CA2612835A1  Nondestructive testing of pipes  Google Patents
Nondestructive testing of pipesInfo
 Publication number
 CA2612835A1 CA2612835A1 CA 2612835 CA2612835A CA2612835A1 CA 2612835 A1 CA2612835 A1 CA 2612835A1 CA 2612835 CA2612835 CA 2612835 CA 2612835 A CA2612835 A CA 2612835A CA 2612835 A1 CA2612835 A1 CA 2612835A1
 Authority
 CA
 Grant status
 Application
 Patent type
 Prior art keywords
 pipe
 thickness
 velocity
 wall
 acoustic
 Prior art date
 Legal status (The legal status is an assumption and is not a legal conclusion. Google has not performed a legal analysis and makes no representation as to the accuracy of the status listed.)
 Granted
Links
Classifications

 G—PHYSICS
 G01—MEASURING; TESTING
 G01N—INVESTIGATING OR ANALYSING MATERIALS BY DETERMINING THEIR CHEMICAL OR PHYSICAL PROPERTIES
 G01N29/00—Investigating or analysing materials by the use of ultrasonic, sonic or infrasonic waves; Visualisation of the interior of objects by transmitting ultrasonic or sonic waves through the object
 G01N29/04—Analysing solids
 G01N29/07—Analysing solids by measuring propagation velocity or propagation time of acoustic waves

 G—PHYSICS
 G01—MEASURING; TESTING
 G01B—MEASURING LENGTH, THICKNESS OR SIMILAR LINEAR DIMENSIONS; MEASURING ANGLES; MEASURING AREAS; MEASURING IRREGULARITIES OF SURFACES OR CONTOURS
 G01B17/00—Measuring arrangements characterised by the use of subsonic, sonic or ultrasonic vibrations
 G01B17/02—Measuring arrangements characterised by the use of subsonic, sonic or ultrasonic vibrations for measuring thickness

 G—PHYSICS
 G01—MEASURING; TESTING
 G01M—TESTING STATIC OR DYNAMIC BALANCE OF MACHINES OR STRUCTURES; TESTING STRUCTURES OR APPARATUS NOT OTHERWISE PROVIDED FOR
 G01M3/00—Investigating fluidtightness of structures
 G01M3/02—Investigating fluidtightness of structures by using fluid or vacuum
 G01M3/04—Investigating fluidtightness of structures by using fluid or vacuum by detecting the presence of fluid at the leakage point
 G01M3/24—Investigating fluidtightness of structures by using fluid or vacuum by detecting the presence of fluid at the leakage point using infrasonic, sonic, or ultrasonic vibrations
 G01M3/243—Investigating fluidtightness of structures by using fluid or vacuum by detecting the presence of fluid at the leakage point using infrasonic, sonic, or ultrasonic vibrations for pipes

 G—PHYSICS
 G01—MEASURING; TESTING
 G01N—INVESTIGATING OR ANALYSING MATERIALS BY DETERMINING THEIR CHEMICAL OR PHYSICAL PROPERTIES
 G01N29/00—Investigating or analysing materials by the use of ultrasonic, sonic or infrasonic waves; Visualisation of the interior of objects by transmitting ultrasonic or sonic waves through the object
 G01N29/22—Details, e.g. general constructional or apparatus details
 G01N29/222—Constructional or flow details for analysing fluids

 G—PHYSICS
 G01—MEASURING; TESTING
 G01N—INVESTIGATING OR ANALYSING MATERIALS BY DETERMINING THEIR CHEMICAL OR PHYSICAL PROPERTIES
 G01N29/00—Investigating or analysing materials by the use of ultrasonic, sonic or infrasonic waves; Visualisation of the interior of objects by transmitting ultrasonic or sonic waves through the object
 G01N29/44—Processing the detected response signal, e.g. electronic circuits specially adapted therefor
 G01N29/4409—Processing the detected response signal, e.g. electronic circuits specially adapted therefor by comparison
 G01N29/4418—Processing the detected response signal, e.g. electronic circuits specially adapted therefor by comparison with a model, e.g. bestfit, regression analysis

 G—PHYSICS
 G01—MEASURING; TESTING
 G01N—INVESTIGATING OR ANALYSING MATERIALS BY DETERMINING THEIR CHEMICAL OR PHYSICAL PROPERTIES
 G01N2291/00—Indexing codes associated with group G01N29/00
 G01N2291/01—Indexing codes associated with the measuring variable
 G01N2291/011—Velocity or travel time

 G—PHYSICS
 G01—MEASURING; TESTING
 G01N—INVESTIGATING OR ANALYSING MATERIALS BY DETERMINING THEIR CHEMICAL OR PHYSICAL PROPERTIES
 G01N2291/00—Indexing codes associated with group G01N29/00
 G01N2291/02—Indexing codes associated with the analysed material
 G01N2291/028—Material parameters
 G01N2291/02827—Elastic parameters, strength or force

 G—PHYSICS
 G01—MEASURING; TESTING
 G01N—INVESTIGATING OR ANALYSING MATERIALS BY DETERMINING THEIR CHEMICAL OR PHYSICAL PROPERTIES
 G01N2291/00—Indexing codes associated with group G01N29/00
 G01N2291/02—Indexing codes associated with the analysed material
 G01N2291/028—Material parameters
 G01N2291/02854—Length, thickness

