray being arranged in the steel body, and four steel bodies form the square that side length is 18m, and the adjacent tower grounding body ray is not total to endpoint.A kind of 500kV electric power line pole tower grounding body ray length evaluation method provided by the invention, provides theoretical foundation for the design and transformation of electric power line pole tower earthing or grounding means, helps to obtain more excellent grounding body.
Description
Technical field
The present invention relates to electrical distribution fields, more specifically, are related to a kind of 500kV electric power line pole tower grounding body and penetrate
Line length evaluation method.
Background technique
In recent years, many areas in China recur because lightning stroke caused by large area short circuit power cut, reason be mostly by
Caused by the impulse earthed resistance of electric power line pole tower grounding body is excessively high.Electric power line pole tower grounding body is protection electric system
Safe and reliable operation, the important measures for protecting personnel safety nearby, tower grounding device diffusing is bad to cause impulse resistance excessive
It is the main reason for causing transmission line lightning stroke to trip.
Recent domestic scholar has carried out a large amount of research for the impulse earthed resistance of earthing or grounding means, proposes various drops
Resistance measure, discovery, which extends horizontal grounding pole and increases ground connection number of poles, can reduce impulse earthed resistance, but grounding body reaches one
After fixed length, continuing to extend grounding body its drop resistance effect of optimization can decline, while there is also same grounding body in difference
Regional using effect it is different, cause earthing material to waste sometimes, and technical requirements are not achieved in grounding body sometimes
Effect.
It is those skilled in the art's urgent problem to be solved as it can be seen that how to provide more excellent grounding body.
Summary of the invention
The object of the present invention is to provide a kind of 500kV electric power line pole tower grounding body ray length evaluation methods, for transmission of electricity
The design and transformation of overhead line structures earthing or grounding means provide theoretical foundation, help to obtain more excellent grounding body.
In order to solve the above technical problem, the present invention provides following technical solutions:
A kind of 500kV electric power line pole tower grounding body ray length evaluation method provided by the invention, the length of the ray
Spending calculation method includes:
Establish tower grounding body Model；
The impulse earthed resistance of tower grounding body Model is calculated according to model；
The formula of the impulse earthed resistance of the Fitting Calculation tower grounding body；
According to the formula of the impulse earthed resistance, it is fitted the effective length formula of tower grounding body ray；
The effective length of tower grounding body ray is obtained according to actual soil resistivity；
Wherein: the ground connection body Model includes four steel bodies and the tower grounding body ray being arranged in the steel body,
The square that four steel bodies composition side length is 18m, the adjacent tower grounding body ray are not total to endpoint.
Preferably, described to be calculated according to model in abovementioned 500kV electric power line pole tower grounding body ray length evaluation method
The impulse earthed resistance of tower grounding body Model, fitting obtain the formula of the impulse earthed resistance of tower grounding body
R=1.1+0.009 ρ+(0.02 ρ 0.97) e^{bl} (l≥0)
Wherein: R is impulse earthed resistance, and ρ is soil resistivity, and e is natural constant,
Preferably, described according to the impact in abovementioned 500kV electric power line pole tower grounding body ray length evaluation method
The formula of ground resistance is fitted the effective length formula of tower grounding body ray, specifically includes:
Impulse earthed resistance is to the ground connection body length derivation, it is assumed that
α=5 ° are obtained, the effective length l for obtaining electric power line pole tower junctor ray is fitted according to α_{e},
Wherein: α is to meet the tangent line of the formula requirement point and the angle of horizontal direction on Rcurve.
