CN105468858A  Structural transformer fault diagnosis method based on finite element simulation and field test  Google Patents
Structural transformer fault diagnosis method based on finite element simulation and field test Download PDFInfo
 Publication number
 CN105468858A CN105468858A CN201510864608.3A CN201510864608A CN105468858A CN 105468858 A CN105468858 A CN 105468858A CN 201510864608 A CN201510864608 A CN 201510864608A CN 105468858 A CN105468858 A CN 105468858A
 Authority
 CN
 China
 Prior art keywords
 transformer
 finite
 simulation
 circuit
 electric
 Prior art date
Links
 238000004088 simulation Methods 0.000 title claims abstract description 29
 238000003745 diagnosis Methods 0.000 title abstract description 10
 230000000875 corresponding Effects 0.000 claims abstract description 35
 235000012970 cakes Nutrition 0.000 claims description 60
 238000006073 displacement reactions Methods 0.000 claims description 26
 230000001808 coupling Effects 0.000 claims description 20
 238000010168 coupling process Methods 0.000 claims description 20
 238000005859 coupling reactions Methods 0.000 claims description 20
 239000011159 matrix materials Substances 0.000 claims description 12
 239000000463 materials Substances 0.000 claims description 4
 230000019771 cognition Effects 0.000 abstract 1
 238000004804 winding Methods 0.000 description 23
 210000002320 Radius Anatomy 0.000 description 4
 238000010586 diagrams Methods 0.000 description 4
 230000000694 effects Effects 0.000 description 4
 239000004020 conductors Substances 0.000 description 3
 238000000034 methods Methods 0.000 description 2
 238000003825 pressing Methods 0.000 description 2
 230000036536 Cave Effects 0.000 description 1
 241001269238 Data Species 0.000 description 1
 239000003990 capacitor Substances 0.000 description 1
 RYGMFSIKBFXOCRUHFFFAOYSAN copper Chemical compound data:image/svg+xml;base64,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 data:image/svg+xml;base64,PD94bWwgdmVyc2lvbj0nMS4wJyBlbmNvZGluZz0naXNvLTg4NTktMSc/Pgo8c3ZnIHZlcnNpb249JzEuMScgYmFzZVByb2ZpbGU9J2Z1bGwnCiAgICAgICAgICAgICAgeG1sbnM9J2h0dHA6Ly93d3cudzMub3JnLzIwMDAvc3ZnJwogICAgICAgICAgICAgICAgICAgICAgeG1sbnM6cmRraXQ9J2h0dHA6Ly93d3cucmRraXQub3JnL3htbCcKICAgICAgICAgICAgICAgICAgICAgIHhtbG5zOnhsaW5rPSdodHRwOi8vd3d3LnczLm9yZy8xOTk5L3hsaW5rJwogICAgICAgICAgICAgICAgICB4bWw6c3BhY2U9J3ByZXNlcnZlJwp3aWR0aD0nODVweCcgaGVpZ2h0PSc4NXB4JyB2aWV3Qm94PScwIDAgODUgODUnPgo8IS0tIEVORCBPRiBIRUFERVIgLS0+CjxyZWN0IHN0eWxlPSdvcGFjaXR5OjEuMDtmaWxsOiNGRkZGRkY7c3Ryb2tlOm5vbmUnIHdpZHRoPSc4NScgaGVpZ2h0PSc4NScgeD0nMCcgeT0nMCc+IDwvcmVjdD4KPHRleHQgZG9taW5hbnQtYmFzZWxpbmU9ImNlbnRyYWwiIHRleHQtYW5jaG9yPSJzdGFydCIgeD0nMTYuMjI1NCcgeT0nNDcuNzk1NScgc3R5bGU9J2ZvbnQtc2l6ZTozOHB4O2ZvbnQtc3R5bGU6bm9ybWFsO2ZvbnQtd2VpZ2h0Om5vcm1hbDtmaWxsLW9wYWNpdHk6MTtzdHJva2U6bm9uZTtmb250LWZhbWlseTpzYW5zLXNlcmlmO2ZpbGw6IzNCNDE0MycgPjx0c3Bhbj5DdTwvdHNwYW4+PC90ZXh0Pgo8L3N2Zz4K [Cu] RYGMFSIKBFXOCRUHFFFAOYSAN 0.000 description 1
 229910052802 copper Inorganic materials 0.000 description 1
 239000010949 copper Substances 0.000 description 1
 238000005516 engineering processes Methods 0.000 description 1
 230000004907 flux Effects 0.000 description 1
 239000003921 oils Substances 0.000 description 1
 230000035945 sensitivity Effects 0.000 description 1
 238000005303 weighing Methods 0.000 description 1
Classifications