 G—PHYSICS
 G01—MEASURING; TESTING
 G01N—INVESTIGATING OR ANALYSING MATERIALS BY DETERMINING THEIR CHEMICAL OR PHYSICAL PROPERTIES
 G01N2291/00—Indexing codes associated with group G01N29/00
 G01N2291/26—Scanned objects
 G01N2291/263—Surfaces
 G01N2291/2634—Surfaces cylindrical from outside
Abstract
Description
NonDestructive Testing of Pipes FIELD OF THE INVENTION
100011 This invention relates to the nondestructive condition assessment of pipes, and in particular buried pipes or pipes that are otherwise inaccessible, such as fire sprinkler systems and pipelines in the oil and gas industry.
BACKGROUND OF THE INVENTION
[0002] Buried pipes, such as pipes used in municipal water systems, lose metal resulting in a reduction in pipe wall thickness, as a result of internal and external corrosion. Sustained wall thickness loss eventually causes the pipe to fail. Such pipes have to be periodically inspected and evaluated for structural adequacy. Accurate information about pipe wall thickness is needed to determine the structural capacity of pipes. Also, monitoring of pipe metal loss is needed to estimate the remaining service life of pipes, which is an important part of maintenance management systems of large pipe networks (e.g., urban water or gas distribution systems). It is therefore desirable to be able to assess the condition of buried pipes in a nondestructive and nonintrusive way, that is without damaging the pipe and without taking it out of service.
[0003] One way of determining pipe wall thickness is to obtain pipe coupons (or samples) and then measure the thickness offsite using thickness callipers. Also, wall thickness can be measured using an ultrasonic gauge at locations where the pipe is naturally exposed or intentionally excavated. Both methods provide only a discrete measurement of wall thickness. An alternative method for obtaining a continuous measurement of pipe wall I
thickness employs ultrasonic or magnetic flux leakage or remotefield eddy current devises which are launched inside pipes using robots (known as pipeline pigs).
100041 Excavating pipes for the purpose of measuring wall thickness is costly, as it requires excavating the pipe at several locations. Also, thickness values based on the coupons may not be statistically representative of the overall condition of the pipe unless a very large number of locations are excavated. Pipeline pigging requires taking the pipe out of service.
It is strictly suitable for large diameter pipes with simple geometry (i.e., no abrupt bends).
Data acquisition and analysis is very intensive and expensive. The method is used mostly for oil and gas transmission pipelines. It is not suitable for water distribution systems, which are geometrically complex and extensive networks comprised of smalldiameter pipes that are usually filled with debris and have no pig launching stations.
SUMMARY OF THE INVENTION
100051 In accordance with the invention, the pipe wall thickness is determined from the average propagation velocity of lowfrequency acoustic disturbances in the pipe (e.g., pressure fluctuations). Lowfrequencies typically have a value of less than about 1000Hz.
The propagation velocity depends on the internal diameter and circumferential thickness profile of the pipe, density and bulk modulus of elasticity of the fluid, and Young's modulus of elasticity and Poisson's ratio of the pipe wall material. The velocity can be calculated using the equations derived theoretically. In the proposed method, the pipe wall thickness is back calculated from these equations using the measured value of the propagation velocity and the above pipe and fluid parameters, which are usually known or easily found.
r 11/20/07 17: 33 FAX 61~ 230 8$21 MAR~S & CLER.R (j004 .. ~ .PCTICA ZoOb/ Q40996 ' . ~ ~ NOV=~ 2007 2 ~
. oiI . Qx [0006] According to the preserit ir~vention therc is provided a method for the nondeStructive condition assessrnent Qf a pipe carrying afluid, comprising detecting an at,oustic disturbance propagating past two 1ongitudinally separated points on said pipe;
. determining an actual value representative of the propagation vei*ocity of said acoustic disturbance; cornputing e cortesponding predicted value for the propagation velocity as a .funrtaon af at least one wall thickness parameter of said pipe by using a theoretical model fnr the propagatfon of acoustic waves hi said pipe that assumes said pipe has a finite wall thickness with a predeterrmined nonuniform circumferential thickness profilc and takes I
. into account stresses across the thickness of the pipe walI, and wherein said wa11 thickness pararneters are representatYve of wail thickness at different circurrrfcrential locations on said pipe; and compu#ing said af least one waii thickness parameter by matching said actuai value with said predicted value.
(00071 The acoustic di sturbance can propagate in the inbracket mode, where the source Qf tbe dasturbAnce lies between the two points and the distarbance propa,gates in opposite :
., directions ljram the source to the separatcd points, or in the outofbracket tnodc, where the a.coustic source lies oeitside the two points, afld the disfiutbance propagates from the source and sequentially past the two points in the saune direction.
[0408] The propag,ation velocity, usually the average prnpag$tion rrelacity, can be detearmmined onrisite nondestructively and nonintrvsively by measuring the time delay between acQustic signals measured at two poEnts Qn the pipe that a,re a known distance apart (e.g., ccntrol valves or fire hydrants). Ambient noise in the.pipe can be iased as the acoustic source. .
10009J Alternativeiy, acoustic noise created by releasing pressurized fluid or by a specially designed device at an inbra,cket 4r outofbracket potnt (e.g., a fire hydrant in the case of water distribution pipes)Or acoustlc noise can be used. Acoustfic signals can l,e measured using a pair of'vibration sensors (e.g., accelerometers) or hydropttonGs. The . AMENDEDSHEET
time delay between the two measured signals is determined using the wellknown timeofflight method or the crosscorrelation function (traditional or enhanced) calculated in the time or frequency domains as described in U.S. patent 6,453,247, the contents of which are herein incorporated by reference. The average propagation velocity in the pipe can then be calculated by dividing the difference between the distances of the sensors from the acoustic source by the time delay.
100101 In addition to determining the average thickness, the acoustic damping capacity of the pipe material can also be determined based on the attenuation of the acoustic signals described above. Alternatively, the damping capacity can be determined based on the width of the frequency spectrum peak that corresponds to the fundamental ring frequency of the pipe or based the logarithmic decrement of transient ring vibration. The frequency spectrum and logarithmic decrement can found using a simple mechanical impact test at a location where the pipe is exposed, e.g., in an access manhole. The damping capacity of the pipe material can be used to obtain information about its tensile strength, especially for cast iron pipes, based on published relationships. This is helpful in view of the fact that the tensile strength of cast iron pipes varies widely, depending on their source of supply and vintage.
For cast iron pipes, the damping capacity increases as their strength decreases, which depends on the carbon content and cooling rate. Carbon content and cooling rate affect the matrix and graphite structure of cast iron and in turn its stressstrain nonlinearity. Nonlinearity in the form of a hysteresis loop leads to high damping capacity.
100111 The method in accordance with the invention has the advantage of being nondestructive and nonintrusive. All required measurements can be made from the ground surface. The length of the pipe section represented by the average profile can be arbitrarily chosen. Initially, a 100 metres long section, which is the usual distance between fire hydrants in urban areas, can be chosen. Subsequently, if higher resolution is needed, small access holes to the pipe may be drilled, e.g., using keyhole vacuum excavation technologies, to measure the thickness over shorter pipes sections. Alternatively, arrays of closely spaced hydrophones may be inserted into pipes thru fire hudrants or corporation stops. The measurement and calculation of the pipe wall thickness can be easily made using Windowsbased PC software. The proposed method is easy to implement (e.g., in conjunction with routine leak detection surveys). Also, it does not require a high level of operator skill.