Preferably, in abovementioned 500kV electric power line pole tower grounding body ray length evaluation method, when ρ is less than or equal to 100
When Ω m, l_{e}≈0m。
Preferably, in abovementioned 500kV electric power line pole tower grounding body ray length evaluation method, the electric wire line pole tower is connect
The effective length l of body ray_{e}, when ρ is greater than 100 Ω m, the effective length l of electric power line pole tower junctor ray_{e},
Preferably, in abovementioned 500kV electric power line pole tower grounding body ray length evaluation method, the method also includes:
According to the effective length formula of tower grounding body ray, the effective length of tower grounding body ray is obtained according to soil resistivity；
According to the effective length of the tower grounding body ray, impulse earthed resistance R is calculated；
Compare design requirement impulse earthed resistance R_{0}With the size of R,
Work as R_{0}When < R, grounding body ray length l_{e}It is unsatisfactory for design requirement；Otherwise meet design requirement.
Preferably, in abovementioned 500kV electric power line pole tower grounding body ray length evaluation method, the steel body be band steel or
Round steel.
500kV electric power line pole tower grounding body ray length evaluation method provided by the invention, provides one kind and is used for
The excellent ground connection body Model of 500kV electric power line pole tower, while a kind of method for estimating grounding body ray length is provided, it helps
In the effective use effective diffusing length of grounding body, while avoiding unnecessary waste of material.It can utmostly be connect using shaft tower
The steel of ground device, and theoretical foundation is provided for the design and transformation of electric power line pole tower earthing or grounding means, help to provide excellent
Good electric power line pole tower earthing or grounding means.
Detailed description of the invention
To describe the technical solutions in the embodiments of the present invention more clearly, make required in being described below to embodiment
Attached drawing is briefly described, it should be apparent that, for those of ordinary skills, do not making the creative labor
Under the premise of property, it can also be obtained according to these attached drawings other attached drawings.
Fig. 1 is grounding body model schematic provided in an embodiment of the present invention；
Fig. 2 is impulse earthed resistance provided in an embodiment of the present invention and tower grounding body ray length relationship change figure；
Fig. 3 is the effective length and soil resistivity relational graph of tower grounding body ray provided in an embodiment of the present invention.
Specific embodiment
A kind of 500kV electric power line pole tower grounding body ray length evaluation method provided in an embodiment of the present invention, for transmission of electricity
The design and transformation of overhead line structures earthing or grounding means provide theoretical foundation, help to obtain more excellent grounding body.
Technical solution in embodiment in order to enable those skilled in the art to better understand the present invention, and make of the invention real
The above objects, features, and advantages for applying example can be more obvious and easy to understand, with reference to the accompanying drawing to the technology in the embodiment of the present invention
Scheme is described in further detail.
A kind of 500kV electric power line pole tower grounding body ray length evaluation method provided in an embodiment of the present invention, it is main to wrap
It includes:
Establish tower grounding body Model.
The ground connection body Model includes four steel bodies and the tower grounding body ray being arranged in the steel body, and described four
Root steel body forms the square that side length is 18m, and the adjacent tower grounding body ray is not total to endpoint, that is, forms windmill and penetrate
Line, with reference to attached drawing 1, the figure shows the structures and shape of ground connection body Model provided in an embodiment of the present invention.Being grounded body Model can
It is made using band steel or round steel.Preferably, the crosssectional width of band steel is greater than 40 millimeters, and thickness is greater than or equal to 5 millimeters；
Or, round steel diameter is greater than 10 millimeters when using round steel.
The impulse earthed resistance of tower grounding body Model is calculated according to model.