 G—PHYSICS
 G06—COMPUTING; CALCULATING; COUNTING
 G06F—ELECTRIC DIGITAL DATA PROCESSING
 G06F30/00—Computeraided design [CAD]
 G06F30/20—Design optimisation, verification or simulation
 G06F30/23—Design optimisation, verification or simulation using finite element methods [FEM] or finite difference methods [FDM]

 G—PHYSICS
 G06—COMPUTING; CALCULATING; COUNTING
 G06F—ELECTRIC DIGITAL DATA PROCESSING
 G06F30/00—Computeraided design [CAD]
 G06F30/30—Circuit design
 G06F30/36—Circuit design at the analogue level
 G06F30/367—Design verification, e.g. using simulation, simulation program with integrated circuit emphasis [SPICE], direct methods or relaxation methods
Abstract
Description
Technical field
The present invention relates to transformer fault diagnosis technical field, specifically a kind of transformer device structure method for diagnosing faults based on finite element simulation and site test.
Background technology
Structural failure causes power transformer to be damaged the one of the main reasons of accident.The safe and stable operation that structural failure diagnosis can guarantee transformer is carried out to the transformer after transport or shortcircuit impact.Transformer device structure fault offline checking method conventional at present mainly contains frequency response method (FrequencyResponseAnalysis, FRA), short circuit impedance method (ShortCircuitImpedanceMethod, SCI) etc.Frequency response method can on wider frequency band Measurement and analysis circuit network frequency response characteristic thus judge winding state, there is higher sensitivity.Short circuit impedance method can reflect the radial deformation of coil, and have accumulated a large amount of field test datas.But, at present for the change of the site test results such as frequency response curve and shortcircuit impedance basic reason and still require study with the corresponding relation of fault type, therefore there is the problem that test findings understanding is indefinite, there is erroneous judgement, causing trouble diagnostic reliability reduces.
Summary of the invention
Technical matters to be solved by this invention is to provide a kind of transformer device structure method for diagnosing faults combined with site test based on finite element simulation, to improve the reliability of transformer device structure fault diagnosis, solve indefinite to test findings understanding in site test, there is the problems such as erroneous judgement.
Based on a transformer device structure method for diagnosing faults for finite element simulation and site test, comprise the steps:
Step one, in finite element emulation software, set up transformer finite element model;
Step 2, in transformer finite element model, different structure fault to be simulated;
In step 3, the dissimilar and degree structural failure model that arranges in step 2, solve its main electrical parameters, set up the relation between " structural failureelectric parameter ";
Step 4, solve the electric parameter obtained according to transformer finite element model, set up the site test results that circuitmodel simulation is corresponding, solved frequency response curve and the shortcircuit impedance of transformer under different electric parameter by simulation circuit model, set up " electric parametertest findings " corresponding relation;
Step 5, be intermediate variable with electric parameter, set up the corresponding relation of test findings and structural failure: by finite element model, dissimilar and degree structural failure are simulated, solve the change of its electric parameter, and then set up different circuit models, solved frequency response curve and the shortcircuit impedance of transformer under different electric parameter by simulation circuit model, set up the corresponding relation of " structural failureelectric parametertest findings ".
Further, the material behavior of main support is considered when setting up transformer finite element model in step one.
Further, by the structure of each parts in change transformer finite element model, relative position, connected mode, transformer common structure fault is simulated in step 2.
Further, described structural failure comprises short circuit between radial deformation, axial displacement, turntoturn short circuit, cake, imperfect earth.
Further, solve transformer electric parameter and mainly its capacitance matrix and inductance matrix carried out, in described finite element model transformer n line cake between electric capacity form the n rank capacitance matrix of transformer, wherein: C _{ij}it is the coupling capacitance between ith line cake and a jth line cake; C _{ii}be the selfcapacitance of ith line cake, it mainly comprises the ground capacitance of line cake and the coupling capacitance sum with other line cakes, and the coupling capacitance between two line cakes is obtained by following formula:
In formula, W _{ij}for electric field storage power, D _{i}the electric displacement density that ith line cake is corresponding, E _{j}for the electric field intensity of jth line cake;
When foreign current is by means of only ith line cake, its selfinductance L _{ii}and resistance R _{ii}following vector form can be described to:
In formula, ω is angular frequency, for induced voltage, the imaginary part of above formula is only associated with the selfinductance of ith line cake, therefore obtains its selfinductance:
In like manner, the coupling inductance between ith line cake and a jth line cake is obtained by following formula:
Further, the circuit model in step 4 comprises lumped parameter model, " fieldLu " coupling model, and lumped parameter model is used for simulation frequency response curve, and coupling magnetic field with electric circuit model is used for artificial shortcircuits impedance.