BRIEF DESCRIPTION OF THE DRAWINGS
100121 The invention will now be described in more detail, by way of example only, with reference to the accompanying drawings, in which:
[0013] Figure 1 a shows an arrangement for measuring propagation velocity of buried pipes in accordance with a first embodiment;
100141 Figure lb shows an arrangement for measuring propagation velocity of buried pipes in accordance with a second embodiment;
[0015] Figures 2a and 2b show PC screens displaying the results of a wall thickness measurement in accordance with an embodiment of the invention;
[0016] Figure 3 shows the variation of predicted pipe thickness as a function of bulk modulus of water; and [0017] Figure 4 shows the frequency spectrum of impactecho tests on ductile iron sample of reference pipe; and 100181 Figure 5 shows the predicted wall thickness of reference pipe using adjusted bulk modulus of elasticity of water of 1.95 GPa at 20.8 C.
DETAILED DESCRIPTION OF THE PREFERRED EMBODIMENTS
100191 In order to assist in understanding the invention, it is helpful to consider the underlying theory.
100201 The propagation velocity of acoustic waves in an unbounded fluid body is defined by the following equation:
vo = yK/ p (1) where K is the bulk modulus of elasticity of the fluid, p is its density, and y is the ratio of the specific heats of the fluid (i.e., the ratio of the fluid's heat capacity in a constant pressure process to the heat capacity in a constant volume process).
[0021] The derivation of this equation can be found in Pearsall, I.S. "The velocity of water hammer waves", Proceedings of the Institution of Mechanical Engineers, Vol. 180, Part 3E, pp. 1220, 1965, the contents of which are herein incorporated by reference.
100221 For a nearly incompressible liquid, which is the case under normal temperatures and pressures in water distribution pipes, y is approximately equal to unity.
Then, Eq. (1) becomes:
vo = K l P (2) 100231 The elasticity of the wall of a pressurized fluidcarrying pipe reduces the velocity of acoustic waves in the fluid. The amount of the reduction of the velocity depends on the size and shape of the crosssectional area of the pipe and the elastic modulus of the material of the pipe. The general equation of the velocity of acoustic waves in the fluid is defined by the following equation:
v=vo 1+yK~~ (3) where A is the crosssectional area occupied by the fluid, p is pressure inside the pipe, and vo is defined by Eq. (1). For a nearly incompressible liquid, yis approximately equal to unity. This equation is explained in Wylie, E. B., and Streeter, V. L. Fluid Transients, McGrawHill, New York, 1982. the contents of which are herein incorporated by reference.
[00241 For such fluids, Eq. (1) becomes:
v=v~ rl+K~~l IA (4) where vo is defined by Eq. (2).
100251 For accurate estimation of the velocity, it is necessary to consider the variation of K and p with the temperature, air content, and pressure of the fluid. For pipes having very thick walls or for gasfilled pipes, ~A is negligible and therefore v~ vo. On the other P
hand, for very flexible pipes, the acoustic velocity may be approximated as:
v = a (5) p [0026] The crosssectional area strain of the pipe, aA/A, is caused by the change in total circumferential strain, 8cB, which in turn is caused by the change in pressure, ap. The total circumferential strain is equal to:
as _ a6e ~ca6, (6) a E
where (r, and 6Q are circumferential and axial stresses in the pipe wall, respectively, and E
and is the elastic modulus and Poisson's ratio of the pipe material.
100271 For a circular pipe, and considering a small angular part of the crosssectional area defined by the angleaB, the partial change in the area is:
aAe = (RaB)auR (7) where R is the internal radius of the pipe and auR is the change in the radial displacement at radius R. Dividing Eq. (7) by (A c'p) and integrating over 9leads to:
l aA 1 2 JauR d9 (8) A ap ;rRap o where the change in the radial displacement at radius R, OUR, is equal to:
au _ Ra9 + ase RaB _ R
R ae (9) = 8CB R
100281 For a pipe that is thinwalled, that is where the ratio between its diameter and thickness is large, stresses in the pipe wall are nearly uniform across its thickness.
Consideration of the equilibrium of forces acting on half of the crosssectional area of the pipe wall shows the circumferential stress to be:
6B = Rp and a6e = Rap (10) t t where t is the thickness of the pipe wall defined by:
t= f(B) (11) [0029] For a pipe that's free to move axially, e.g., with expansion joints throughout its length, or for a pipe material having a high modulus of elasticity, e.g., steel or concrete, the change in axial stress, a6, , is negligible and can be assumed to be zero.
For other fixation conditions, the change in the axial stress can be significant and should be taken into account. For example, for a pipe constrained against axial movement throughout its length, ct = 0 and hence: a6, =P'06B (12) [0030] Substituting Eq. (10) and (12) in (6), Eq. (6) in (9), and finally Eq.
(9) in (8) leads to (assuming that the wall thickness profile is symmetric about the pipe's centreline):
laA r 2ird9 A ap ,rE O f(e) (13) D dO
_ C;,rE j.f(B) where D is the diameter of the pipe and c is a factor that takes into account the fixation method of the pipe and is given by:
rl for a pipe having expansion joints throughout its length or having a high modulus of elasticity c= jl 1~ll z for a pipe constrained against axial movement throteghottt its length (14) [0031] Pipes buried in corrosive soils may not loose their thickness evenly around the circumference. Most likely, this is due to the formation of corrosion cells on the outer surface of the pipe as a result of differential aeration. This happens when the pipe's crosssection is partially in contact with two soils , for example a porous and hence wellaerated soil, such as soils used for backfill, and an impermeable and hence poorly aerated soil, such as native clay soils. Differential aeration may also occur on the internal surface of the pipe due to the accumulation of deposits at the bottom of the pipe. To take this phenomenon into account, the wall thickness of the pipe may be assumed to vary linearly with the angular coordinate as follows:
tmax tmin B+t for  f9r < B< f9r t = ~ min (15) t nax for fir <_ B<_  fir \
wheref is the fraction of the pipe crosssection having nonunifonm thickness, and tmin is the minimum wall thickness at e= 0 and t,,,ax is the maximum wall thickness at B= 7T.
The mean thickness, tmean, is then equal to:
t _ f tmax 2 tinin + l(1 _ f)t,nax (16) mean [0032] A linear circumferential thickness profile was selected in the example above for its simplicity and ease of demonstration. However, if more accurate results are required, more representative profiles can be used. Substituting Eq. (15) in (13) and evaluating the integral leads to:
1 aA = c D (1 f) + ln W tmax + ll  J) tinin 1 ln(t,nin ) (17) A ap E tmax tinax  tinin and substituting Eq. (16) in (4) leads to the following equation for the pipe's acoustic velocity:
V V 1+ CD K (1  f)+ 1nLJ tmax + ll  J) tmin 1 ln(tmin ) (1 g) tmax tmax  tmin where c is defined by Eq. (14).
[0033] The validity of Eq. (18) can be checked by considering the special case of a pipe having uniform thickness profile, i.e., tmin = tmax = t= Since lim in(x)  ln(x  a)  1 (19) a>o x(xa) x Eq. (18) becomes:
v=vo 1+c~ K (20) t E
The velocity of acoustic waves given by Eq. (20) is the same as that derived in standard textbooks for fluidfilled cylindrical thinwalled pipes with a uniform crosssection.
100341 The errors resulting from assumption that the pipe is thinwalled, as is the case in US patent no. 6,531,032, are small for the purpose of locating pipe leaks.
However, for thickness measurements, the error may not be sufficiently small. For example, for a 152 mm cast iron pipe that is 10 mm thick with v = 1218 m/s, the backcalculated uniform thickness is equal to 9 mm, assuming that the pipe is thinwalled. This corresponds to a spurious loss of 10%. For more accuracy, full account must be taken of the variation of stresses across the thickness of the pipe wall.