For obtain tower grounding body Model impulse earthed resistance, to 500kV electric power line pole tower grounding body ray length,
Relationship between soil resistivity and impulse earthed resistance three is analyzed, and a kind of analysis side is provided in the embodiment of the present invention
Method establishes CDEGS shaft tower simulation analysis model, and when grounding body uses round steel in model, round steel diameter is greater than 10 millimeters.In model
In by changing the length of soil resistivity and grounding body ray length, calculate separately the impulse earthed resistance for obtaining shaft tower.
Such as, in CDEGS software, respectively change ray length be 0m, 3m, 6m, 12m, 18m, 32m, 46m, 57m, 79m,
And soil resistivity be respectively set as 100 Ω m, 200 Ω m, 300 Ω m, 400 Ω m, 500 Ω m, 800 Ω m,
1000 Ω m, 1500 Ω m, 2000 Ω m, 2500 Ω m, 3000 Ω m obtain impulse grounding electricity by simulation calculation
Resistance distribution is as shown in Fig. 2.
With reference to attached drawing 2, analysis can be obtained no matter under which kind of soil resistivity, and the impulse resistance of earthing or grounding means is all with ray
The increase of length and reduce, and reach there is after certain length saturation trend.Therefore, when ray reaches certain length, after
For the long ray length that renews substantially without resistance reducing effect, we are defined as the length effective length of tower grounding device.
To curve in attached drawing 2 be fitted to obtain 500kV tower grounding body impulse earthed resistance and soil resistivity and
The relational expression of ray length are as follows:
The formula of the impulse earthed resistance of the Fitting Calculation tower grounding body: R=1.1+0.009 ρ+(0.02 ρ 0.97) e^{bl}
(l >=0), in which: R is impulse earthed resistance, and ρ is soil resistivity, and e is natural constant,
According to the formula of the impulse earthed resistance, it is fitted the effective length formula of tower grounding body ray.
Using IEEE TRANSACTIONS ON POWER DELIVERY the 2nd phase in 2005 document " Effective
Length of Counterpoise Wire Under Lightning Current " provide method: impulse grounding will be met
Earthing pole length when resistance is less than a certain specified value to the derivative of ground connection body length is defined as the effective length of earthing pole, it may be assumed thatIn formula, α is to meet the tangent line of the formula requirement point and the angle of horizontal direction on curve.When α=5 °, after
Renew long ray length, and impulse earthed resistance varies less, it is believed that ray reaches its effective length at this time.
With reference to attached drawing 3, fitting obtains the effective length l of electric wire line pole tower junctor ray_{e},
When soil resistivity is 100 Ω m, the effective length l of tower grounding body ray_{e}Only 1.89m, i.e., when ρ=
When 100 Ω m, l_{e}=1.89m so can choose when soil resistivity is less than 100 Ω m, there is tower grounding body ray
Effective length l_{e}Can be approximately considered is 0m, i.e., as the Ω m of ρ≤100, l_{e}≈0m。
The effective length of tower grounding body ray is obtained according to actual soil resistivity.
The soil resistivity of acquisition is substituted into abovementioned formula, obtains the effective of shaft tower grounding body ray under this soil resistivity
Length l_{e}。
In this way, after the effective length for obtaining tower grounding body ray, it can also having according to this tower grounding body ray
Effect length carries out judging whether this effective length meets design needs.By the effective length for the tower grounding body ray being calculated
Wait enterR value is sought, by itself and design requirement or requirements R_{0}Into
Row is relatively (design requirement or requirements be R0).Work as R_{0}When < R, grounding body ray length l_{e}It is unsatisfactory for design requirement；Otherwise meet
Design requirement.
As R0 > R, grounding body ray length l_{e}When meeting design requirement, the grounding body ray length l which uses exists
Effective length l is taken in conservative design_{e}；It can be calculate by the following formula to obtain from material l is saved:
As R0 < R, impulse earthed resistance can not be effectively reduced in the ray length for extending shaft tower grounding body at this time, therefore
L takes effective length l_{e}, at this time using by increasing other measure drop resistances such as amount of radiation.