The present invention proposes the fault diagnosis thinking based on " structural parameterselectric parametertest findings ", by setting up transformer limit element artificial module, different structure fault type and different faults degree are emulated, solve the electric parameter under Different structural parameters, according to the electric parameter solved, set up the typical transformer field test of emulation (shortcircuit impedance, frequency response) result, set up the corresponding relation of test findings and structural failure, realize transformer device structure fault diagnosis.
Accompanying drawing explanation
Fig. 1 is the schematic flow sheet of the transformer device structure method for diagnosing faults that the present invention is based on finite element simulation and site test;
Fig. 2 is the transformer finite element model figure of the 110kV electric pressure of being built by AnsoftMaxwell software;
Fig. 3 is distortion winding wire cake schematic diagram;
Fig. 4 is axis of winding displacement diagram;
Fig. 5 is the capacitance matrix that finite element solving obtains;
Fig. 6 is frequency response method corresponding circuits illustraton of model;
Fig. 7 is short circuit impedance method corresponding circuits illustraton of model;
Frequency response curve corresponding when Fig. 8 is axial displacement fault 3%, 6% and 9%.
Embodiment
Below in conjunction with the accompanying drawing in the present invention, the technical scheme in the present invention is clearly and completely described.
Figure 1 shows that the schematic flow sheet of the transformer device structure method for diagnosing faults that the present invention is based on finite element simulation and site test, described method comprises the steps:
Step one, in finite element emulation software, set up transformer finite element model; Be different from general transformer realistic model, for Exact Solution is carried out in the electric parameter change caused transformer device structure Parameters variation, the present invention need set up the finite element model considering transformer real material characteristic.Except the structure such as transformer core, winding, this model also needs the material behavior considering main support (as stay, cushion block).
Fig. 2 is the transformer finite element model of the 110kV electric pressure of being built by AnsoftMaxwell software.This type transformer is 110/10.5kV, threephase threecolumn oil immersed type core type transformer.Carry out support structure by stay between high and low pressure winding, each line cake is formed by the flat type copper wire surrounding empire paper, in simulation process, highpressure side winding is set to 8 cakes, each cake 220 circle; Low pressure winding is set to 8 cakes, each cake 21 circle.
In Fig. 2, Corecrosssection is cross section of transformer core schematic diagram, and unshakable in one's determination by adopting DW360 type siliconized plate to consist of laminar, its BH curve is consistent with actual measurement with maintenance by outside input.In Fig. 2, Clamping is apparatus for fixing transformer, and Support is stay, and carry out support structure to each line cake of winding, Spacer is elastic cushion block, is evenly distributed between each line cake of transformer.
Step 2, in transformer finite element model, different structure fault to be simulated; By changing the structure of each parts in transformer finite element model, relative position, connected mode simulate transformer common structure fault, mainly comprises following fault simulation: short circuit, imperfect earth etc. between radial deformation, axial displacement, turntoturn short circuit, cake.Be described for the radial deformation of line cake and axis of winding displacement below.
(1) the radial deformation of line cake
Inside transformer winding is subject to inside electromagnetic force, and outside winding is subject to outside electromagnetic force.Therefore, under the effect of the radial component of electromagnetic force, may there is radial deformation in Transformer Winding.When the rigidity of winding conductor is much smaller than the rigidity of support member, internal lowvoltage winding is fixedly secured by stay, and electromagnetic force makes conductor bend, and causes winding to cave at a place or have more, is forced to warpage.As shown in Figure 3, the line cake that the depression of line cake is R by two mean radiuss intersects and forms, and the mean radius of two line cakes is identical in the process, and the central angle intersecting section correspondence is consistent, and therefore circumference total length is constant.For weighing the distortion degree of annulus molded line cake, define following sign:
In formula, R is the mean radius of line cake, and R1 is the minimum average B configuration radius of line cake.
(2) axis of winding displacement
Fig. 4 is integral axial displacement schematic diagram, and figure mesolow winding moves Δ h in the axial direction.Axis of winding displacement is that integral is subject to the effect of axial electromagnetic force and creates axial movement due under the effect of shortcircuit current and radial leakage flux.Simultaneously because winding two end clamp plate is not by the effect of shortcircuit electromagnetic force, the winding conductor to one end movement can produce extruding to the end pressing plate of winding direction of motion, may bring out the damage of pressing plate.
In step 3, the dissimilar and degree structural failure model that arranges in step 2, solve its main electrical parameters (such as ground capacitance, turntoturn capacitance, coupling capacitance etc.), set up the relation between " structural failureelectric parameter ".