[0035] The radial displacement at the inner radius for an unconstrained pipe with expansion joints throughout its length, taking into account the variation of stresses across its thickness, is given by:
au ap D3 +D(1+~C> (21) R E 4t(D+t) 2 and for pipes with constrained axial movement throughout it's given by: ap [
D' auR = ~. 4t(D+r)(1P2)+~(l+,u) (22) Halliwell, A.R. "Velocity of a water hammer wave in an elastic pipe", Proceedings of the American Society of Civil Engineers, Journal of the Hydraulics Division, Vol.
89, No.
HY4, pp. 120, 1963.
100361 Substituting Eq. (15) in (21) and (22), Eq. (21) and (22) in (8), Eq.
(8) in (4) and evaluating the integral leads to the following velocity equation for a pipe with expansion joints throughout its length:
v=v,, F+E D F+2(1+,u) (23a) ;z and the following equation for pipes with constrained axial movement throughout its length:
D F(1,u2)+2(1+fc) (23b) v=vo F+E
where F (1f);T + 1 In 2nfa + b  b2 4ac ln (blb2 4ac (24) tmax (D + tmax ) b2 4ac 2nfa + b+ b2  4ac b+ b2  4ac a tinax  tinin (25a) b = ~ tmax tmin (2tmin + D) (25b) C = tinin + tminD (25c) [0037] For a thickwalled pipe having a uniform thickness, Eq. (23) becomes:
v=vo I+D EK (~(1+~)+D+t) (26a) for a pipe with expansion joints throughout its length, and v=vo 1+D E(~(l+u)+D+t(1_P2)) (26b) //~ t for a pipe with constrained axial movement, which are in agreement with expressions derived in standard textbooks for fluidfilled cylindrical thickwalled pipes with a uniform crosssection.
[0038] The above formulations for thin and thickwalled pipes with nonuniform circumferential thickness profiles do not take into account shear stresses in the pipe wall that are expected to develop as a result of having unaxisymetric radial displacement. In the formulation for thinwalled pipes, it is assumed that the crosssection of the pipe remains circular in order to simplify the calculation of the circumferential stress, i.e., Eq.
10. Similarly, to simplify the formulation for thickwalled pipes, radial displacements for pipes with uniform thickness profiles are used. A rigorous formulation, taking into account shear stresses in the pipe wall, is possible. However, such formulation would be too complex and the small gain in accuracy is unwarranted.
[00391 The above formulations for both thin and thickwalled pipes do not take into account the inertia of the pipe wall and the surrounding soil. It is assumed that the pipe responds statically to propagating dynamic pressure waves. At low frequencies, well below the ring frequency of the pipe, errors caused by this assumption are small as the pipe's response is dominated by the stiffness of its wall. For example, considering only the inertia of the pipe wall, the velocity equation for a pipe having uniform crosssection and with expansion joints throughout its length, the velocity equation is given by:
v=vo 1+D K 2 21 (27) t E 1D CV Ppipel4E
where co is the frequency of the propagating pressure wave (in radians per second) and pp.pe is the density of the pipe wall material. The derivation of this expressions is explained in Muggleton, J.M, Brennan, M.J., and Pinnington, R.J. "Wavenumber prediction of waves in buried pipes for water leak detection", Journal of Sound and Vibration, Vol. 249, No. 5, pp. 939954, 2002, the contents of which are herein incorporated by reference.
[0040] For the case of a cast iron pipe that is 152 mm in diameter and 12 mm thick, the maximum frequency of acoustic noise signals is typically 800 Hz. The maximum error in velocity resulting from ignoring the inertia of the pipe wall is a miniscule 0.07% (E = 128 GPa, ppipe 7100 kg/m3, K = 2.157 GPa at 16 C). This is also the case for other metallic pipes.
100411 Change in the nominal internal diameter, due to wall thickness loss, is not taken into account. However, such changes can be easily incorporated, although the small gain in accuracy makes the additional effort unwarranted.
100421 In deriving the general form of the velocity equation, i.e., Eq. 3, based on conservation of mass in a infinitesimal pipe section, small terms are neglected. It is assumed that this has a negligible effect on the acoustic velocity. Even if the effect is not so, determination of the bulk modulus of elasticity of the fluid carried by the pipe as described later amounts to calibrating the whole thickness measurement method.
The back calculated bulk modulius implicitly includes corrections for approximations made in the derivation of the velocity equation, e.g., neglecting small terms and inertial effects.
[0043] The minimum thickness of the pipe, tm;n, can be back calculated using Eqs. (18) or (23) for pipes with linearly varying wall thickness. The maximum thickness, tmax, is assumed to be equal to the original thickness of the pipe wall, which is usually known or can be measured using a single pipe sample. This is justified based on the observation that a certain part of the pipe's crosssection normally retains its original thickness. This part corresponds to the cathode of the corrosion cell created by differential aeration of the pipe's surface. The minimum thickness can also be calculated using Eq. (16) from the mean thickness back calculated using Eq. (20) or (26) for pipes having uniform wall thickness. This will lead to less accurate results than would be obtained using Eq. (23) for a thickwalled pipe with linearly varying wall thickness. For the same fixation condition, using Eqs. (18), (20), or (26) underestimates t,n;n. If the pipe can be assumed to have a uniform thickness profile (as may be found from experience for a particular area), the average thickness can be back calculated using Eq. 26.
100441 The velocity of acoustic waves in the pipe, v, can be measured by correlating acoustic noise signals, which can be ambient or created by intentionally by an acoustic source at a known location. The internal diameter of the pipe, D, bulk modulus of elasticity of the fluid, K, and its density, p, elastic modulus of the pipe material, E, and its Poisson's ratio, p, are usually known or can be easily found.
[0045] In order to practice the method in accordance with the invention, it is necessary to know the velocity of sound in unbounded fluid, vo or the bulk modulus of the fluid, and its density. Considering the case of water distribution pipes, the velocity of sound in an unconfined body of pure water is given by:
v = 1.402385 x 103 + 5.038813 T 5.799136 x 102Tz +3.287156 x 104 T3 (28)  1.398845 x 106 T4 + 2.787860 x 109 T5 where T is the water temperature in C. This expression is based on Marczak, W. (1997), Water as a standard in the measurement of the speed of sound in liquids.
Journal of the Acoustical Society of America, Vol. 102, No. 5, pp. 27762779, the contents of which are incorporated herein by reference.
[0046] Table 1 lists the velocity of sound, density and the corresponding bulk modulus of elasticity for temperatures between 0 and 40 C. Density values are based on the Handbook of Chemistry and Physics, CRC Press, 85'h edition, 20042005, the contents of which are incorporated herein by reference. Bulk modulus values were obtained by using Eq. 2.
Table 1: Velocity of sound, density and bulk modulus of elasticity of water Temperature Velocity of sound Density of water Bulk modulus ( C) (m/s) (kg/m3) (GPa) 0 1402 999.8426 1.966 1 1407 999.9015 1.980 2 1412 999.9429 1.994 3 1417 999.9672 2.008 4 1422 999.975 2.021 1426 999.9668 2.034 6 1431 999.943 2.046 7 1435 999.9043 2.059 8 1439 999.8509 2.071 9 1443 999.7834 2.083 1447 999.7021 2.094 11 1451 999.6074 2.105 12 1455 999.4996 2.116 13 1459 999.3792 2.127 14 1462 999.2464 2.137 1466 999.1016 2.147 16 1469 998.945 2.157 17 1473 998.7769 2.166 18 1476 998.5976 2.176 19 1479 998.4073 2.185 1482 998.2063 2.194 21 1485 997.9948 2.202 22 1488 997.773 2.210 23 1491 997.5412 2.218 24 1494 997.2994 2.226 1497 997.048 2.234 26 1499 996.787 2.241 27 1502 996.5166 2.248 28 1504 996.2371 2.255 29 1507 995.9486 2.261 1509 995.6511 2.268 31 1511 995.345 2.274 32 1514 995.0302 2.280 33 1516 994.7071 2.285 34 1518 994.3756 2.291 1520 994.0359 2.296 36 1522 993.6883 2.301 37 1524 993.3328 2.306 38 1525 992.9695 2.311 39 1527 992.5987 2.315 1529 992.2204 2.319 (0047] Limited available information about the compressibility of lake waters indicates that it is not significantly different from that of pure water, see for example Dorsey, N.E.