500kV electric power line pole tower grounding body ray length evaluation method provided by the invention, provides one kind and is used for
The excellent ground connection body Model of 500kV electric power line pole tower, while a kind of method for estimating grounding body ray length is provided, it helps
In the effective use effective diffusing length of grounding body, while avoiding unnecessary waste of material.It can utmostly be connect using shaft tower
The steel of ground device, and theoretical foundation is provided for the design and transformation of electric power line pole tower earthing or grounding means, help to provide excellent
Good electric power line pole tower earthing or grounding means.
All the embodiments in this specification are described in a progressive manner, same and similar portion between each embodiment
Dividing may refer to each other, and the highlights of each of the examples are differences from other embodiments.
The embodiments of the present invention described above are not intended to limit the scope of the present invention.It is any in the present invention
Spirit and principle within made modifications, equivalent substitutions and improvements etc., should all be included in the protection scope of the present invention.
Claims (5)
1. a kind of 500kV electric power line pole tower grounding body ray length evaluation method, which is characterized in that the length gauge of the ray
Calculation method includes:
Establish tower grounding body Model；
The impulse earthed resistance of tower grounding body Model is calculated according to model；
The formula of the impulse earthed resistance of the Fitting Calculation tower grounding body；
According to the formula of the impulse earthed resistance, it is fitted the effective length formula of tower grounding body ray；
The effective length of tower grounding body ray is obtained according to actual soil resistivity；
Wherein: the ground connection body Model includes four steel bodies and the tower grounding body ray being arranged in the steel body, described
The square that four steel body composition side lengths are 18m, the adjacent tower grounding body ray are not total to endpoint；
Wherein, the impulse earthed resistance that tower grounding body Model is calculated according to model, fitting obtain rushing for tower grounding body
Hit the formula of ground resistance
R=1.1+0.009 ρ+(0.02 ρ 0.97) .e^{bl}, l >=0
Wherein: R is impulse earthed resistance, and ρ is soil resistivity, and l is tower grounding body ray length, and e is natural constant,
The method also includes: according to the effective length formula of tower grounding body ray, shaft tower is obtained according to soil resistivity and is connect
The effective length of ground body ray；
According to the effective length of the tower grounding body ray, impulse earthed resistance R is calculated；
Compare design requirement impulse earthed resistance R_{0}With the size of R,
Work as R_{0}When < R, the effective length l of electric power line pole tower grounding body ray_{e}It is unsatisfactory for design requirement；Otherwise meet design to want
It asks.
2. 500kV electric power line pole tower grounding body ray length evaluation method according to claim 1, which is characterized in that
The formula according to the impulse earthed resistance is fitted the effective length formula of tower grounding body ray, specifically includes:
Impulse earthed resistance is to the grounding body ray length derivation, it is assumed that
α=5 ° are obtained, the effective length l for obtaining electric power line pole tower grounding body ray is fitted according to α_{e},
Wherein: α is to meet the tangent line of the formula requirement point and the angle of horizontal direction on Rcurve.
3. 500kV electric power line pole tower grounding body ray length evaluation method according to claim 2, which is characterized in that
When ρ is less than or equal to 100 Ω m, l_{e}≈0m。
4. 500kV electric power line pole tower grounding body ray length evaluation method according to claim 2, which is characterized in that
The effective length l of the electric power line pole tower grounding body ray_{e}, when ρ is greater than 100 Ω m, electric power line pole tower grounding body is penetrated
The effective length l of line_{e},
5. 500kV electric power line pole tower grounding body ray length evaluation method according to claim 1, which is characterized in that
The steel body is band steel or round steel.
Priority Applications (1)
Application Number  Priority Date  Filing Date  Title 