Solve transformer electric parameter mainly to solve its capacitance matrix and inductance matrix.
In finite element model transformer n line cake between electric capacity constitute the n rank capacitance matrix of transformer.Wherein: C _{ij}it is the coupling capacitance between ith line cake and a jth line cake; C _{ii}be the selfcapacitance of ith line cake, it mainly comprises the ground capacitance of line cake and the coupling capacitance sum with other line cakes.Coupling capacitance between two line cakes obtains by following formula:
In formula, W _{ij}for electric field storage power, D _{i}the electric displacement density that ith line cake is corresponding, E _{j}for the electric field intensity of jth line cake.
When foreign current is by means of only ith line cake, its selfinductance (L _{ii}) and resistance (R _{ii}) following vector form can be described to:
In formula, ω is angular frequency, for induced voltage.The imaginary part of above formula is only associated with the selfinductance of ith line cake, therefore can obtain its selfinductance:
In like manner, the coupling inductance between ith line cake and a jth line cake obtains by following formula:
Fig. 5 solves by finite element model the transformer capacitor matrix obtained.The selfcapacitance of this matrix description high pressure winding 8 line cakes and low pressure winding 8 line cakes and mutual capacitance size between any two.
Table 1 ~ 3 are in axial displacement fault 1% ~ 9% situation, solve the transformer main electrical parameters obtained respectively.
Electric parameter during table 1 axial displacement 1% ~ 3%
Electric parameter during table 2 axial displacement 1% ~ 3%
Electric parameter during table 3 axial displacement 1% ~ 3%
Step 4, solve the electric parameter obtained according to transformer finite element model, set up the site test results that circuitmodel simulation is corresponding, by simulation circuit model (as lumped parameter model, " fieldLu " coupling model), solve frequency response curve and the shortcircuit impedance of transformer under different electric parameter, set up " electric parametertest findings " corresponding relation.
For different site tests, different circuit models can be adopted to emulate.Adopt lumped parameter model simulation frequency response curve in the present invention, adopt coupling magnetic field with electric circuit model emulation shortcircuit impedance.
Fig. 6 is frequency response method corresponding circuits illustraton of model.The electric parameter solved in employing table 1 ~ 3, can simulate frequency response test result, achieves the corresponding of structural failure and frequency response curve.
Fig. 7 is short circuit impedance method corresponding circuits illustraton of model.This lumped parameter coupling magnetic field with electric circuit model can be simulated shortcircuit impedance test findings, achieves the corresponding of structural failure and shortcircuit impedance.
Step 5, be intermediate variable with electric parameter, set up the corresponding relation of test findings and structural failure: by finite element model, dissimilar and degree structural failure are simulated, solve the change of its electric parameter, and then set up different circuit models, solved frequency response curve and the shortcircuit impedance of transformer under different electric parameter by simulation circuit model, set up the corresponding relation of " structural failureelectric parametertest findings ".
Frequency response curve corresponding when Fig. 8 is axial displacement fault 3%, 6% and 9%.Therefore, the corresponding relation of axial displacement fault and test findings is set up:
Corresponding relation 1: axial displacement faultfrequency response curve occurs amplitude deviation at 150kHz;
Corresponding relation 2: axial displacement faultthe entirety of frequency response curve harmonic peak moves to right;
Corresponding relation 3: axial displacement faultfrequency response curve first harmonic peak amplitude reduces;
Corresponding relation 4: axial displacement faultfrequency response curve first antiresonance peak amplitude increases;
Corresponding relation 5: axial displacement faultshortcircuit impedance does not change.
That is, the changing features trend from the direct deagnostic structure fault of test findings is established.
For axial displacement fault 3%, 6% and 9%, according to " structural failureelectric parametertest findings " this diagnosis thinking proposed by the invention, solve the electric parameter (table 1 ~ 3) under fault in various degree respectively, and then obtain corresponding frequency response curve (Fig. 8).Finally draw from the changing features trend of the direct deagnostic structure fault of test findings and (that is, thought that axial displacement fault can cause frequency response curve to produce amplitude change at about 150kHz, cause the entirety of harmonic peak to move to right simultaneously.Along with the aggravation of axial displacement degree, the amplitude of its first resonance peaks will obviously reduce, and the amplitude at first antiresonance peak place will obviously increase).
The above; be only the specific embodiment of the present invention, but protection scope of the present invention is not limited thereto, anyly belongs to those skilled in the art in the technical scope that the present invention discloses; the change that can expect easily or replacement, all should be encompassed within protection scope of the present invention.Therefore, protection scope of the present invention should be as the criterion with the protection domain of claim.
Claims (6)
Priority Applications (1)
Application Number  Priority Date  Filing Date  Title 