(1940). Properties of Ordinary WaterSubstance. Reinhold Publishing Corporation, New York, U.SA. However, the velocity of sound given by Eq. 28 is based on experimental results that have been obtained for pure water at MHz frequencies. Therefore, this equation may not be applicable for pure or ordinary water at frequencies below 1000 Hz, which dominate acoustic signals in water distribution pipes. It was shown by O'Donnell M., Jaynes E.T., and Miller J.G. (1981), KramersKronig relationship between ultrasonic attenuation and phase velocity, J. Acoust. Soc. Am. Vol 69, No 3, pp 696701that a system that exhibits attenuation, which is the case for water, must exhibit dispersion, i.e., dependence of phase velocity on frequency. Also, they showed that acoustic velocities at low frequencies are typically lower than those at higher ones. Consequently, the bulk moduli of water in distribution pipes may be lower than those listed in Table 1.
100481 Bulk moduli used for water hammer analysis in some texts and handbooks are the same as those listed in Table 1; while they are slightly lower in others.
Small discrepancies in the bulk modulus have a minor effect on water hammer calculations.
However, when bulk moduli listed in Table I were used with the proposed nondestructive testing method, the predicted thickness loss was overestimated.
The dependence of predicted wall thickness on the bulk modulus of water is shown in Figure 3 for a 12 mm thick, 152 mm 0 pit cast iron pipe having an acoustic velocity of 1247 m/s.
For example, using a bulk modulus equal to 2.2 GPa, as used by some texts at 20 C, predicted thickness would be 8.3 mm, while it would be 10.4 mm using a modulus of 2.03 GPa, as used by other texts at 20 C.
100491 The uncertainty regarding the appropriate value of the bulk modulus to be used for thickness calculations can be minimized in accordance with an embodiment of the invention by careful measurement. First, the acoustic velocity is measured for a "reference" pipe of a known wall thickness, diameter and Young's modulus.
Preferably, a recently installed pipe of a known class should be used and its Young's modulus should be measured dynamically for an exhumed or leftover sample. Then, the bulk modulus is back calculated from the appropriate theoretical acoustic velocity equation or a numerical model for waterfilled pipes together with other already known or measured pipe parameters. Measurement of the acoustic velocity of the reference pipe and other pipes should be performed within few days of each other. This is to ensure that temperatures of the fluids in the pipes are similar.
[0050] Alternatively, the bulk modulus may be determined from a relationship established from a set of measurements of the fluid's bulk modulus and temperature for the reference pipe at different times of the year. Determination of the bulk modulus as described here amounts to calibrating the whole thickness measurement method. The back calculated modulus implicitly includes corrections for approximations made in the derivation of the velocity equation, e.g., neglecting small terms and inertial effects.
100511 Following is an example of the determination of the relationship between the bulk modulus of elasticity of the fluid and its temperature. Acoustic velocity was measured for a recently installed 152 mm 0 Class 52 cementlined ductile iron water distribution pipe having the following temperatures: 20.8, 11.7, and 5.3 C.
[00521 For a cementlined pipe of circular crosssection, the acoustic wave velocity can determined by the following equation, given in Fluid Transients in Pipes and Tunnels:
Speed of Propagation of Pressure Waves. Engineering Sciences Data Item No.
83046, ESDU International, 1983, London, U.K:
v = KwlP,v (29) 1+K (Dep)(IP Z)[(DZ +ep)(1f.c)+2,uDep]
EpDep(Dep)(1,u)+Ele,[(DZ +epz)(1 ft)+2,uDeP]
where v is velocity of acoustic waves in the pipe, K,v and p,,, are bulk modulus of elasticity and density of water, respectively; Ep, D, and ep are Young's modulus, internal diameter, and metal thickness of the pipe, respectively; El and el are Young's modulus and thickness of the cement lining, respectively; and p is Poisson's ratio, assumed to be the same for ductile iron and the cement lining.
[0053] The thicknesses of the metal section and cement lining for 152 mm 0 Class 52 ductile iron pipes are 7.9 and 2 mm, respectively. The thickness of an "equivalent" ductile iron pipe with no cement lining is equal to 8.2 mm, as found from Eq. 29. The equivalent pipe has the same acoustic wave velocity as the cementlined one. Young's modulus of ductile iron is equal to 169 GPa, as found from the resonance frequency of a rod sample using an impactecho test that can be seen in Figure 4; Poisson's ratio was taken equal to 0.3; and Young's modulus of the cement lining was taken equal to 24 GPa. The impactecho test and modulus calculation was performed in accordance with ASTM
standard E
187601: Standard test method for dynamic Young's modulus, shear modulus, and Poisson's ratio by impulse excitation of vibration, 2001.
100541 The bulk modulus of water was back calculated by adjusting its value until the predicted pipe wall thickness was equal to 8.2 0.1 mm. The modulus was found to be 1.95 GPa at 20.8 C, 1.875 GPa at 11.7 C, and 1.81 GPa at 5.3 C. A straight line was fitted to the backcalculated moduli and is shown in Figure 5 together with moduli based on the velocity of sound given by Eq. 28 for pure water at MHz frequencies.
Over the 5 to 25 C temperature range shown in Figure 5, which is expected for water in distribution pipes, the modulus for pure water at high MHz frequencies almost varies linearly with temperature. This lends support to the adequacy of the fitted straight line for estimating the bulk modulus of water in distribution pipes.
[0055] Typical setups in accordance with embodiments of the invention are shown in Figures la and lb. A buried water pipe 10 has hydrants 12a, 12b, 12c. Sensors 1,2 are mounted on two of the hydrants, while the third provides a source outside the hydrants including the sensors. In Figure la, the sensors are mounted on hydrants 12a and 12b, while the hydrant 12c acts as a source. In this case the propagation velocity is determined by measuring the propagation time between hydrants 12a and 12b. The propagation velocity is given by the expression v = D / AT, where OT is the time delay between the signals sensed by sensors 1 and 2, and assuming equal lengths for pipes connecting fire hydrants 12a and 12b to the main pipe 10.
[0056] In Figure lb, the hydrant 12b acts as the source, and the disturbance is detected by the sensors 1, 2 at hydrants 12a, 12c on either side of the source. In this case the propagation velocity is given by the expression v = (L2  Lj)/ AT, assuming equal lengths for pipes connecting fire hydrants 12a and 12c to the main pipe 10.
100571 Signals are sent remotely from transmitters 14 attached to the sensors 1, 2 to a receiver 15 connected to PC 16 running a program transferred to its hard drive from a storage medium, such as a CD ROM 18. The computer 16 is WindowsTM based (although it will be appreciated that any other suitable operating system can be used) and displays the results in windows shown in Figures 2a and 2b. Figure 2a shows the results of a measurement. Figure 2b is a screen allowing the user to enter relevant parameters, such as the pipe material, the temperature etc. The signals may be transmitted in analogue or digital forms. In an alternative setup, signals from the sensors 1, 2 can be sent to the PC
via cables. Alternatively, dedicated hardware can be used instead of a PC to calculate the time delay between acoustic signals and determine the pipe's wall thickness.
[0058] When sensors are mounted on fire hydrants that are connected to the pipe being tested, the connecting pipes should be traced on the surface and their lengths measured accurately and incorporated in the sensors' distances from the acoustic source. If it is not possible to trace the connecting pipes and hence their lengths are based on a "best guess' of their layout, the lengths should be checked for accuracy. One way of doing so is to measure the propagation velocities of acoustic noise created by at least two sources at different locations. For example, two outofbracket sources on opposite sides of the bracket can be used. If distances of the sensors from the acoustic sources are inaccurate due to errors in the lengths of connecting pipes between fire hydrants and the main pipe, the separately measured propagation velocities of acoustic noise induced by the two sources will be different.