CN201510960102.2A CN105608269B (en)  20151221  20151221  A kind of 500kV electric power line pole tower grounding body ray length evaluation method 
Applications Claiming Priority (1)
Application Number  Priority Date  Filing Date  Title 

CN201510960102.2A CN105608269B (en)  20151221  20151221  A kind of 500kV electric power line pole tower grounding body ray length evaluation method 
Publications (2)
Publication Number  Publication Date 

CN105608269A CN105608269A (en)  20160525 
CN105608269B true CN105608269B (en)  20190405 
Family
ID=55988201
Family Applications (1)
Application Number  Title  Priority Date  Filing Date 

CN201510960102.2A Active CN105608269B (en)  20151221  20151221  A kind of 500kV electric power line pole tower grounding body ray length evaluation method 
Country Status (1)
Country  Link 

CN (1)  CN105608269B (en) 
Families Citing this family (2)
Publication number  Priority date  Publication date  Assignee  Title 

CN106093589B (en) *  20160809  20180918  国网重庆市电力公司南岸供电分公司  A kind of pole tower ground resistance Accurate measurement and device 
CN111880010B (en) *  20200810  20211109  西南交通大学  Method for detecting impact effective length of grounding electrode of power transmission line tower 
Citations (1)
Publication number  Priority date  Publication date  Assignee  Title 

CN105098391A (en) *  20150826  20151125  云南电网有限责任公司电力科学研究院  500 kV transmission line tower grounding body and estimation method of impulse grounding resistance thereof 

2015
 20151221 CN CN201510960102.2A patent/CN105608269B/en active Active
Patent Citations (1)
Publication number  Priority date  Publication date  Assignee  Title 

CN105098391A (en) *  20150826  20151125  云南电网有限责任公司电力科学研究院  500 kV transmission line tower grounding body and estimation method of impulse grounding resistance thereof 
NonPatent Citations (4)
Title 

Effective Length of Counterpoise Wire Under Lightning Current;Jinliang He 等;《IEEE TRANSACTIONS ON POWER DELIVERY》;20050430;第20卷(第2期);第15851591页 
接地模块冲击特性的试验研究;吴昊 等;《电瓷避雷器》;20130630(第3期);第110115页 
输电线路杆塔及接地体雷电冲击响应分析;吴昊 等;《高压电》;20150516;第51卷(第5期);第1925、30页 
输电线路杆塔接地极冲击接地电阻特性分析;张敏 等;《电瓷避雷器》;20120831(第4期);第59页 
Also Published As
Publication number  Publication date 

CN105608269A (en)  20160525 
Similar Documents
Publication  Publication Date  Title 

CN105631096B (en)  A kind of 110kV/220kV electric power line pole tower grounding body ray length evaluation method  
CN203983732U (en)  The antilightning strike catch net of Architectural Equipment  
CN202352841U (en)  Multipole grounding device for power transmission line tower  
CN105929241A (en)  Grounding network design method for reducing impact grounding resistance of grounding network  
CN105243176A (en)  Graphic analysis method for optimized configuration of lightning arrester of 110kV/220kV power transmission line  
CN204156112U (en)  A kind of grounding system  
CN105652093A (en)  Grounding device impact grounding impedance test method  
CN105098391B (en)  A kind of evaluation method of 500kV electric power line pole towers grounding body and its impulse earthed resistance  
CN105608269B (en)  A kind of 500kV electric power line pole tower grounding body ray length evaluation method  
CN205646216U (en)  Insulation is tested denso and is established earth connection auxiliary rod  
CN106451308A (en)  35kv/10kv commontower distribution line lightning protection device  
CN103825113A (en)  Grounding device for highsoil resistivity region  
CN203205552U (en)  Net for reducing grounding resistance of power transmission line tower  
WO2013040361A3 (en)  Fluid turbine lightning protection system  
CN203850445U (en)  A high soil resistivity region grounding device  
CN103066544A (en)  Cable terminal steel pipe pole  
CN205863643U (en)  A kind of skyscraper power circuit facility discharging rod  
CN206259506U (en)  Perpendicular grounding device in the range of a kind of column foot of electric power line pole tower  
CN205212178U (en)  Spherical lightning rod  
CN209200168U (en)  A kind of transmission tower earthing or grounding means  
CN203910986U (en)  A lowresistance and anticorrosion type grounding module used for lightning protection  
CN211530203U (en)  Graphitebased flexible grounding device with low impact resistance  
CN204304163U (en)  Ultrahightension power transmission line down conductor  
CN206516777U (en)  It is a kind of to reduce the structure of grounding resistance  
CN102957115B (en)  500kV electric transmission line lightning arrester arranges method 
Legal Events
Date  Code  Title  Description 

C06  Publication  
PB01  Publication  
C10  Entry into substantive examination  
SE01  Entry into force of request for substantive examination  
GR01  Patent grant  
GR01  Patent grant 