CN201510864608.3A CN105468858A (en)  20151201  20151201  Structural transformer fault diagnosis method based on finite element simulation and field test 
Applications Claiming Priority (1)
Application Number  Priority Date  Filing Date  Title 

CN201510864608.3A CN105468858A (en)  20151201  20151201  Structural transformer fault diagnosis method based on finite element simulation and field test 
Publications (1)
Publication Number  Publication Date 

CN105468858A true CN105468858A (en)  20160406 
Family
ID=55606553
Family Applications (1)
Application Number  Title  Priority Date  Filing Date 

CN201510864608.3A CN105468858A (en)  20151201  20151201  Structural transformer fault diagnosis method based on finite element simulation and field test 
Country Status (1)
Country  Link 

CN (1)  CN105468858A (en) 
Cited By (4)
Publication number  Priority date  Publication date  Assignee  Title 

CN105956269A (en) *  20160429  20160921  国家电网公司  Method for acquiring relationship between transformer winding state and interpancake capacitance parameter 
CN106485009A (en) *  20161018  20170308  三峡大学  The simulation method of transformer winding fault situation under a kind of lightning impulse voltage 
CN107247208A (en) *  20170720  20171013  云南电网有限责任公司电力科学研究院  A kind of transformer shortedturn fault location positioning method 
CN107633114A (en) *  20170821  20180126  江苏省电力试验研究院有限公司  A kind of primary cutout latency Mechanical Fault Vibration Signals emulation mode and device 
Citations (4)
Publication number  Priority date  Publication date  Assignee  Title 

CN101819239A (en) *  20100406  20100901  嘉兴学院  Rapidly constructed transformer fault diagnosis system based on threedimensional temperature field 
CN104237713A (en) *  20141017  20141224  国家电网公司  Transformer winding deformation diagnostic method based on discrete wavelet transform 
CN104748838A (en) *  20150327  20150701  国家电网公司  Transformer winding loose determination system and method based on finite element analysis 
CN105046036A (en) *  20150917  20151111  国网天津市电力公司  Magneticstructuralcouplingfieldbased transformer winding deformation analysis method 

2015
 20151201 CN CN201510864608.3A patent/CN105468858A/en not_active Application Discontinuation
Patent Citations (4)
Publication number  Priority date  Publication date  Assignee  Title 

CN101819239A (en) *  20100406  20100901  嘉兴学院  Rapidly constructed transformer fault diagnosis system based on threedimensional temperature field 
CN104237713A (en) *  20141017  20141224  国家电网公司  Transformer winding deformation diagnostic method based on discrete wavelet transform 
CN104748838A (en) *  20150327  20150701  国家电网公司  Transformer winding loose determination system and method based on finite element analysis 
CN105046036A (en) *  20150917  20151111  国网天津市电力公司  Magneticstructuralcouplingfieldbased transformer winding deformation analysis method 
NonPatent Citations (4)
Title 