[00591 A system of linear equations can be formed based on the relationship between time delays of acoustic signals induced by acoustic sources at different locations, acoustic propagation velocity in the pipe, and lengths of connecting pipes. Time delays between measured acoustic noise can be determined using the timeflight method or the crosscorrelation function (either traditional or enhanced). The acoustic velocity can then be found by solving the system of linear equations. The number of acoustic sources at different locations should be equal to the number of unknowns. Two or three acoustic sources are sufficient in most cases.
[00601 As an example, consider the case in which the sensors 1 and 2 are mounted on fire hydrants that are connected to the main pipe with perpendicular connecting pipes having unknown lengths of L, and L2, respectively. The distance between the two points where the connecting pipes to the fire hydrants branch out from the main pipe is D
and can be measured accurately. The time delays Ot, and At2 between acoustic signals induced by outofbracket sources at the side of sensors I and 2, respectively, are related to the acoustic velocity, v, and LI and L2 by the following equations:
Ot, (D+L2)L, (30) v At2  L2 (D+L,) (31) v which can be solved to determine the propagation velocity as follows:
v   2D (32) (At2  Ot,) 100611 The pipe wall thickness determined by the method described represents an average value for the pipe section between the two points where acoustic signals are measured. This is not a limiting aspect of the method. Generally, pipes will have a roughly uniform thickness profile over significant lengths, say 100 metres, as soil and bedding conditions are unlikely to change significantly over wide areas. Even for situations where the longitudinal thickness profile varies, an average thickness profiles is more appropriate and meaningful than discrete thickness values for evaluating the residual life of pipes for the purpose of longterm planning of rehabilitation and replacement needs.
100621 Virtually every water utility in the industrialized countries of the world is facing major challenges in securing capital dollars to replace aging underground water distribution pipes. This nondestructive technology in accordance with embodiments of the present invention to measure pipe metal loss, i.e., to determine the remaining thickness of pipe walls, provides these utilities with a reliable and accurate way to obtain data that allows them to calculate the remaining service life of pipes. This allows the formulation of capital budget plans that are based on technically sound engineering data, which in turn enhances the decision making process.
[0063] The invention also has applicability to the oil and gas industry as well as the building industry (e.g., pipes of fire sprinkler systems, which are known to suffer severely from the action of corrosion).
Claims (32)
detecting an acoustic disturbance propagating past two longitudinally separated points on said pipe;
determining an actual value representative of the propagation velocity of said acoustic disturbance;
computing a corresponding predicted value for the propagation velocity as a function of at least one wall thickness parameter of said pipe by using a theoretical model for the propagation of acoustic waves in said pipe that assumes said pipe has a finite wall thickness with a predetermined nonuniform circumferential thickness profile and takes into account stresses across the thickness of the pipe wall, and wherein said wall thickness parameters are representative of wall thickness at different circumferential locations on on said pipe; and computing said at least one wall thickness parameter by matching said actual value with said predicted value.
where v is the predicted value, v0 is the propagation velocity of the unbounded fluid, D is the diameter of the pipe, K is the bulk modulus of elasticity of the fluid, E
is the elastic modulus of material forming the pipe, and t max and t min are respectively the maximum and minimum pipe wall thicknesses at respective angular locations .theta. = 0 and .theta. = .pi., where .theta.
is a polar coordinate, and F is given by the expression:
where
where v is the predicted value, v0 is the propagation velocity of the unbounded fluid, D is the diameter of the pipe, E is the elastic modulus of material forming the pipe, and t max and t min are respectively the maximum and minimum pipe wall thicknesses at respective angular locations .theta. = 0 and .theta. = .pi., where .theta. is a polar coordinate, and F is given by the expression:
where
where v is the predicted value, v0 is the propagation velocity of the unbounded fluid, D is the diameter of the pipe, K is the bulk modulus of elasticity of the fluid, E
is the elastic modulus of material forming the pipe, and t is the thickness, and µ is the Poisson ratio.
where v is the predicted value, v0 is the propagation velocity of the unbounded fluid, D is the diameter of the pipe, K is the bulk modulus of elasticity of the fluid, E
is the elastic modulus of material forming the pipe, and t is the thickness, and µ is the Poisson ratio.
a) first and second sensors for detecting an acoustic disturbance propagating past two longitudinally separated points on said pipe; and b) a processor receiving inputs from said first and second sensors and programmed to:
(i) determine an actual value representative of the propagation velocity of said acoustic disturbance;
(ii) compute a corresponding predicted value for the propagation velocity as a function of at least one wall thickness parameter of said pipe by using a theoretical model for the propagation of acoustic waves in said pipe that assumes said pipe has a finite wall thickness with a predetermined nonuniform circumferential thickness profile and takes into account stress across the thickness of the pipe wall, and wherein said wall thickness parameters are representative of wall thickness at different circumferential locations on said pipe; and (iii) compute said at least one wall thickness parameter by matching said actual value with said predicted value.
hydrants connected to said pipe, control valves attached to the pipe, and the pipe wall accessed via manholes or small excavated keyholes in the soil.
accept signals from sensors responsive to an acoustic disturbance propagating along a pipe;
compute an actual value representative of the propagation velocity of said acoustic disturbance by dividing the difference between the distances of said sensors from corresponding acoustic source by the time delay between successive acoustic disturbances;
compute a corresponding predicted value for the propagation velocity as a function of at least one wall thickness parameter of said pipe by using a theoretical model for the propagation of acoustic waves in said pipe that assumes said pipe has a finite wall thickness with a predetermined nonuniform circumferential thickness profile and takes into account stress across the thickness of the pipe and wherein said wall thickness parameter is different at different circumferential locations on said pipe;
and compute said at least one wall thickness parameter by matching said actual value with said predicted value.
detecting acoustic disturbances from at least two sources of acoustic disturbance at each of said points;
computing the propagation velocities of each of said disturbances detected at said points; and comparing the measured propagation velocities of acoustic disturbances.
detecting acoustic disturbances from two or more acoustic sources at two or more detection points on the pipe; and computing the propagation velocity by solving a system of linear equations relating time delays corresponding to different acoustic sources with the acoustic velocity and lengths of pipe between sources of said disturbances and sensors.
Priority Applications (3)
Application Number  Priority Date  Filing Date  Title 

US11/156,573  20050621  
US11156573 US7328618B2 (en)  20050621  20050621  Nondestructive testing of pipes 
PCT/CA2006/000996 WO2006136013A1 (en)  20050621  20060619  Nondestructive testing of pipes 
Publications (2)
Publication Number  Publication Date 

CA2612835A1 true true CA2612835A1 (en)  20061228 
CA2612835C CA2612835C (en)  20130813 
Family
ID=37570059
Family Applications (1)
Application Number  Title  Priority Date  Filing Date 

CA 2612835 Active CA2612835C (en)  20050621  20060619  Nondestructive testing of pipes 
Country Status (5)
Country  Link 

US (2)  US7328618B2 (en) 
EP (1)  EP1896842B1 (en) 
JP (3)  JP2008544260A (en) 
CA (1)  CA2612835C (en) 
WO (1)  WO2006136013A1 (en) 
Families Citing this family (32)
Publication number  Priority date  Publication date  Assignee  Title 

US8017858B2 (en) *  20041230  20110913  Steve Mann  Acoustic, hyperacoustic, or electrically amplified hydraulophones or multimedia interfaces 
US7328618B2 (en) *  20050621  20080212  National Research Council Of Canada  Nondestructive testing of pipes 
US7810378B2 (en)  20070621  20101012  National Research Council Of Canada  Monitoring of leakage in wastewater force mains and other pipes carrying fluid under pressure 
CA2718476C (en)  20080314  20161115  Cidra Corporate Services, Inc.  Flow and pipe management using velocity profile measurement and/or pipe wall thickness and wear monitoring 
US9182081B2 (en) *  20080630  20151110  Bp Corporation North America Inc.  Rapid databased data adequacy procedure for pipeline integrity assessment 
US7941282B2 (en)  20080801  20110510  Bp Exploration Operating Company Limited  Estimating worst case corrosion in a pipeline 
CA2732937C (en) *  20080805  20170530  Pure Technologies Ltd.  Device and method to assess impairment of pipeline wall strength 
GB2475014B8 (en)  20080815  20130814  Adelaide Res & Innovation Pty  Method and system for assessment of pipeline condition 
GB0914463D0 (en)  20090819  20090930  Sev Trent Water Ltd  Leak detector 
WO2011061739A1 (en) *  20091122  20110526  Acousticeye Ltd  Apparatus and method for real time monitoring of tube systems 
KR100989515B1 (en) *  20100503  20101026  부경엔지니어링주식회사  Pipe conduit block testing equipment using microprocessor and the method thereof 
EP2582886A4 (en)  20100616  20161207  Mueller Int Llc  Infrastructure monitoring devices, systems, and methods 
RU2467299C1 (en) *  20110512  20121120  Дочернее Открытое Акционерное Общество (ДОАО) "Оргэнергогаз" ОАО "Газпром"  Method of hydraulic impact test and rehabilitation of pipeline, which is implemented during its increased pressure loading in field conditions 
GB201111980D0 (en) *  20110713  20110831  Statoil Petroleum As  Acoustic surveying 
US9291520B2 (en)  20110812  20160322  Mueller International, Llc  Fire hydrant leak detector 
US9766175B1 (en)  20120305  20170919  Vista Precision Solutions, Inc.  Method and apparatus for inservice measurement of the bottom thickness and corrosion rate of a tank bottom 
JP5673593B2 (en) *  20120411  20150218  日本電気株式会社  Water leak detection methods and water leak detection equipment 
EP2912416B1 (en)  20121026  20180530  Mueller International, LLC  Detecting leaks in a fluid distribution system 
EP2725352A1 (en)  20121027  20140430  Valerian Goroshevskiy  Apparatus for noncontact metallic constructions assessment 
EP2956751A1 (en) *  20130318  20151223  Siemens Aktiengesellschaft  Method and monitoring device for monitoring a structure 
RU2516766C1 (en) *  20130409  20140520  Открытое Акционерное Общество (ОАО) "Оргэнергогаз"  Method to recover bearing capacity of pipeline 
US9651445B2 (en)  20130415  20170516  UtBattelle, Llc  Fluid pipeline leak detection and location with miniature RF tags 
WO2014169965A1 (en) *  20130419  20141023  Gutermann Ag  Method for evaluating acoustic sensor data in a fluid carrying network and evaluation unit 
US9528903B2 (en)  20141001  20161227  Mueller International, Llc  Piezoelectric vibration sensor for fluid leak detection 
CN104535654B (en) *  20150129  20170616  太原工业学院  An apparatus for ultrasonic nondestructive testing of metal rods detecting means 
US20160290974A1 (en) *  20150331  20161006  Mueller International, Llc  Determination of pipe wall failure based on minimum pipe wall thickness 
US9835592B2 (en)  20150616  20171205  Mueller International, Llc  Determination of tuberculation in a fluid distribution system 
WO2017078004A1 (en) *  20151104  20170511  日本電気株式会社  Pipe condition detection device, pipe condition detection method, computerreadable recording medium, and pipe condition detection system 
US9670650B2 (en) *  20151109  20170606  Sensus Spectrum Llc  Fire hydrant monitoring system 
US20170176395A1 (en) *  20151218  20170622  Mueller International, Llc  Noisemaker for pipe systems 
RU2620023C1 (en) *  20160809  20170522  Общество с ограниченной ответственностью "ТЕХНОАССК"  Method of determining the place of the flow in the pipeline and the device for its implementation 
KR101794968B1 (en) *  20170427  20171107  (주)서용엔지니어링  Leak sencing apparatus of water supply using fire hydrant 
Family Cites Families (19)
Publication number  Priority date  Publication date  Assignee  Title 