NASER HASHEMNIA等: "Improved Power Transformer Winding Fault Detection using FRA Diagnostics–Part 1: Axial Displacement Simulation", 《IEEE TRANSACTIONS ON DIELECTRICS AND ELECTRICAL INSULATION》 * 
刘思维等: "基于有限元分析的电力变压器结构性故障诊断", 《中国电机工程学会高电压专业委员会2015年学术年会》 * 
吕妍等: "电力变压器绕组变形常用检测方法", 《山东电力技术》 * 
梁振光等: "采用场路耦合的三维有限元法分析变压器突发短路过程", 《中国电机工程学报》 * 
Cited By (6)
Publication number  Priority date  Publication date  Assignee  Title 

CN105956269A (en) *  20160429  20160921  国家电网公司  Method for acquiring relationship between transformer winding state and interpancake capacitance parameter 
CN106485009A (en) *  20161018  20170308  三峡大学  The simulation method of transformer winding fault situation under a kind of lightning impulse voltage 
CN106485009B (en) *  20161018  20190709  三峡大学  The simulation method of transformer winding fault situation under a kind of lightning impulse voltage 
CN107247208A (en) *  20170720  20171013  云南电网有限责任公司电力科学研究院  A kind of transformer shortedturn fault location positioning method 
CN107633114A (en) *  20170821  20180126  江苏省电力试验研究院有限公司  A kind of primary cutout latency Mechanical Fault Vibration Signals emulation mode and device 
CN107633114B (en) *  20170821  20180814  江苏省电力试验研究院有限公司  A kind of highvoltage circuitbreaker latency Mechanical Fault Vibration Signals emulation mode and device 
Similar Documents
Publication  Publication Date  Title 

MartinezVelasco  Power system transients: parameter determination  
CN102721465B (en)  System and method for diagnosing and preliminarily positioning loosening faults of iron core of power transformer  
Bagheri et al.  Advanced transformer winding deformation diagnosis: moving from offline to online  
Kezunovic et al.  Experimental evaluation of EMTPbased current transformer models for protective relay transient study  
Behjat et al.  Diagnosing shorted turns on the windings of power transformers based upon online FRA using capacitive and inductive couplings  
Kumbhar et al.  Analysis of shortcircuit performance of splitwinding transformer using coupled fieldcircuit approach  
Mitchell et al.  Modeling power transformers to support the interpretation of frequencyresponse analysis  
CN101232176B (en)  Noneffective earthing distribution system fault locating method based on neutral point of transient traveling wave  
Jayasinghe et al.  Winding movement in power transformers: a comparison of FRA measurement connection methods  
KR101794429B1 (en)  Method and device for testing a transformer  
CN103278756B (en)  A kind of method assessing transformer oil paper insulation ageing state  
CN104991161B (en)  Doublefed aerogenerator stator winding interturn shortcircuit models and feature extracting method  
CN101833043B (en)  Method for measuring electric capacity and dielectric loss of capacitance type voltage transformer  
Hashemnia et al.  Improved power transformer winding fault detection using FRA diagnostics–part 2: radial deformation simulation  
FilipovićGrčić et al.  Highfrequency model of the power transformer based on frequencyresponse measurements  
CN102435941B (en)  Method for simulating very fast transient overvoltage during opening/closing process of isolating switch  
Pham et al.  A new method for purposes of failure diagnostics and FRA interpretation applicable to power transformers  
CN102590703B (en)  Singlephase grounding failure route selection method of resonance grounding system based on zerosequence transient charge  
CN101699301B (en)  Method for measuring line parameter through induced electricity  
CN103091609A (en)  Performance detecting system and method thereof of gas insulated substation (GIS) partial discharge online monitoring device  
Cardoso  Leakage inductances calculation for power transformers interturn fault studies  
CN103698695A (en)  Multifunctional electrical characteristic testing device and testing method for highvoltage circuit breaker  
CN104111393B (en)  Comprehensive evaluation analysis method for power transformer shortcircuiting resistance  
Sofian et al.  Interpretation of transformer FRA responses—Part II: Influence of transformer structure  
CN103926466B (en)  A kind of electrical equipment loop resistance test system and contact condition appraisal procedure 
Legal Events
Date  Code  Title  Description 

C06  Publication  
PB01  Publication  
C10  Entry into substantive examination  
SE01  Entry into force of request for substantive examination  
RJ01  Rejection of invention patent application after publication  
RJ01  Rejection of invention patent application after publication 
Application publication date: 20160406 