US4056970A (en) *  19751030  19771108  Yeda Research And Development Co., Ltd.  Ultrasonic velocity and thickness gage 
US4930358A (en) *  19870327  19900605  Tokyo Keiki Co., Ltd.  Method of and apparatus for measuring flow velocity by using ultrasonic waves 
JPH0476454A (en) *  19900719  19920311  Shimada Phys & Chem Ind Co Ltd  Inspection method for liquid piping 
GB2253907B (en) *  19910321  19950524  Halliburton Logging Services  Device for sensing fluid behaviour 
US5531099A (en) *  19941109  19960702  At&T Corp.  Underground conduit defect localization 
US5708211A (en) *  19960528  19980113  Ohio University  Flow regime determination and flow measurement in multiphase flow pipelines 
US5970434A (en) *  19980129  19991019  Southwest Research Institute  Method for determining average wall thickness for pipes and tubes using guided waves 
US6000288A (en) *  19980421  19991214  Southwest Research Institute  Determining average wall thickness and wallthickness variation of a liquidcarrying pipe 
US7261002B1 (en) *  19990702  20070828  Cidra Corporation  Flow rate measurement for industrial sensing applications using unsteady pressures 
EP1194745B1 (en) *  19990702  20070919  Weatherford/Lamb, Inc.  Flow rate measurement using unsteady pressures 
JP2001194349A (en) *  19991104  20010719  Mitsubishi Heavy Ind Ltd  Apparatus and method for inspecting back face of lining 
US6453247B1 (en) *  20000114  20020917  National Research Council Of Canada  PC multimediabased leak detection system for water transmission and distribution pipes 
US6561032B1 (en) *  20000515  20030513  National Research Council Of Canada  Nondestructive measurement of pipe wall thickness 
JP2002236115A (en) *  20010206  20020823  Sonoda Engineering:Kk  Method and device for degradation diagnosis of conduit 
JP2003185643A (en) *  20011217  20030703  Matsushita Electric Ind Co Ltd  Crack detecting system 
JP3986049B2 (en) *  20020115  20071003  財団法人くまもとテクノ産業財団  Defect inspection method and a defect inspection apparatus 
JP3913144B2 (en) *  20020827  20070509  株式会社日立製作所  Piping inspection method and apparatus 
US7328618B2 (en) *  20050621  20080212  National Research Council Of Canada  Nondestructive testing of pipes 
US7881884B2 (en) *  20070206  20110201  Weatherford/Lamb, Inc.  Flowmeter array processing algorithm with wide dynamic range 
Also Published As
Publication number  Publication date  Type 

JP2015083979A (en)  20150430  application 
EP1896842B1 (en)  20170301  grant 
JP5930427B2 (en)  20160608  grant 
JP5687262B2 (en)  20150318  grant 
EP1896842A4 (en)  20110810  application 
WO2006136013A1 (en)  20061228  application 
US20060283251A1 (en)  20061221  application 
CA2612835C (en)  20130813  grant 
US7328618B2 (en)  20080212  grant 
JP2013061350A (en)  20130404  application 
JP2008544260A (en)  20081204  application 
EP1896842A1 (en)  20080312  application 
US7475596B2 (en)  20090113  grant 
US20080078247A1 (en)  20080403  application 
Similar Documents
Publication  Publication Date  Title 

Finno et al.  Supported excavations: observational method and inverse modeling  
US6971259B2 (en)  Fluid density measurement in pipes using acoustic pressures  
Park et al.  Feasibility of using impedance‐based damage assessment for pipeline structures  
Barshinger et al.  Guided wave propagation in an elastic hollow cylinder coated with a viscoelastic material  
Hunaidi et al.  Acoustical characteristics of leak signals in plastic water distribution pipes  
US20040123665A1 (en)  Nondestructive detection of reinforcing member degradation  
Long et al.  Attenuation characteristics of the fundamental modes that propagate in buried iron water pipes  
Sanderson et al.  Guidelines for the use of ultrasonic noninvasive metering techniques  
Gao et al.  A model of the correlation function of leak noise in buried plastic pipes  
US20030136186A1 (en)  Phase flow measurement in pipes using a density meter  
Kwun et al.  Torsional guidedwave attenuation in coaltarenamelcoated, buried piping  
US20100315630A1 (en)  Method and system for estimating fluid leak flow rates using distributed optical fiber sensors  
Muggleton et al.  Axisymmetric wave propagation in fluidfilled pipes: wavenumber measurements in in vacuo and buried pipes  
Mi et al.  An ultrasonic method for dynamic monitoring of fatigue crack initiation and growth  
US6666095B2 (en)  Ultrasonic pipe assessment  
Long et al.  Acoustic wave propagation in buried iron water pipes  
Glisic et al.  Fiber optic method for health assessment of pipelines subjected to earthquakeinduced ground movement  
WO2009158630A1 (en)  Method and system for estimating fluid leak flow rates using distributed optical fiber sensors  
US6561032B1 (en)  Nondestructive measurement of pipe wall thickness  
Castaings et al.  Finite element modeling of torsional wave modes along pipes with absorbing materials  
Dixon et al.  Acoustic emission monitoring of slope instability: development of an active waveguide system  
Zhu  Noncontact ndt of concrete structures using air coupled sensors  
Pavlakovic et al.  A general purpose approach to calculating the longitudinal and flexural modes of multilayered, embedded, transversely isotropic cylinders  
JP2009036516A (en)  Nondestructive inspection device using guide wave and nondestructive inspection method  
Wang et al.  Guided wave propagation and spectral element method for debonding damage assessment in RC structures 
Legal Events
Date  Code  Title  Description 

EEER  Examination request 